HVAC & Plumbing Services in Richmond Heights
Richmond Heights homeowners have to deal with some rather aggressive weather all year round. Since summers are hot and the winter seasons are surprisingly glacial, you need home HVAC systems that are at the top of their class and serviced routinely by leading specialists. At Classic Aire Care Heating, Air Conditioning & Plumbing, we take your comfort needs seriously, offering services and solutions that place your comfort and satisfaction first.
We are a fully licensed, certified, and insured HVAC and plumbing service company in the Richmond Heights and Greater St. Louis area. It’s been nearly a century since we opened our doors, and in that time we’ve always been the specialists you can turn to for the complete heating services, cooling solutions, and maintenance that you need in order to stay comfortable in your home throughout all seasons.
For services you can trust, contact Classic Aire Care online or call 314-300-6755. We provide service for all of Richmond Heights, from West Bruno to Clayton Road!
HVAC Installation & Replacement
How well your home HVAC systems are installed will dictate the level of service and comfort the system can provide for its entire lifespan. That’s why at Classic Aire Care, we take great pains to offer our clients a service that is a cut above. We handle system installations and replacements with exacting detail, from helping you choose the perfect home system all the way to thorough installations and testing. We want you to have the best, and we stop at nothing to ensure our service brings you exactly that and more.
HVAC Repair & Maintenance
Whether it’s an air flow obstruction or slow, grating component wear, any problem at all with your heating or cooling system can lead to miserable days and restless nights. When you need repair services, you need them to be quick and efficient, on top of being wholly accurate. With Classic Aire Care, you can trust that our repair services utilize cutting-edge tools and superior training to get your home back to normal as soon as precision will allow.
To reduce your risks of a breakdown, and to optimize system efficiency and lifespan, take advantage of our full range maintenance services! We provide thorough system inspections, cleaning, and calibration services in order to ensure you get the most from your home heating and cooling.
Are you looking for reliable home plumbing installation services? Do you need drain cleaning or repairs? You’ve come to the right place! Our certified plumbing specialists offer complete and comprehensive plumbing services to our clients. We take your need for access to clean water and effective sewer systems seriously, bringing you a full range of plumbing solutions that guarantee you’re covered in all situations.
Trust our Richmond Heights team for:
- Plumbing repair services
- Plumbing fixture installation
- Plumbing remodels
- Water heater services
- Sump pump services
- Commercial plumbing services
- Commercial drain services
- And more!
HVAC Company in Richmond Heights, MO
Our team has been serving Richmond Heights, MO and the surrounding areas of St. Louis for generations—over 90 years, in fact! When we bring service to your home, you are the primary goal. We cut no corners and stop at nothing to ensure your complete satisfaction and to make sure we’ve done our very best every time. With summers in the 90-100 degree range, plus cold winters, you can count on us to keep your home comfortable all year round.
Learn more about what Classic Aire Care can provide for your home or schedule a service today by contacting us online or calling 314-300-6755!
for Richmond Heights, MO
Our Reviews by City
wonderful service, nice servicemen
Marty - Richmond Heights, MO
Howard - Richmond Heights, MO
Arrived on time, efficient, fixed the problem.
Kathleen - Richmond Heights, MO
Scott - Richmond Heights, MO
Scott - Richmond Heights, MO
excellent job as usual
Sadye - Richmond Heights, MO
I trust this service
Pes - Richmond Heights, MO
We have been having our system serviced with this company for many, many years.
Morey - Richmond Heights, MO
The man who came to our house did a great job, and was patient w our questions.
Marty - Richmond Heights, MO
Tom was very efficient in diagnosing the problem with our furnace, and was extremely efficient in his recommended repairs.
Joyce - Richmond Heights, MO
Showed me the situation with the furnace, explained and answered all my questions, polite.
Serviced ac..found leak in evaporater coil..replacing under part warranty only
Replaced warranty sensor on ac
Customer described Icing of coil symptoms. Found superheat creeping to 30+. I relocated thermostatic expansion valve bulb and retested. Superheat regulating normal now. Compressor: 5.4A .Condenser fan: 0.32A . Blower: 700 cfm .ambient: 76.liquid line:77 .suction line:48 .metering device: TXV . Suction pressure: 103(33) .head pressure: 279(91). Thermostat: 71.
Work Done: Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. Second floor system: installed PURE-AIR maintenance kit for air purification system. Compressor: 9.5A .Condenser fan: .78A . Blower: 1600 .ambient: 68 .liquid line: 68.suction line: 57 .metering device: TXV . Suction pressure: 101(32). First floor system: Found blower run capacitor too weak. Replaced capacitor and tested amp draw of 3/4hp blower. Compressor: 12.3A .Condenser fan: 1.4A Blower: 9.1A.ambient: 76. metering device: TXV . Suction pressure: 55-62. Return air: 67.supply air:49-52 .wet bulb: 59 . SC: 3-10. SH: 16-22. (Noncond)
Work Done: Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked electronic air cleaner: very dirty and blocking air flow. Compressor: 13A.Condenser fan: 1.45A . Blower: 5.7A, mh.ambient: 60 .liquid line: 66 .suction line: 35.metering device: TXV . Return air:65.5 .supply air: 44 .wet bulb: 55 . Work suggested: customer plans to clean air cleaner.
Check out water leak...
Returned March 23, 2018: John’s note: replaced blower motor and capacitor for second floor system air handler (9059).
Checked out heat pump units
Checked for gas leak,cleaned pilot and relite