Ballwin Plumbing, HVAC & Insulation Services
Located west of St. Louis, Ballwin is a small city with just over 30,000 people that was first formed in 1837. At Classic Aire Care, we are proud to offer our neighbors in Ballwin a wide selection of quality home comfort services, including:
- Heating and air conditioning
- Plumbing and drain services
- Energy efficiency and insulation services
- Indoor air quality services
- 24-hour emergency services
- And more!
Whether you live near New Ballwin Park or Ballwin Golf Course, our team of dependable and knowledgeable professionals is available at any time to handle all your HVAC, plumbing, and home comfort needs.
Contact Classic Aire Care at 314-300-6755 to request an estimate or to schedule an appointment!
Heating and Air Conditioning Services in Ballwin
At Classic Aire Care we offer a variety of heating and cooling services, including:
- Heating services: From replacing a thermocouple or changing an air filter, to repairing a flue or replacing the blower motor, our team can handle all your heating system maintenance, repair, and replacement needs.
- Air conditioning services: Whether you have a refrigerant leak or major compressor problems, our team can diagnose your air conditioning system quickly and provide affordable repair options. We also offer complete maintenance and replacement services, as well as convenient preplanned maintenance agreements.
- Emergency services: If your heating or air conditioning system breaks down after standard business hours, you can receive the help you need anytime with our 24-hour emergency HVAC repair service!
Our HVAC professionals are NATE certified, and are familiar with all common HVAC equipment, including furnaces, boilers, heat pumps, central air conditioners, ductless systems, packaged systems, air handlers, and more.
For HVAC repairs or maintenance, contact us today!
Plumbing Services in the Ballwin Area
Whether you have a minor faucet leak, a clogged sewer pipe, or a frozen water line, our team at Classic Aire Care can help. We provide a full selection of plumbing and drain services, including:
- Water, sewer, and drain pipe repair
- Pipe installation and replacement
- Gas line repair and replacement
- Sewer and drain cleaning
- Clog removal
- Trenchless pipe repair and relining
- Leak detection
- Backflow testing
- Fixture and faucet installations
- Toilet repair and replacement
- 24-hour emergency services
- And more!
Our plumbing professionals are available at any time, through our 24/7 emergency plumbing service, and they have the tools and experience necessary to solve nearly any pluming problem.
For help with your plumbing system, contact us today for service anywhere in Ballwin, from Kehrs Mill Road to Henry Avenue and anywhere in between!
Home Energy and Air Quality Services
If you home lacks insulation, has drafty windows, or is not properly sealed form air intrusion, your indoor air quality may suffer and your costs for heating and cooling will be unnecessarily high. At Classic Aire Care, we offer a variety of indoor air quality and home energy services that can improve your comfort and reduce your energy costs. These include:
- Home energy audits
- Programmable thermostat installations
- Insulation services
- Air sealing services
- Air purifier and air cleaner installation and maintenance
- Humidifier and dehumidifier installation and maintenance
- Ventilation system installation and repair
- And more!
To learn more about reducing your energy usage, talk to our team at Classic Aire Care today!
Call Today For Plumbing & HVAC Services in Ballwin
From HVAC maintenance and repair, to plumbing, drain, energy efficiency, and air quality services, you can trust our team at Classic Aire Care for all your home comfort needs.
To schedule an appointment, contact us at 314-300-6755 today!
for Ballwin, MO
Our Reviews by City
Stephen - Ballwin, MO
You guys are always the best!!!
Merry Kweiter - Ballwin, MO
Always the best experiences with this company. Honest, transparent, and easy to work with.
Great & friendly service.
Ralph - Ballwin, MO
Martin - Ballwin, MO
Natalie - Ballwin, MO
Pam - Ballwin, MO
The service was very thorough and the technician was professional and friendly.
Jeff was very professional and extremely knowledgable.
Ron - Ballwin, MO
very fast response
John - Ballwin, MO
excellent service and professional work
Always great service, but...
Susan - Ballwin, MO
We had a zoning system installed in May of 2016. Today (3/5/18) we had to replace a damper, of which the damper was covered under warranty, but we paid $152 for labor. I am disturbed that a part such as a damper cannot last even two years. It makes me worry about future problems with dampers, and how much extra we'll have to pay to keep the zoning system functional. Otherwise, we've been using Classic Aire Care for many years, and are pleased with the service.
Great and quick check
Janet - Ballwin, MO
Jeff did a fine job for us today. He arrived when expected, was friendly and courteous, checked what he needed to check, and just left a few minutes ago. Thank you!
