HVAC & Plumbing Contractor in Chesterfield, MO
Comfort is important for many Chesterfield homeowners, and this requires a reliable HVAC system, good air quality, and a quality plumbing system. When problems do happen, you need a company you can trust to diagnose the cause and repair the plumbing or HVAC system quickly and affordably.
With over 90 years of service in the Chesterfield and St. Louis County area, our team at Classic Aire Care has the experience and knowledge necessary to solve nearly any HVAC or plumbing problem you may encounter. We offer both residential and commercial service throughout the Chesterfield area, including heating, air conditioning, plumbing, insulation, energy efficiency, and air quality services.
For more information about our company culture, contact us at (314) 300-6755 today!
Why Choose Us as Your Chesterfield HVAC & Plumbing Contractor?
As a customer of Classic Aire Care, you can expect:
- Happy, helpful, and timely service
- Respect for your property
- Top-notch technicians
- Superior product quality
- 100% satisfaction guarantee
Read more about our company values and see our mission statement here.
Heating & Air Conditioning Services in Chesterfield, MO
At Classic Aire Care, our NATE-certified professionals are familiar with all common types of HVAC equipment, including furnaces, boilers, heat pumps, central air conditioners, packaged systems, ductless mini-splits, rooftop AC units, process coolers, and more. We provide complete HVAC services in Chesterfield, including:
- New installations: Installation of HVAC equipment in new construction, including system design, sizing, duct installation, equipment installation, and installation of accessories, like thermostats.
- System replacements: Removing old HVAC equipment and sizing and installing modern versions—typically with greater efficiency, improved comfort, and new technologies like zoning or Wi-Fi thermostats.
- Routine maintenance: Annual or semi-annual maintenance that includes tasks like replacing air filters, cleaning coils, cleaning burners, checking refrigerant levels, and inspecting electrical and safety systems. This helps to improve efficiency and prevent future problems, and our optional planned maintenance agreements make the process simple.
- Repairs: Consisting of basic repairs like replacing belts or faulty gas valves, to major repairs like replacing blower motors or compressors. We offer the best repair options for your needs and budget.
- 24-hour emergency HVAC service: When problems happen after business hours, our technicians are available at any time, day or night, for major or minor repairs.
Air Conditioning Services
Our technicians are trained to service traditional units, ductless mini-splits, heat pumps, or commercial HVAC equipment. Our services include:
- Air conditioner repair service
- Air conditioner installation and replacement
- Air conditioner maintenance
- 24-hour emergency air conditioning service
- Heat pump repair, installation, and maintenance
- Air handler repair, installation, and maintenance
- Ductless AC system installation, repair, and maintenance
- Planned maintenance agreements for cooling systems
Our NATE-certified technicians install thermostats, clean burners, replace blower motors, change air filters, and more. Additional heating services include:
- Furnace replacement
- Furnace repair
- Cleaning and repairing the air handler
- Boiler service, repair, or replacement
- Ductless heating services
- Heat pump repair, installation, or maintenance
- Planned maintenance agreements for heating systems
To learn more about our HVAC services, contact our team today!
Chesterfield Plumbing Services
When plumbing problems happen, you have to take care of them quickly to avoid damage to your home from water, mold, or mildew. At Classic Aire Care, our team of plumbing professionals can take care of nearly any plumbing problem, from a clogged drain to a major leak. Our plumbing services include:
- Gas, water, and sewer pipe repair and installation
- Inspection and maintenance of plumbing systems
- Sewer and drain repair and installation
- Drain and sewer cleaning
- Clog removal
- Installation of grease traps
- Video camera sewer inspection
- Detection and repair of leaks
- Installation and repair of water heaters
- Installation and repair of plumbing fixtures
- Emergency 24-hour plumbing service
- And more!
Regardless of the cause, our team will diagnose your plumbing problems quickly and offer affordable, permanent solutions. Contact us today for a plumbing service appointment!
Insulation, Air Quality & Energy Efficiency Services in St. Louis County
To maximize your comfort and reduce your energy costs, our team at Classic Aire Care offers a variety of other services, including:
- Insulation and air sealing
- Air purifier, air cleaner, and ventilation system installations
- Humidity control using humidifiers and dehumidifiers
- Energy audits
- Programmable thermostat installations
- Duct cleaning, repair, and installation
For more information about improving energy efficiency and comfort, contact our team today!
Call Classic Aire Care for Plumbing & HVAC Services in the Chesterfield Area
From Bellefontaine and Lake to Gumbo and Monarch, our team at Classic Aire Care can handle all your plumbing and HVAC needs in the Chesterfield area, including routine maintenance, repairs, and new installations.
Contact us today at (314) 300-6755 to schedule your plumbing or HVAC service!
