Classic Aire Care has been providing heating and cooling services in the Hazelwood area for decades. Whether your furnace needs a tune up or your air conditioner needs replacing, Classic Aire Care has the staff to get the job done. Our highly trained, licensed service technicians and installers get the job right the first time. If you live in the Hazelwood area and you need a furnace or air conditioner repair, maintenance or install call us at 314-300-6755.
There are 25,703 people living in Hazelwood, MO and 10,933 households. Whether you are looking for a system replacement, repair, or need to complete your annual maintenance on your Hazelwood home or business, Classic Aire Care is a phone call away. Head on over to Harry S. Truman Park! We’ll call you when we’re on our way.
for Hazelwood, MO
Our Reviews by City
Great service, always on time,
Shirley - Hazelwood, MO
No Heat Delema!
Vern - Hazelwood, MO
he has helped us several time and is always very good at what he does.
Pamela Leong - Hazelwood, MO
Very fast service response. Efficient, knowledgeable and personable technician. Thank you Patrick.
CsSmith - Hazelwood, MO
I will request future service calls from Classic Aire.
Great customer service
Morton - Hazelwood, MO
Coret took the time to explain how the system works and how to best maintain it for optimum service.
Shirley - Hazelwood, MO
Roger arrived in the time period agreed upon, and did a great job servicing the air conditioner.
Great Professional Service
Jim - Hazelwood, MO
I cannot say that I have ever felt more confident that a technician understood and represented my needs as much I do with Classic Aire Care. He let's us know in advance what may need replacement in the future allowing us time to plan. The technician is very thorough and takes the time for a complete analysis. Thanks for the confidence!
Pamela - Hazelwood, MO
Spring service call was done expertly. Needed to add a piece to control mold and bacteria found. Roger explain the options available for my unit. Purchased one item. All done same day. Great job by Classic Aire Care.
Jayne - Hazelwood, MO
Thanks for the information about the air filter & purifier options.
My experience with Classic Care
Betty - Hazelwood, MO
The service as always was great told me what I needed
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Found run capacitor weak: 11%low. Replaced capacitor and tested amp draw. customer declined humidifier service. Adj Blower: H:3.4A . Inducer: 0.6A . Temperature rise: 61 . Supply: 139 . Return: 78 .
I found condenser coil extremely dirty, requiring chemical cleaning. I performed chemical cleaning of condenser coil. Back flushed coil with water saber. I rechecked Freon pressures. Indoor blower moving excess air. Recommend adjustment. Minor dents to condenser coil fins are insignificant. Causing no problem or efficiency reduction. Electronic air cleaner cells are in need of chemical cleaning. Prefilters should be installed in front of electronic air cleaner cells. Compressor: 8.3A . Condenser fan: 0.43A . ambient: 87. suction line: 55 . metering device: piston . Suction pressure: 79(47). wet bulb:66 . System is cooling OK. Work suggested: chemical cleaning of electronic air cleaner cells. Blower speed adjustment.
No ac service call—dual capacitor shorted on compressor side
Arrived checked in with customer. Checked unit operation to find compressor not running checked power, tested capacitor to find compressor cap out of range. Checked compressor to find open and hot will need to allow compressor to cool. Left unit off at disconnect.Return Sunday, May 28, 2018: Checked filter. Checked blower. replaced bad dual capacitor. Tested operation. Compressor: 9.1 A. Fan motor: .84 A. Ambient: 88. Suction: 143(50). Suction line: 75. Liquid line: 97. Blower: 3.0 A.Lennox Model XC14-036-230-03 Serial 5810H08534
Checked out system found unit low on refrigerant customer to get estimate
Serviced air conditioner and replaced filter
Replaced flue tee
Serviced ac and replaced filter
Serviced air conditioner