There are 8,603 people living in Richmond Heights, MO and 4,244 households. Classic Aire Care is here to take care of any repair, replacement or maintenance you may need on your furnace and AC. Whether you have a new home or a historic Richmond Heights home, we’re here to help! Head over to THE HEIGHTS. We’ll call you when we’re on our way!
Classic Aire Care has been providing heating and cooling services in the Richmond Heights area for decades. Whether your furnace needs a tune up or your air conditioner needs replacing, Classic Aire Care has the staff to get the job done. Our highly trained, licensed service technicians and installers get the job right the first time. If you live in the Richmond Heights area and you need a furnace or air conditioner repair, maintenance or install call us at 314-300-6755.
for Richmond Heights, MO
Our Reviews by City
I trust this service
Pes - Richmond Heights, MO
We have been having our system serviced with this company for many, many years.
Morey - Richmond Heights, MO
The man who came to our house did a great job, and was patient w our questions.
Marty - Richmond Heights, MO
Tom was very efficient in diagnosing the problem with our furnace, and was extremely efficient in his recommended repairs.
Joyce - Richmond Heights, MO
Showed me the situation with the furnace, explained and answered all my questions, polite.
On time, never stopped working, answered all questions.
Susan - Richmond Heights, MO
Joe was wonderful. It was great that he put shoe covers on without being asked.
Complete Professional Service
Derwin - Richmond Heights, MO
Serviceman - Joe was excellent
Excellent work, as usual.
Dick - Richmond Heights, MO
Roger is a fine professional. I usually request him for any service work. There are probably other fine technicians, but I know he's good.
Cofman - Richmond Heights, MO
Our heating repair man was amazing. He diagnosed the problem immediately, and also resolved some other minor aggravating issues.
Wonderful service, Josh was just GREAT!!
Margaret - Richmond Heights, MO
Scott - Richmond Heights, MO
Replaced flue piping
Spring startup on three ac
Maintenance on two AC systems!
Replaced blower module and relay
Checked out system,found bad motor module,ordered
Replaced failed part
Replaced failed part
Clean and check
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. 1019: Replaced air filter. Compressor: 8.6A.Condenser fan: .83A .ambient: 70 .liquid line: 81 .suction line: 49 .metering device:TXV . Suction pressure: 108(36) . Return air: 70 .supply air: 50 . 1021: Found blower run capacitor weak: 14%low. Replaced capacitor under parts only warranty and tested amp draw. Compressor: 6.6A .Condenser fan: 1.55 . Blower: 4.0A .ambient: 72 .liquid line: 78 .suction line: 38 .metering device: piston . Suction pressure: 66(38) . Return air: 68 .supply air: 50 .wet bulb: 58 .
Diagnosed a/c problem