Professional Foristell, MO HVAC & Plumbing Contractor
Our customers have trusted Classic Aire Care for all HVAC services for over 90 years. Whether you need to complete your annual maintenance or are looking for a new furnace and air conditioner, Classic Aire Care is only a phone call away. Whether you are in a brand new home or one of Foristell’s charming older homes, Classic Aire Care is here for you with 24 hour emergency service.
Classic Aire Care has received 1000s of 5 star reviews from new and existing customers. With one of the best reputations in the Foristell area, Classic Aire Care has the trained and certified technicians and installers to get the job done. Our highly trained, licensed service technicians and installers get the job right the first time. If you live in Foristell and you need a furnace or air conditioner repair, maintenance or install call us at 314-300-6755.
for Foristell, MO
Our Reviews by City
Coleen - Foristell, MO
Jeff was thorough, polite, very knowledgable, and an excellent representative of your company. We have always been very satisfied with all of your technicians.
John - Foristell, MO
Always great service and explains everything they did. Very professional and nice.
Furnace maintenance! Replaced filter, humidifier pad, and thermostat batteries
I found compressor capacitor bad: open circuit. Replaced compressor capacitor under parts warranty and tested cooling operation. Compressor:13.4A .Condenser fan: .95A . Blower: .ambient: 88.liquid line: 102 .suction line: 51-54 .metering device: TXV . Suction pressure:128-133 . Return air: 77.5.supply air: 59.5.wet bulb: 67.5.
June 30, 2017: pump down system. Removed evaporator coil and drain pan. Cleaned drain pan and attached to new replacement evaporator. Clean the PVC trap. Evacuate low side. Topped off with 410A Freon.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Checked Freon level. Cleaned condenser coil. Replaced air filter. Reset filter timer. Test capacitors. Found blower run capacitor weak: 15%low. Replaced capacitor and tested amp draw. Compressor: 10.4A .Condenser fan: 1.05A . Blower: 7.8A .ambient: 72 .liquid line: 77 .suction line: 50 .metering device: TXV. Return air: 73.5.supply air: 51 .wet bulb: 60 .
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level: low. Charged system for temporary cooling. Performed system leak search. Found evaporator coil leaking! needs a new coil. Cleaned condenser coil.
Heating maintenance on 2 Lennox heat pump systems
Heat pump maintenance on Rheem system
Heat pump maintenance on Lennox system and humidifier
Furnace maintenance on carrier system and humidifier
Ac maintenance on Rheem heat pump
Maintenance on furnace