Professional HVAC & Plumbing Services in Chesterfield, MO
Comfort is important for many Chesterfield homeowners, and this requires a reliable HVAC system, good air quality and a quality plumbing system. When problems do happen, you need a company you can trust to diagnose the cause and repair the plumbing or HVAC system quickly and affordably.
With over 90 years of service in the Chesterfield and St Louis County area, our team at Classic Aire Care has the experience and knowledge necessary to solve nearly any HVAC or plumbing problem you may encounter. We offer both residential and commercial service throughout the Chesterfield area, including heating, air conditioning, plumbing, insulation, energy efficiency and air quality services.
For more information about or services, contact us at 314-300-6755 today!
Heating & Air Conditioning Services in Chesterfield, MO
At Classic Aire Care, our NATE-certified professionals are familiar with all common types of HVAC equipment, including furnaces, boilers, heat pumps, central air conditioners, packaged systems, ductless mini-splits, rooftop AC units, process coolers, and more. We provide several HVAC services including:
- New installations: Installation of HVAC equipment in new construction, including system design, sizing, duct installation, equipment installation and installation of accessories, like thermostats.
- System replacements: Removing old HVAC equipment, sizing and installing modern versions, typically with greater efficiency, improved comfort and new technologies like zoning or Wi-Fi thermostats.
- Routine maintenance: Annual or semi-annual maintenance that includes tasks like replacing air filters, cleaning coils, cleaning burners, checking refrigerant levels, and inspecting electrical and safety systems. This helps to improve efficiency and prevent future problems, and our optional planned maintenance agreements make the process simple.
- Repairs: Consisting of basic repairs like replacing belts or faulty gas valves, to major repairs like replacing blower motors or compressors. We offer the best repair options for your needs and budget.
- 24-hour emergency HVAC service: When problems happen after business hours, our technician are available at any time, day or night, for major or minor repairs.
To learn more about our HVAC services, contact our team today!
Chesterfield Plumbing Services
When plumbing problems happen, you have to take care of them quickly to avoid damage to your home from water, mold or mildew. At Classic Aire Care, our team of plumbing professionals can take care of nearly any plumbing problem, from a clogged drain to a major leak. Our plumbing services include:
- Installation and repair of sewer, drain, water and gas lines
- Sewer and drain cleaning
- Clog removal
- Fixture installation and repair
- Toilet repair and emplacement
- Leak detection
- Camera pipe inspections
- Backflow testing
- Grease trap plumbing
- Water heater replacement and repair
- Plumbing system inspections and maintenance
- 24-Hour emergency plumbing service
Regardless of the cause, our team will diagnose your plumbing problems quickly and offer affordable, permanent solutions.
Contact us today for a plumbing estimate!
Insulation, Air Quality & Energy Efficiency Services for St. Louis County
To maximize your comfort and reduce your energy costs, our team at classic aire care offers a variety of other services, including:
- Insulation and air sealing
- Air purifier, air cleaner and ventilation system installations
- Humidity control using humidifiers and dehumidifiers
- Energy audits
- Programmable thermostat installations
- Duct cleaning, repair and installation
For more information about improving energy efficiency and comfort, contact our team today!
Call Classic Aire Care for Plumbing & HVAC services in the Chesterfield Area
From Bellefontaine and Lake, to Gumbo and Monarch, our team at Classic Aire Care can handle all your plumbing and HVAC needs in the Chesterfield area, including routine maintenance, repairs and new installations.
Contact us today at 314-300-6755 to schedule your plumbing or HVAC service!
for Chesterfield, MO
Our Reviews by City
Always Wonderful Service
Maureen - Chesterfield, MO
John Murphy is thorough and I have confidence in him. I always ask for him.
Farrokh - Chesterfield, MO
Shirly - Chesterfield, MO
very informative, however, I am waiting for receipt of piece purchased for my A/C. please send
Dennis - Chesterfield, MO
Classic Aire Care always does a good job and I especially like that they try hard to send out the same technician every time.
Friendly and great service
Susan - Chesterfield, MO
We welcomed John. Trust he did a fine job.
Larry - Chesterfield, MO
He was thorough and found all in order.
Jack - Chesterfield, MO
Professional 10 is the best u can get
Will - Chesterfield, MO
Prompt, friendly and efficient
Howard - Chesterfield, MO
Very satisfied. Would recommend to others.
Always excellent service
Kay - Chesterfield, MO
We have used Classic Aire Care for several years and have never been disappointed. Always a great experience. They are completely transparent with services and costs which makes me much more comfortable dealing with topics I know nothing about.
Gary - Chesterfield, MO
Gary - Chesterfield, MO
Showed up on time; discussed in great detail any issues he found and what he fixed; listened to any other concerns I had and made suggestions.
Great service from a very nice young man.
Sandra - Chesterfield, MO
Jeff came, had the wrong product, but figured it out, ordered the correct product and installed it the same day. Great service.
Fast and great service
Mrs - Chesterfield, MO
Earl - Chesterfield, MO
Classic Aire Care technician quickly found the problem and had my furnace up and running very quickly.
David - Chesterfield, MO
Maintenance was performed on my furnace and everything checked out good. He was here on time and out when finished.
John was very helpful
Lee - Chesterfield, MO
Ronald - Chesterfield, MO
Actual Working Humidifier
Brenda - Chesterfield, MO
Jeff arrived ahead of schedule, quickly removed old humidifuer and installed the new one. Great job!
Wonderful customer service!
Mrs Hargrave - Chesterfield, MO
Dave's expert customer service is why we request him each time. Hang onto this guy. He is a valuable employee!!