Kathleen - Ballwin, MO
excellent service, answered all of client's questions, prompt, courteous.
Anna - Ballwin, MO
excellent representative of your company
Stacy - Ballwin, MO
great service as usual from Tom
Virginia - Ballwin, MO
Sharon was so nice on the phone and Tom did a very good job to get our heat back on. We have been pleased with Classic Aire Care for years. Thanks
Chris - Ballwin, MO
Charlie - Ballwin, MO
Richard - Ballwin, MO
Arrived within time estimate. Brian did a very thorough job.
Sandra - Ballwin, MO
I received the excellent service I have come to expect from Classic Aire. The technician was on time, courteous, friendly, and professional. Bravo to Classic Aire and their staff members!
Robin - Ballwin, MO
He arrived on time. He was friendly and professional. He put the doors back the way he found them, which some service persons do not. I have to assume he did a good job. I don't know how to assess that since I don't know how to do what he does.
Ernest - Ballwin, MO
Second floor system: 7274: I found blower capacitor very weak: 97% low. I also found system low on Freon. Also, air-conditioners are in need of cleaning! I replaced blower capacitor and topped off Freon level per customer request. Work suggested: Maintenance plan: two systems: $318. Freon leak search: $189. Freon leak repair: $?
I found dual capacitor bad: open circuit on compressor side. Replaced dual capacitor. Tested cooling operation. Suction: 74 (44). Suction line: 70. Liquid line: 102. Ambient: 78. Wet bulb: 67.
Replaced evaporater coil
No answer at the door. Checked at outdoor unit. Appears to be icing up.
Replaced bad capacitor on ac
Work done: Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Set 2nd floor damper for summer. Compressor: 16.8A .Condenser fan: 1.3A . Blower: 6.8A .ambient: 71.liquid line: 78.Crankcase: dry. suction line: 34 .wet bulb: 60. Relative humidity: 57%. Work suggested: set a fan to “auto“ for best dehumidification when in the cooling mode. Found basement pressure negative (-.017 inches water column) due to leaks in return-air ducting. This is causing downdraft of flu and fluegas spillage at water heater.
Spring maintenance on new ac system!
Spring maintenance for both AC systems!
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Adj blower. 800. Tested capacitors. Checked Freon level: low. Compressor: 5.0A .Condenser fan: .83A . Blower: 800cfm .ambient: 77.metering device: TXV . Suction pressure: 107 .head pressure: 265. Superheat: 29. Sub cooling: zero. Work suggested: Freon leak search: $189. Freon leak repair: $?
Found wet-switch tripped again. I discovered a hairline crack on the underside of PVC trap!! Trap is slowly dripping water! I rebuilt trap with fittings and piping off of truck.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Replaced air cleaner media. Compressor: 9.9A .Condenser fan: 1.3A. Blower: 7.2A.ambient: 68 .liquid line: 68 .suction line: 50.metering device: piston . Suction pressure: 65(38) .head pressure: 156(85) . Return air: 72 .supply air: 54.wet bulb: 61 . SH: T+8.
I found wet-switch in attic tripped. Found water in safety pan under the air handler. I found PVC drain trap dry! Also, found condensate pump functional. Unit apparently could not drain due to try trap, causing air handler to leak water into safety pan. I reset wet-switch, I primed trap with water, observed operation. Draining and pumping OK.
Installed reme halo UV light for HD employee special!
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter: .42” drop. Run time: 97/3. Compressor:5.9/8.8A .Condenser fan: 1.15/1.55A . Blower: /5.8A .ambient: 54 .liquid line: 55 .suction line: 42.metering device: TXV . Return air: 67.supply air: 44.5.wet bulb:55 . Work suggested: replace air cleaner media.
First floor system: 0 superheat from TXV: I pumped down system. I pumped oil back into the compressor. I brazed in new thermostatic expansion valve, using nitrogen purge. I evacuated system low side. Tested Freon level. Sub cooling: nine. Superheat: 4. Head pressure: 231 (79). Suction: 103 (33). Parts and labor warranty.
Maintenance for whole HVAC system!
Found system low on Freon again. I recharge system with 2 pounds, R-22 Freon. Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Cleaned condenser coil. Compressor: 8.65A.Condenser fan: .78A .ambient: 66 .liquid line: 74 .suction line: 32.metering device: cap tube . Suction pressure: 57(32). Expect Freon to leak back out.
Serviced air conditioner and replaced filter
Spring maintenance on AC system!