Quality Heating, Cooling & Plumbing Services in St. Charles, MO
The heating, cooling and plumbing systems in your St. Charles home are critical not only to your comfort, but to the value of your home as well. To protect your investment, you need a company that you can trust for all your HVAC and plumbing needs.
At Classic Aire Care, we are a family owned heating, cooling and plumbing company that has been serving the St. Charles area since 1926. We provide both residential and commercial services, and our highly skilled-and knowledgeable professionals offer some of the best value and customer service available. We provide heating, air conditioning, plumbing, insulation, air quality and home energy services, as well as 24-hour HVAC and plumbing emergency services.
From Weldon Spring Heights to Elm point and beyond, you can trust Classic Care Aire for all your HVAC and Plumbing needs. Contact us today at 314-300-6755 to schedule an appointment!
HVAC Services for St. Charles Home & Business Owners
At Classic Aire Care, we feature highly-trained, NATE-certified technicians that provide a complete selection of heating and cooling services, including routine maintenance, repairs, system replacements and new installations. We work with a variety of HVAC equipment including:
- Heat pumps
- Central air conditioners
- Air handlers
- Packaged systems
- Ductless mini-splits
- Rooftop AC units
- Process coolers
- And more
We can handle all of your HVAC maintenance needs, from changing air filters to cleaning air conditioning coils or furnace burners, as well as repairs ranging from simple tasks like replacing belts to complex ones like replacing compressors or installing a completely new system. We also offer planned maintenance agreements, to make the maintenance process simple and convenient, as well as 24-Hour HVAC emergency service, for problems that happen outside of normal business hours.
Contact us today to learn more about our HVAC service or to schedule an apportionment!
Plumbing Services in St. Charles County
Whether you have a minor plumbing problem like a clogged drain or a leaky toilet, or you have a major plumbing emergency, our team of professional plumbers at Classic Aire Care can help. We provide a wide variety of plumbing services for St. Charles county residents and businesses, including:
- Water, drain and sewer pipe installation, repairs and maintenance
- Gas pipe installations and repairs
- Complete re-piping services
- Water and gas leak detection and repair
- Sewer and drain cleaning and clog removal
- Trenchless sewer pipe lining
- Grease trap installations and maintenance
- Video camera pipe inspections
- Plumbing system inspections
- Water heater installation, repair and maintenance
- Plumbing fixture installation and maintenance
- Toilet installations and repairs
- 24-hour emergency plumbing service
To learn more about our plumbing services or to request an estimate, contact us today!
St. Charles Home Energy & Air Quality Services
In addition to our standard HVAC and plumbing services, our team at Classic Aire Care also offers a variety of services that can help improve your indoor air quality, reduce your utility costs and make you more comfortable overall. These include:
- Air cleaner and filter installation and maintenance
- Installation of humidifiers and dehumidifiers
- Home energy audits
- Air sealing and insulation services
- Duct cleaning and installation
- Programmable thermostat installation and service
Contact us today to learn how you can reduce your energy costs!
Call Classic Aire Care for HVAC & Plumbing Services in the St. Charles Area
Whether you need some basic HVAC maintenance, plumbing repairs or a new programmable thermostat, you can trust our team at Classic Aire Care for all your HVAC and plumbing needs in St. Charles and the surrounding areas.
Contact us today at 314-300-6755 to schedule an appointment!
for Saint Charles, MO
Our Reviews by City
Mark - Saint Charles, MO
Great Customer Service
Roxanne - Saint Charles, MO
excellent service-technian wore his shoe covers-very polite
Terry - Saint Charles, MO
Great asset to company
Eric - Saint Charles, MO
Sean was very knowledgeable and walk me through the entire process. He was was also very compassionate that we had a newborn baby and made sure the heat worked before leaving
Helpful, friendly service
Stephen - Saint Charles, MO
Paul - Saint Charles, MO
Very professional and honest.
Linda - Saint Charles, MO
Wallace - Saint Charles, MO
Angela - Saint Charles, MO
Quick and Complete fix
Wayne - Saint Charles, MO
John, was on time and quickly and efficiently found and repaired my issue....
Good, reliable service
Pat - Saint Charles, MO
Brian was friendly, professional, proficient.
Glenda - Saint Charles, MO
Brian was excellent
Joanne - Saint Charles, MO
very nice young man, explained service. Put new filter that I had into furnace . Good Job.
Service on 11/30/17
Frank - Saint Charles, MO
Friendly guy, great service and helpful suggestions!
Timothy - Saint Charles, MO
We were very pleased with our furnace tune up..your tech,Jeffrey K was super..He was very polite and easy and fun to talk to...
I can always count on John Murphy to give me the very best service and is very helpful in giving me recommendations to help me keep my system running
Wayne - Saint Charles, MO
Classic has been my HVAC company for years and they have never disappointed me in keeping my HVAC and plumbing in great working order.....
Thank you for your excellent service.
Gryfon - Saint Charles, MO
Angela - Saint Charles, MO
Jeff is a great technician. He paid attention to detail and was helpful explaining the questions I had. I hope I can request him by name the next time I need service work on our systems.
yearly furnace clean & check
Lois - Saint Charles, MO
Been using classic care for a few years. Terrific service. No unnecessary repairs. I minor part replaced. Nominal cost. Great company and service people.
Annual home furnace inspectiom
Chris - Saint Charles, MO
Excellent, very good
Clean and check 2systeks, replaced 2capicatoesm
Furnace maintenance...replaced filter, water panel and installed Bluetube UV purifying system
Furnace maintenance for both system!
Clean and check recommend humidifier
Replaced warranty pressure switch, customer signed up for maintenance agreement and ordered filter package
Clean and check customer,er signed up for a maintenance plan
Serviced furnace and replaced filter
Clean and check 90% Lennox, replaced apco bulb and humidifer pad
Fall clean & check on Lennox furnace, also servicing humidifier
Fall clean and check on 21yr old Carrier furnace
Fall clean and check on 10yr old furnace
No heat, found element not connected
Return December 28, 2017: replaced blower motor module. Tested operation. HP temperature rise: 18. System temperature rise: 64.
Service call—high limit trip, changed filter
I found pressure switch that senses pressure in combustion blower housing would not close! I replaced pressure switch and calibrated to 1.15 inches WC using manometer. Tested furnace operation. Manifold pressure: 3.6 inches. Checked filter.
Found system cycling low stage heat on and off. Thermostat is set about 6 degrees above current room temperature. Has 20 KW heat kit. Checked fault history. Found active fault. Fault 26 (255 events): invalid heater size. I checked wiring harness and all connections. Heat kit suddenly started working properly. I checked heat kit resistor: 23,630 ohms. (Colors: red yellow orange gold). Average temperature rise: 60. Airflow: 1050 CFM. Blower RPM: 620. Static pressure: .08 inches. LM w/Scott S. @ Koch.
Found system cycling low stage heat on and off. Thermostat is set about 6 degrees above current room temperature. Has 20 KW heat kit. Checked fault history. Found active fault. Fault 26 (255 events): invalid heater size. I checked wiring harness and all connections. Heat kit suddenly started working properly. I checked heat kit resistor: 23,630 ohms. (Colors: red yellow orange gold).
Check performance of new Mitsubishi mini split system. Both units set for high speed blower. I set vanes to automatic: pointing down for heat. Living room unit: temperature rise: 30. Kitchen unit: temperature rise 31. Ambient at outdoor unit: 15. Outlet: 10.
Bedroom system: 7578: I found code 44: motor module not communicating with fancoil control. Checked fancoil Communication leads output. Has 12 VDC present. Need to replace motor module.