Ballwin Plumbing, HVAC & Insulation Services
Located west of St. Louis, Ballwin is a small city with just over 30,000 people that was first formed in 1837. At Classic Aire Care, we are proud to offer our neighbors in Ballwin a wide selection of quality home comfort services, including:
- Heating and air conditioning
- Plumbing and drain services
- Energy efficiency and insulation services
- Indoor air quality services
- 24-hour emergency services
- And more!
Whether you live near New Ballwin Park or Ballwin Golf Course, our team of dependable and knowledgeable professionals is available at any time to handle all your HVAC, plumbing, and home comfort needs.
Contact Classic Aire Care at 314-300-6755 to request an estimate or to schedule an appointment!
Heating and Air Conditioning Services in Ballwin
At Classic Aire Care we offer a variety of heating and cooling services, including:
- Heating services: From replacing a thermocouple or changing an air filter, to repairing a flue or replacing the blower motor, our team can handle all your heating system maintenance, repair, and replacement needs.
- Air conditioning services: Whether you have a refrigerant leak or major compressor problems, our team can diagnose your air conditioning system quickly and provide affordable repair options. We also offer complete maintenance and replacement services, as well as convenient preplanned maintenance agreements.
- Emergency services: If your heating or air conditioning system breaks down after standard business hours, you can receive the help you need anytime with our 24-hour emergency HVAC repair service!
Our HVAC professionals are NATE certified, and are familiar with all common HVAC equipment, including furnaces, boilers, heat pumps, central air conditioners, ductless systems, packaged systems, air handlers, and more.
For HVAC repairs or maintenance, contact us today!
Plumbing Services in the Ballwin Area
Whether you have a minor faucet leak, a clogged sewer pipe, or a frozen water line, our team at Classic Aire Care can help. We provide a full selection of plumbing and drain services, including:
- Water, sewer, and drain pipe repair
- Pipe installation and replacement
- Gas line repair and replacement
- Sewer and drain cleaning
- Clog removal
- Trenchless pipe repair and relining
- Leak detection
- Backflow testing
- Fixture and faucet installations
- Toilet repair and replacement
- 24-hour emergency services
- And more!
Our plumbing professionals are available at any time, through our 24/7 emergency plumbing service, and they have the tools and experience necessary to solve nearly any pluming problem.
For help with your plumbing system, contact us today for service anywhere in Ballwin, from Kehrs Mill Road to Henry Avenue and anywhere in between!
Home Energy and Air Quality Services
If you home lacks insulation, has drafty windows, or is not properly sealed form air intrusion, your indoor air quality may suffer and your costs for heating and cooling will be unnecessarily high. At Classic Aire Care, we offer a variety of indoor air quality and home energy services that can improve your comfort and reduce your energy costs. These include:
- Home energy audits
- Programmable thermostat installations
- Insulation services
- Air sealing services
- Air purifier and air cleaner installation and maintenance
- Humidifier and dehumidifier installation and maintenance
- Ventilation system installation and repair
- And more!
To learn more about reducing your energy usage, talk to our team at Classic Aire Care today!
Call Today For Plumbing & HVAC Services in Ballwin
From HVAC maintenance and repair, to plumbing, drain, energy efficiency, and air quality services, you can trust our team at Classic Aire Care for all your home comfort needs.
To schedule an appointment, contact us at 314-300-6755 today!
for Ballwin, MO
Our Reviews by City
Again, Jeff did an excellent job for us
Janet - Ballwin, MO
Jeff replaced the coil on our air conditioner very recently. He came back to check everything and to clean the outside unit.
Janet - Ballwin, MO
Jeff and Classic Aire did a wonderful job for us. We needed a new coil. Jeff spent over 4 hours getting the damaged coil out and the new coil installed. Throughout the process, he was good-natured and pleasant. I am impressed with the way Classic Aire calls when they say they will and lets us know when when the technician is on the way. thank you.
Excellent response time
Tom - Ballwin, MO
Had a service Interruption on one of the holidays and service response was within 3 to 4 hours.