Other Cities We Serve
We serve cities throughout the St. Louis area including much of St. Louis, St. Charles, and Jefferson counties. Specific areas we serve include Creve Coeur, Olivette, Maryland Heights, St. Charles, University City, Chesterfield, Clayton, Town and Country, and Overland.
for Chesterfield, MO
Our Reviews by City
Mareen - Chesterfield, MO
John has always been professional and thorough. I always ask for him.
Very nice, efficient and informative!
Peggy - Chesterfield, MO
Alyce - Chesterfield, MO
Kathy - Chesterfield, MO
John Murphy is a great serviceman
Joseph - Chesterfield, MO
Great service by service tech John.
Always Professional and Cordial
Ronald - Chesterfield, MO
What I appreciate best about Classic Air Care is the customer service and clear communications. From the office staff to the technicians, we have never been disappointed and also learn a great deal about our HVAC maintainance.
AC - Chesterfield, MO
Great and friendly service
Leonard - Chesterfield, MO
Came on time. Did a thorough job and was very pleasant and professional
Always Wonderful Service
Maureen - Chesterfield, MO
John Murphy is thorough and I have confidence in him. I always ask for him.
Farrokh - Chesterfield, MO
Shirly - Chesterfield, MO
very informative, however, I am waiting for receipt of piece purchased for my A/C. please send
Dennis - Chesterfield, MO
Classic Aire Care always does a good job and I especially like that they try hard to send out the same technician every time.
Friendly and great service
Susan - Chesterfield, MO
We welcomed John. Trust he did a fine job.
Larry - Chesterfield, MO
He was thorough and found all in order.
Jack - Chesterfield, MO
Professional 10 is the best u can get
Will - Chesterfield, MO
Prompt, friendly and efficient
Howard - Chesterfield, MO
Very satisfied. Would recommend to others.
Always excellent service
Kay - Chesterfield, MO
We have used Classic Aire Care for several years and have never been disappointed. Always a great experience. They are completely transparent with services and costs which makes me much more comfortable dealing with topics I know nothing about.
Gary - Chesterfield, MO
Gary - Chesterfield, MO
Showed up on time; discussed in great detail any issues he found and what he fixed; listened to any other concerns I had and made suggestions.
Great service from a very nice young man.
Sandra - Chesterfield, MO
Jeff came, had the wrong product, but figured it out, ordered the correct product and installed it the same day. Great service.
Fast and great service
Mrs - Chesterfield, MO
Earl - Chesterfield, MO
Classic Aire Care technician quickly found the problem and had my furnace up and running very quickly.
David - Chesterfield, MO
Maintenance was performed on my furnace and everything checked out good. He was here on time and out when finished.
John was very helpful
Lee - Chesterfield, MO
Cleaned & checked 2 gas furnaces, 1 electric furnace, 1 electric package unit. Inspected heat exchangers & flue venting. cleaned burners & flame sensors. Checked voltage & amp draw of motors. Test capacitors. First floor system: Replaced thermostat batteries. Vacuum filter. Blower: 4.4/5.6A . Inducer: 0.31/0.60A. Temperature rise: 39/52 . Supply: 115/128 . Return: 76. Antique room: vacuum filter. Blower: 2.8A. Inducer: 0.95A. Gas pressure: 3.6 inches water column. Temperature rise: 66. Thermostat: 50. Supply: 128. Return: 61 . Second floor system: Replaced thermostat batteries. Vacuum filter. Tested heating elements. Tested sequencer. Checked voltage & amp draw of blower. Test capacitor. Package unit: Tested heating elements. System amp draw: 43.3A. Tested sequencers. Checked voltage & amp draw of blower. Test capacitor. Check temperature rise. 46. Return: 74. Supply: 120.
Clean and check electric furnace. Tested heating elements. 15kw. Tested sequencers. Checked voltage & amp draw of blower. Test capacitor. Total amps: 64. Voltage: 248. Tested thermostat batteries. Checked filter.
Cleaned & checked condensing gas furnace. Inspected heat exchanger with scope. Checked flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Checked drain. Replaced air cleaner media. Clean and check humidifier, replace pad, checked water flow and drain. Blower: 2.6/6.8A . Inducer: 0.95/2.6A . Gas pressure: 1.7/3.6 inches water column. Temperature rise: 63/63 . Supply: 139/141 . Return: 76/78 .
Fall maintenance today for the furnace! Replaced filter and humidifier water panel. Good to go
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Replaced air filter. Blower: 3.7A . Inducer: 1.42A . Gas pressure: 3.4 inches water column. Temperature rise: 51.
Fall maintenance today for the furnace!
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Checked filter. Blower: 3.5/ . Inducer: 0.33/AGas pressure: 3.4 inches water column. Clean and check humidifier, replace pad, checked water flow and drain. Found solenoid valve clogged! Replaced solenoid valve. Replaced drain tubing.
Cleaned & checked condensing gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Checked filter. Clean and check humidifier, replace pad, checked water flow and drain. Blower: 4.0/5.1A . Inducer: 0.33/0.59A. Cut W915. I enabled 2 stage cooling operation.
