Ballwin Plumbing, HVAC & Insulation Services
Located west of St. Louis, Ballwin is a small city with just over 30,000 people that was first formed in 1837. At Classic Aire Care, we are proud to offer our neighbors in Ballwin a wide selection of quality home comfort services, including:
- Heating and air conditioning
- Plumbing and drain services
- Energy efficiency and insulation services
- Indoor air quality services
- 24-hour emergency services
- And more!
Whether you live near New Ballwin Park or Ballwin Golf Course, our team of dependable and knowledgeable professionals is available at any time to handle all your HVAC, plumbing, and home comfort needs.
Contact Classic Aire Care at 314-300-6755 to request an estimate or to schedule an appointment!
Heating and Air Conditioning Services in Ballwin
At Classic Aire Care we offer a variety of heating and cooling services, including:
- Heating services: From replacing a thermocouple or changing an air filter, to repairing a flue or replacing the blower motor, our team can handle all your heating system maintenance, repair, and replacement needs.
- Air conditioning services: Whether you have a refrigerant leak or major compressor problems, our team can diagnose your air conditioning system quickly and provide affordable repair options. We also offer complete maintenance and replacement services, as well as convenient preplanned maintenance agreements.
- Emergency services: If your heating or air conditioning system breaks down after standard business hours, you can receive the help you need anytime with our 24-hour emergency HVAC repair service!
Our HVAC professionals are NATE certified, and are familiar with all common HVAC equipment, including furnaces, boilers, heat pumps, central air conditioners, ductless systems, packaged systems, air handlers, and more.
For HVAC repairs or maintenance, contact us today!
Plumbing Services in the Ballwin Area
Whether you have a minor faucet leak, a clogged sewer pipe, or a frozen water line, our team at Classic Aire Care can help. We provide a full selection of plumbing and drain services, including:
- Water, sewer, and drain pipe repair
- Pipe installation and replacement
- Gas line repair and replacement
- Sewer and drain cleaning
- Clog removal
- Trenchless pipe repair and relining
- Leak detection
- Backflow testing
- Fixture and faucet installations
- Toilet repair and replacement
- 24-hour emergency services
- And more!
Our plumbing professionals are available at any time, through our 24/7 emergency plumbing service, and they have the tools and experience necessary to solve nearly any pluming problem.
For help with your plumbing system, contact us today for service anywhere in Ballwin, from Kehrs Mill Road to Henry Avenue and anywhere in between!
Home Energy and Air Quality Services
If you home lacks insulation, has drafty windows, or is not properly sealed form air intrusion, your indoor air quality may suffer and your costs for heating and cooling will be unnecessarily high. At Classic Aire Care, we offer a variety of indoor air quality and home energy services that can improve your comfort and reduce your energy costs. These include:
- Home energy audits
- Programmable thermostat installations
- Insulation services
- Air sealing services
- Air purifier and air cleaner installation and maintenance
- Humidifier and dehumidifier installation and maintenance
- Ventilation system installation and repair
- And more!
To learn more about reducing your energy usage, talk to our team at Classic Aire Care today!
Call Today For Plumbing & HVAC Services in Ballwin
From HVAC maintenance and repair, to plumbing, drain, energy efficiency, and air quality services, you can trust our team at Classic Aire Care for all your home comfort needs.
To schedule an appointment, contact us at 314-300-6755 today!
for Ballwin, MO
Our Reviews by City
Linda - Ballwin, MO
Very thorough and friendly.
Pam - Ballwin, MO
All is good
Robert - Ballwin, MO
Again, Jeff did an excellent job for us
Janet - Ballwin, MO
Jeff replaced the coil on our air conditioner very recently. He came back to check everything and to clean the outside unit.
Janet - Ballwin, MO
Jeff and Classic Aire did a wonderful job for us. We needed a new coil. Jeff spent over 4 hours getting the damaged coil out and the new coil installed. Throughout the process, he was good-natured and pleasant. I am impressed with the way Classic Aire calls when they say they will and lets us know when when the technician is on the way. thank you.
Excellent response time
Tom - Ballwin, MO
Had a service Interruption on one of the holidays and service response was within 3 to 4 hours.
Very impressed with John Murphy
Gus - Ballwin, MO
The new travel video is very impressive! I don't know how costly this service is but it sure is helpful in knowing when the person will arrive.
Carolyn - Ballwin, MO
Professional work. Spent the time to do a good job
Jim - Ballwin, MO
Stephen - Ballwin, MO
You guys are always the best!!!
Merry Kweiter - Ballwin, MO
Always the best experiences with this company. Honest, transparent, and easy to work with.
Great & friendly service.
Ralph - Ballwin, MO
Martin - Ballwin, MO
Natalie - Ballwin, MO
Pam - Ballwin, MO
The service was very thorough and the technician was professional and friendly.
Jeff was very professional and extremely knowledgable.
Ron - Ballwin, MO
very fast response
John - Ballwin, MO
excellent service and professional work
Always great service, but...