Very impressed with John Murphy
Gus - Ballwin, MO
The new travel video is very impressive! I don't know how costly this service is but it sure is helpful in knowing when the person will arrive.
Carolyn - Ballwin, MO
Professional work. Spent the time to do a good job
Jim - Ballwin, MO
Stephen - Ballwin, MO
You guys are always the best!!!
Merry Kweiter - Ballwin, MO
Always the best experiences with this company. Honest, transparent, and easy to work with.
Great & friendly service.
Ralph - Ballwin, MO
Martin - Ballwin, MO
Natalie - Ballwin, MO
Pam - Ballwin, MO
The service was very thorough and the technician was professional and friendly.
Jeff was very professional and extremely knowledgable.
Ron - Ballwin, MO
very fast response
John - Ballwin, MO
excellent service and professional work
Always great service, but...
Susan - Ballwin, MO
We had a zoning system installed in May of 2016. Today (3/5/18) we had to replace a damper, of which the damper was covered under warranty, but we paid $152 for labor. I am disturbed that a part such as a damper cannot last even two years. It makes me worry about future problems with dampers, and how much extra we'll have to pay to keep the zoning system functional. Otherwise, we've been using Classic Aire Care for many years, and are pleased with the service.
Great and quick check
Janet - Ballwin, MO
Jeff did a fine job for us today. He arrived when expected, was friendly and courteous, checked what he needed to check, and just left a few minutes ago. Thank you!
Kathleen - Ballwin, MO
excellent service, answered all of client's questions, prompt, courteous.
Anna - Ballwin, MO
excellent representative of your company
Stacy - Ballwin, MO
great service as usual from Tom
Virginia - Ballwin, MO
Sharon was so nice on the phone and Tom did a very good job to get our heat back on. We have been pleased with Classic Aire Care for years. Thanks
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Checked filter. Blower: 3.1/ A . Inducer: .30/ . Gas pressure: 1.8/3.5 inches water column. Temperature rise: 44 . Supply:1: 119 . Return: 75 .
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Compressor:9.5A . Condenser fan: 0.5A . Blower: 2.1A. ambient: 89. liquid line: 93 . suction line: 45. metering device: TXV. Return air: 69. supply air: 47 .
Customer complaint: high gas bills and I electric bills. New equipment November 2017. Air filter very dirty. I replaced air filter. Tested stage two cooling: 21 degree temperature drop. Jumper W915 to enable first stage cooling. Checked temperature drop: 21. Check and adjust subcooling. Rem: .5. Compressor:6.65/9.15 . Condenser fan: 1.24A . Blower: 850,1100 . ambient: 86. metering device: TXV . Suction pressure: 118, sh:16 . head pressure: 311, sc:7, coil dirty. Return air: 72.5 . supply air: 51 . wet bulb: 59. Checked heat operation. Fine tuned gas pressures. Blower: 800/1000 . Inducer: 0.24A/ . Gas pressure:2.2/3.9 inches water column.
