Classic Aire Care has been providing heating and cooling services in the Manchester area for decades. Whether your furnace needs a tune up or your air conditioner needs replacing, Classic Aire Care has the staff to get the job done. Our highly trained, licensed service technicians and installers get the job right the first time. If you live in the Manchester area and you need a furnace or air conditioner repair, maintenance or install call us at 314-300-6755.
There are 18,094 people living in Manchester and 7,239 homes. Classic Aire Care would love the opportunity to help you maintain the furnace and air conditioner in your beautiful Manchester home. Annual maintenance is important to ensure your furnace and AC are running properly and everything is working at peak efficiency. Whether you’re looking to repair your current system, or are shopping for a new one, our team of professionals is always ready to assist you. Head over to Margaret Stoecker Park. We’ll call you when we’re on our way!
for Manchester, MO
Our Reviews by City
Elizabeth - Manchester, MO
Sean was very polite and friendly. He attended to his work and explained the problem with my furnace. I felt I could trust in his recommendation.
Terry - Manchester, MO
Sean should be commended for his professionalism and overall customer service skills. He arrived on time, completed the service call in a timely manner and provided a complete overview of the service maintenance items that you completed.
Erin - Manchester, MO
Bill - Manchester, MO
Jeff is a credit to your company.
Superior service by the technician and extremely professional. We are very well satisfied with the work and service that has been done by the company
Bob - Manchester, MO
Quick resolution of problems with A/C
David - Manchester, MO
All seems good
Susan - Manchester, MO
Great, as expected
I found liquid line solenoid valve inside the condensing unit shorted, causing unit to run without a call for cooling. I wired unit to bypass solenoid valve. Valve was only used for efficiency improvement. I found system approximately 30% low on Freon. I topped off partially with 1 pound of R-22 Freon for temporary cooling. Suction: 74(44). Suction line: 68. Expect Freon will leak back out. Recommend replacing air conditioner. Repair cost may apply to new equipment. Project manager is scheduled for before 4 o’clock tomorrow. Need to call customer to confirm a timeframe.
Cleaned and checked 3 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. Checked filters. Bedroom system: Compressor: 11.5A .Condenser fan: 1.45A . Blower: 6.1A .ambient: 76.liquid line: 85. suction line: 40 .metering device: Piston. Return air: 72.supply air: 52.5 .wet bulb:62 . Living room system: Compressor: 11.6A .Condenser fan: 1.2A . Blower: 6.1A,m.ambient: 78 .liquid line: 98.suction line: 39 .metering device: piston . Return air: 71 .supply air: 51.5 .wet bulb: 61 . Rear system: was reconnected earlier today. I found system 75 to 80% low on Freon. If Freon was pumped down properly when unit was disconnected (By others last year) there should be close to a full charge and the air-conditioner. System may have a Freon leak. System uses the older type of Freon that is being phased out. needs R22 Freon charge: $456. Freon leak search: $189. Freon leak repair:
Goodman air conditioner
Maintenance on Lennox heat pump
AC maintenance! Replace filter and weak dual capacitor!
A/C start up on new Lennox install
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. I replaced air cleaner media. I tested zone system and found 1 zone damper not closing for zone two.
Customer complaint: gas bills were higher than last year. I explained that the air conditioner is 50% more efficient, not the furnace. I fine tuned furnace using combustion analyzer. Stage one: manifold: 2.6 inches. Oxygen: 7.4%. CO: 42 ppm. Stack: 349. Supply air: 123. Return air: 69. Temperature rise: 54. Inducer: .08 A. Blower: 4.2 A. Stage two: timing: 12 minutes. manifold: 4.0 inches. Oxygen: 7.7%. CO: 29. Stack: 421. Supply air: 128. Return air: 69. Temperature rise: 59. Inducer: 0.22 A. Blower: 5.2 A.
Scheduled maintenance on a Lennox furnace.
Scheduled maintenance on a Amanda furnace.
Clean and check
Cleaned dirty flame sensor
Clean and check
Replaced a thermostat for a York furnace.
Serviced heating system
Maintenance on Lennox furnace.
Working on Lennox furnace
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Checked filter. Blower: 5.1A . Inducer: 1.0A . Gas pressure: 3.4inches water column. Temperature rise: 56.