Clean and check electric furnace. Tested heating elements: 100A . Tested sequencers. Checked voltage & amp draw of blower: 3.2A. Test capacitor: 16% low. Checked filter. Clean and check humidifier, replace pad, checked water flow and drain. Water is dripping off of evaporator coil in air handler/furnace. Checked temperature drop of AC: T+2. Air-conditioner in need of maintenance. May need Freon added. May need chemical cleaning of evaporator coil to prevent water from dripping off of coil. Or, possibly replacement coil if available. Need to schedule air-conditioner maintenance next spring. Customer complaint of high electric bills during winter. Project manager to price heat pump system.
Furnace and ac maintenance today!
Second floor system: 1343: I found blower run capacitor extremely weak, causing motor to overheat and system to ice up. I replaced blower capacitor and tested cooling operation. Found dual run capacitor in condensing unit 22% oversized. Replaced with proper size capacitors. First floor system:3470: has bad compressor. Shorted to ground. Kitchen system: missing air filter. I installed air filter and set blower speed. Work suggested: Project manager is scheduled to price new air conditioner for first floor system. Recommend maintenance plan for three systems: $447
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Replaced air filter. Compressor: 14.6A. Condenser fan: . Blower: 7.8A . ambient: 75 . liquid line: 79 . suction line: 53 . metering device: TXV . Return air: 76 . supply air: 53 . wet bulb: 62 .
Heating maintenance for furnace! Also cleaned air conditioner
I found contactor points stuck closed! I replaced contactor. Cleaned out drain pan outlet. Removed deteriorating putty from Plenum. I checked Freon level and found about 10% low. I topped off Freon for proper superheat level: chart-10.
cleaned & checked 2 A/Cs & performed Ameren post data efficiency analysis. Both systems low on Freon and Condenser coils were extremely dirty. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Rechecked Freon levels. Cleaned condenser coils. Second floor system: 4063: Found run capacitor weak: 14&36%low. Found system very low on Freon. Compressor: 6.0A . Condenser fan: 0.82A . Blower: 4.2A . ambient:78 . liquid line: 85 . suction line: 67 . metering device: TXV . Suction pressure:93(28) . head pressure: 254(85) . Return air: 70.2 . supply air: 57.6 . wet bulb:59.5 . Saturation temperature is currently 28. May ice up. Currently cooling at 77% capacity. First floor system: Compressor:10.25A . Condenser fan: 1.25A . Blower: 5.0A. ambient: 78 . liquid line: 90 . suction line:55 . metering device: TXV . Suction pressure: 117(39) . head pressure: 275(90). Return air: 68.6 . supply air: 49.4. wet bulb:58 . System a lit
Second floor system: 5223: Found burnt wire and terminal at dual run capacitor. Replaced capacitor and tested amp draw of motors. Checked filter. Checked Freon level. First floor system: 5897: Found low on Freon. Topped off with R22 Freon per superheat chart. Expect Freon to leak back out. Work suggested: Freon leak search: $189. Freon leak repair: $? John C. to price new AC Friday at 1:00.
AC Maintenance for both AC systems- good to go
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Compressor: 8.65A. Condenser fan: 0.83A . Blower: 4.7A, 1210 . ambient: 82. liquid line: 91 . suction line: 57 . metering device: TXV . Suction pressure: 120(41). head pressure:308(98) . Return air: 70.5 . supply air: 53.5 . wet bulb: 62. RH: 63%. Work suggested: set fan switch to “auto” when in cooling mode for proper dehumidification.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Found blower run capacitor weak. Replaced capacitor under parts and labor warranty and tested amp draw. Found condenser fan run capacitor weak: 40%low! Replaced capacitor and tested amp draw. Checked Freon level. Replaced air filter. Compressor: 15.1A. Condenser fan: . Blower: 5.2A, mh. ambient: 80. suction line: 40 . metering device: piston . Suction pressure: 68(40) . Condenser coil very dirty. Cleaned condenser coil.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Compressor:11.2A . Condenser fan: 0.83A. Blower: 5.1A . ambient: 79 . liquid line:84, dirty . suction line: 52 . metering device: TXV . Suction pressure: 114(38) . Return air: 70.5 . supply air: 53.5 . wet bulb: 61 .
Ac system maintenance for all 4 systems! Good to go
Replaced evaporator coil and performed AC maintenance on both systems
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Replaced thermostat batteries. Replaced air filter. Compressor: 8.7A. Condenser fan: 0.55A. Blower: 7.4A . ambient: 68 . liquid line: 75 . suction line: 55 . metering device: TXV . head pressure: 250+. Return air: 75 . supply air: 56. Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Blower: 5.4A,MH. Inducer: 1.0A . Gas pressure: 3.4 inches water column. Temperature rise: 52 . Supply: 130. Return: 78 . Blower motor amp draw is high: 28% over RLA. Expect motor windings failing. Repair declined at this time. Work suggested: replace blower motor: $544.