Susan - Ballwin, MO
We had a zoning system installed in May of 2016. Today (3/5/18) we had to replace a damper, of which the damper was covered under warranty, but we paid $152 for labor. I am disturbed that a part such as a damper cannot last even two years. It makes me worry about future problems with dampers, and how much extra we'll have to pay to keep the zoning system functional. Otherwise, we've been using Classic Aire Care for many years, and are pleased with the service.
Great and quick check
Janet - Ballwin, MO
Jeff did a fine job for us today. He arrived when expected, was friendly and courteous, checked what he needed to check, and just left a few minutes ago. Thank you!
Kathleen - Ballwin, MO
Cleaned & checked condensing gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Replaced air filter. Customer complained of banging noise at times when system turns on. No noises found at this time. I found damper in first floor duct not closing. Damper was hitting mounting screws. I replaced with shorter mounting screws. Clean and check humidifier, replace pad, checked water flow and drain. Solenoid valve not opening. Replaced solenoid valve. Replaced UV lamp for APCO air purifier. Checked blower speeds. Setup furnace for two stage operation.
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Replaced air filter. Clean and check humidifier, replace pad, checked water flow and drain. 8.4uA. Blower: 3.1A . Inducer: 0.08A . Gas pressure: 2.0 inches water column. Temperature rise: 53 . Supply: 123 . Return:70 . Flame:14.5uA. Suggestions: Need to add humidifier to maintenance plan at next renewal.
Ordered Drain Spud, Distribution tray, Center insert... Won't be delivered to shop till at least Wednesday... lke Tech to collect $182.85... ----------------------------------------------------------------------- Found water leaking from humidifier pad holder and drain spud..need to replaced pad as well...ordered call when comes in...collect remaining balance when installed... John’s notes: January 3, 2019 : Replaced distributor tray, pad frame, drain spud, and pad. Tested operation. Checked for leaks.
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Checked filter. Blower: stg2: 4.6A . Inducer: 0.1/0.24A. Gas pressure: 2.0/3.5inches water column. Temperature rise: stg2: 60 . Supply: 128 . Return: 68 . Clean and check humidifier, replace pad, checked water flow and drain.
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Checked filter. Blower: 2.2/2.8A . Inducer: 0.08//0.23A. check humidifier. checked water flow and drain. Calibrated humidistat.
Cleaned & checked condensing gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Checked drain. Turned up humidistat. Blower: 2.2/5.3A . Inducer: 0.70/0.73A . Adjust Gas pressure:1.9 inches water column. Temperature rise: 53/59. Supply: 117/123. Return: 64. Suggestions: Replace thermostat batteries.
Cleaned and checked gas boiler. Checked voltage & amp draw of pump. Inspected heat exchanger & flue venting. cleaned burners & pilot assembly. Check compression tank pressure: 12. Tested water feed regulator. OK. Regulator setting: eight psi. Pressure gauge reads six PSI higher than actual. Checked vent. Oil pump motor. Set primary air. Supply: 137. Return: 105. Pressure: 22-6= 18.
Cleaned & checked 2 gas furnaces. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Replaced air filter. First floor system: customer complaint of noise when furnace turns on and when it turns off. I found no unusual noises at this time. Blower: 5.7A . Inducer: 1.25A . Gas pressure: 3.4inches water column. Temperature rise: 53 . Supply: 127 . Return: 74 . Second floor system: Blower:3.8A . Inducer: 1.2A . Gas pressure: 3.4inches water column. Temperature rise: 53 . Supply: 125. Return: 72 .
Customer replaced part that we delivered. Tested heat cycle. I collected payment.
Maintenance completed about two weeks ago. Found circuit boards showing pulse light: (normal no call for heat). Upon calling for heat board continued showing pulse indicator light! Picked up new board and replaced.
Found blower control board bad! Needs new board. Check temperature rise. 50. Suggestions: Need to check on cost and availability for repair.
Clean and check electric furnace. Tested heating elements. Tested sequencers. Checked voltage & amp draw of shaded pole blower. Vacuum filter. Total amps: 42.7. Voltage: 242. Check temperature rise. 38.
Fall maintenance today for the home furnace!
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Replaced air filter. Blower: 5.0A. Inducer: 1.7A. Gas pressure: 3.5 inches water column. Temperature rise: 57.
I replaced cracked condensate trap fitting. Reconnected piping using primer and glue. Secured and purged drain.
Replaced right roll-out safety. Tested operation. Billing cc on file.
Turn on heat at thermostat and tested operation. Inducer: 1.93A. Blower: 4.7A. Thermostat circuit: .59A. Checked filter. Check temperature rise. 62. Furnace is dirty. Recommend cleaning. After running about 25 minutes thermostat started dropping out voltage to furnace randomly. I removed thermostat to replace and customer changed her mind. I left switch to furnace off and thermostat off of the wall.
I replaced parts and wiring that was damaged from water leaking into furnace. Replaced hot surface igniter, wiring harness, and furnace control board. I discovered right rollout safety rusted and damaged. I bypassed part for temporary heat. Relying only on left rollout. I replaced clogged air conditioner drain tubing And fitting. Billing cc on file. Suggestions: replace right rollout safety. Need check on price and availability.
Fall maintenance today for the furnace!