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. First floor system: closed 2 basement vents to help kitchen air flow. Compressor: 15.1A. Condenser fan: 1.25A . Blower: ad. 7.3A . ambient: 75 . liquid line: 79 . suction line: 50 . metering device: piston . Suction pressure:62(35). Return air: 73. supply air:55 . wet bulb: 60 . Second floor system: Compressor: 5.6A . Condenser fan: 0.77A . Blower: adjust for proper td: 3.3A . ambient: 75 . liquid line: 74, now: 83. suction line: 69(40) . CC: 40. Rem: 2.5. metering device: piston . Suction pressure: now: 68(39) . head pressure: 176(92). Return air:73 . supply air: 55. wet bulb: 60. Work suggested: air filters to be delivered. Replace first floor air filter soon. Close more first floor vents in front rooms to help kitchen airflow. Also, try offsetting second floor 2 degrees higher than
I found low-voltage wire in condensing unit rubbed against high voltage terminal, causing contactor coil to burn out. Also caused control voltage fuse at furnace circuit board to blow and caused burn spot at resistors on furnace control board. I tested furnace control board in cooling and heating mode. Working OK! I tested thermostat in cooling and heating mode. Working OK. I replaced contactor in condensing unit. Condenser coil was very dirty. Cleaned and checked air conditioner per PMA purchase. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Back-flushed condenser coil with Water-Saber. Re-checked Freon pressures. OK. SH: T+9.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Replaced air filter. Compressor: 15.6A . Condenser fan: 1.0A . Blower: 5.7A . ambient: 86 . liquid line: 104, dirty . suction line: 56 . metering device: TXV. Return air: 74. supply air: 50 . wet bulb: 59. Found dual run capacitor weak: 14%low. Replaced capacitor and tested amp draw. Back-flushed condenser coil with Water-Saber.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Replaced air filter. Checked Freon level: low. System is 20 to 25% low. Compressor: 16.7A . Condenser fan: 1.18A . Blower: 7.4A. ambient: 84. liquid line: 106 . suction line: 60 . metering device: TXV . Suction pressure: 110(36). Return air: 70.5 . supply air: 57 . wet bulb:59 . Installed customer supplied Nest stat. Setup wifi. Work suggested: Freon leak search: $189. Freon leak repair: $?
No cool-blown dual cap-sign up for maintenance plan and performed first visit!
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Condenser coil very dirty! Back-flushed condenser coil with Water-Saber. Compressor: 13.8A . Condenser fan: 1.24A . Blower: 5.3A . ambient: 90 . liquid line: 98 . suction line: 60 . metering device: piston . Suction pressure: 78(47) . Return air: 75 . supply air: 57.5 . wet bulb: 63 .
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Compressor: 5.7A . Condenser fan: 0.31A . Blower: 1.5A, 800 . ambient: 86. liquid line: 87 . suction line: 58. metering device: TXV . Suction pressure: 129(44.5) . head pressure: 305(97). Return air: 78 . supply air: 57 . wet bulb: 65 .
AC maintenance for both home systems today!
Replaced evaporator coil!
Replaced evaporator coil!
I found condensate drain tubing clogged. I replaced drain tubing and fittings with larger size. Treated system with antibacterial. I also found system in need of cleaning. Cleaned and checked air conditioner per maintenance plan purchase. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Back-flushed condenser coil with Water-Saber and retested Freon: low! Topped off with R-22 Freon. Compressor: 15.45A. Condenser fan: 1.35A . ambient: 78 . liquid line: 88. suction line: 38. metering device: piston . Suction pressure: 65(38) . Return air: 68. supply air: 48 . wet bulb:58 .
AC maintenance today! Running great!
Ac maintenance. Found leak in evaporator coil
cleaned & checked A/C & performed Ameren post data efficiency analysis. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Found dual run capacitor weak: 18%low. Replaced capacitor and tested amp draw. Checked Freon level. Topped off with 1#, R22. Cleaned condenser coil. Compressor: 8.4A. Condenser fan: 0.97A . Blower: 5.8A . ambient: 80 . liquid line: 90 . suction line: 52. metering device: TXV . Suction pressure: 68(39) . head pressure: 185(96) . Return air: 70 . supply air: 48 . wet bulb: 58.7 .
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Checked filter. AH tonnage: ? Compressor: 8.5A. Condenser fan: 0.70A. ambient: 81 . liquid line: 92 . suction line: 34 . metering device: piston . SH: 0 . Return air: 70.5 . supply air: 49.5. wet bulb: 60 . Cleaned condenser coil.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Compressor: 8.5A . Condenser fan: 1.2A. Blower: adj. 1350 . ambient: 79. liquid line: 81 . suction line: was61 . metering device: TXV . Suction pressure: was 115(39). Return air: 71.5 . supply air: 54 . wet bulb:60 . Moved bulb. Supply: 53. Suction line: 57. Water heater is apparently releasing water from pressure relief valve intermittently. Needs expansion tank installed. Work suggested: expansion tank for water heating system.
Replaced evaporator coil under parts warranty