Great Service, Great Price!
Brenda - Chesterfield, MO
Brian was prompt, professional, very efficient in handling my needs. I am extremely satisfied and confident in his performance.
Very thorough in his work
Sharon - Chesterfield, MO
I am very satisfied with the service Patrick provided on my heating system.
John Murphy is the best!
Kathy - Chesterfield, MO
Tom always does a great job and is ready to answer any questions I might have!
Peggy - Chesterfield, MO
I think Classic Aire is great - always courteous, polite and helpful.
Tom - Chesterfield, MO
Tom has been our service technician since we have been at our present location. He takes care of our Furnace/AC like it is his own. In short he does an Excellent job!!!!!
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Compressor: 20.3A .Condenser fan: 1.57A . Adj Blower: 1700 .ambient: 74 .suction line: 34 .metering device: Piston . Suction pressure: 60(34) . Return air: 72 .supply air: 52 .wet bulb:61 .
Work Done: Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Compressor: 9.9A .Condenser fan: 0.75A . Blower: 3.0A .ambient: 73.suction line: 45 .metering device: piston. Suction pressure: 74 .wet bulb: 61. Work Suggested: customer declined leak search at this time.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Replaced air filter. Adjust blower for 350cfm. Compressor: 11.5A .Condenser fan:0.8A . Blower: 6.3A@1600 .ambient: 85 .liquid line: 89. suction line: 53. metering device: TXV. Return air wet bulb: 58 . Found basement pressure negative (-.02 inches water column) due to leaks in return-air ducting. This is causing downdraft of flu and fluegas spillage at water heater. Customer keeps basement door open. Customer plans to seal leaks in return air ducting.
Replaced ac fan motor and performed ac maintenance
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Replaced air filter. Compressor: 7.3A.Condenser fan: 1.0A . Blower: 3.1A .ambient: 70.liquid line: 74 .suction line: 65. metering device: piston . Suction pressure: 65(38). wet bulb: 64 . SH: T+6.
Spring maintenance for both home systems!
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Replaced air cleaner media. Compressor: 10.6A .Condenser fan: 2.1A . Blower: 1125/1600.ambient: 69 .liquid line: 71 .suction line: 55 .metering device: TXV . Suction pressure: 113(37) .head pressure: 237(80). Return air: 70. supply air: 47 .wet bulb: 57 .
Cleaned and checked 3 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. First floor system: Compressor: 9.4A.Condenser fan: 0.9A . Blower: 4.7A .ambient: 69 .liquid line: 74. suction line:54 .metering device: TXV . Return air: 74 .supply air: 54 .wet bulb: 62. Second floor system: Compressor: 8.3ACondenser fan: 0.8A. ambient: 70 .liquid line: 74. suction line: tt .metering device: TXV . Return air: 74.supply air: 53 .wet bulb: 61. Package unit: Replaced air filter. metering device: piston. Return air: 71 .supply air: 54 .wet bulb:61.
Spring maintenance on ac system! Replaced weak dual capacitor for condenser
Spring maintenance on ac system! Renewed maintenance plan!
Spring maintenance for ac system! Replaced pitted contactor
Spring maintenance on AC system!
No heat—bad ignitor—found heat exchangers with cracks...getting FREE estimate to replace
Spring maintenance performed!
Work Done: Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. I installed low-level carbon monoxide monitor for second floor. Second floor system: Compressor: 3.6A .Condenser fan: .82A .ambient: 40 .liquid line: 41 .suction line: 36 .metering device: piston . Return air:64 .wet bulb: 50 . Removed and flushed drain trap. First floor system: Compressor: 8.3A .Condenser fan: .83A .ambient: 40. liquid line: 43.suction line: 42.metering device: TXV . Return air: 64.supply air:stg1, 36 .wet bulb: 50 .
I tested humidifier operation. Checked water flow and drain. Checked motor. OK. Inlet temperature: 125. Outlet temperature: 105. I set up i-comfort thermostat to precision humidification mode, allowing humidifier to run when needed without a call for heat. I checked thermostat humidity reading. Reads 3 to 6 points low. I calibrated humidity reading +3 points. Work suggested: replace humidifier water panel annually for best performance.
Replaced steam humidifier canister and O-ring
Replaced warranty inducer motor
Replaced inducer motor
Carrier gas furnace replaced humidifier control board added #50 relay
New second floor furnace installed today. Second floor furnace working OK. I found gas shut off to first floor furnace. Turned on gas and installed new filter. Customer said wrong furnace was replaced!! She said another company condemned furnace for heat exchanger failure. I shut the gas valve back off. Customer is contacting Jeff Q.
New second floor furnace installed today. Second floor furnace working OK. I found gas shut off to first floor furnace. Turned on gas and installed new filter. Furnace was apparently turned off for changing filter and was not turn back on.
Carrier gas furnace replaced furnace transformer disconnected humidifier circuit due to shorted control board
Circuit board shows code 32. I found low-fire pressure safety switch contacts sticking open! Do you part deliver to job. I replaced set of pressure safety switches and tubing. Tested operation of furnace. Blower: 6.0/7.6A . Inducer: .49/.93A. Gas pressure: 1.7/3.6 inches water column. Temperature rise: 56/61 . Supply: stg1:128 . Return: 70 . Humidifier dripping water. Clean and check humidifier, replace pad, checked water flow and drain.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Replaced air filter. Compressor:11.8A .Condenser fan: 1.9A . Blower: 1600 .ambient: 71.liquid line: 76 .suction line: 49 .metering device: TXV . Return air: 65.5 .supply air: 42.5 .wet bulb:52 .