The heating, cooling and plumbing systems in your St. Charles home are critical not only to your comfort, but to the value of your home as well. To protect your investment, you need a company that you can trust for all your HVAC and plumbing needs.
At Classic Aire Care, we are a family owned heating, cooling and plumbing company that has been serving the St. Charles area since 1926. We provide both residential and commercial services, and our highly skilled-and knowledgeable professionals offer some of the best value and customer service available. We provide heating, air conditioning, plumbing, insulation, air quality and home energy services, as well as 24-hour HVAC and plumbing emergency services.
From Weldon Spring Heights to Elm point and beyond, you can trust Classic Care Aire for all your HVAC and Plumbing needs. Contact us today at 314-300-6755 to schedule an appointment!
HVAC Services for St. Charles Home & Business Owners
At Classic Aire Care, we feature highly-trained, NATE-certified technicians that provide a complete selection of heating and cooling services, including routine maintenance, repairs, system replacements and new installations. We work with a variety of HVAC equipment including:
- Heat pumps
- Central air conditioners
- Air handlers
- Packaged systems
- Ductless mini-splits
- Rooftop AC units
- Process coolers
- And more
We can handle all of your HVAC maintenance needs, from changing air filters to cleaning air conditioning coils or furnace burners, as well as repairs ranging from simple tasks like replacing belts to complex ones like replacing compressors or installing a completely new system. We also offer planned maintenance agreements, to make the maintenance process simple and convenient, as well as 24-Hour HVAC emergency service, for problems that happen outside of normal business hours.
Contact us today to learn more about our HVAC service or to schedule an apportionment!
Plumbing Services in St. Charles County
Whether you have a minor plumbing problem like a clogged drain or a leaky toilet, or you have a major plumbing emergency, our team of professional plumbers at Classic Aire Care can help. We provide a wide variety of plumbing services for St. Charles county residents and businesses, including:
- Water, drain and sewer pipe installation, repairs and maintenance
- Gas pipe installations and repairs
- Complete re-piping services
- Water and gas leak detection and repair
- Sewer and drain cleaning and clog removal
- Trenchless sewer pipe lining
- Grease trap installations and maintenance
- Video camera pipe inspections
- Plumbing system inspections
- Water heater installation, repair and maintenance
- Plumbing fixture installation and maintenance
- Toilet installations and repairs
- 24-hour emergency plumbing service
To learn more about our plumbing services or to request an estimate, contact us today!
St. Charles Home Energy & Air Quality Services
In addition to our standard HVAC and plumbing services, our team at Classic Aire Care also offers a variety of services that can help improve your indoor air quality, reduce your utility costs and make you more comfortable overall. These include:
- Air cleaner and filter installation and maintenance
- Installation of humidifiers and dehumidifiers
- Home energy audits
- Air sealing and insulation services
- Duct cleaning and installation
- Programmable thermostat installation and service
Contact us today to learn how you can reduce your energy costs!
Call Classic Aire Care for HVAC & Plumbing Services in the St. Charles Area
Whether you need some basic HVAC maintenance, plumbing repairs or a new programmable thermostat, you can trust our team at Classic Aire Care for all your HVAC and plumbing needs in St. Charles and the surrounding areas.
Contact us today at 314-300-6755 to schedule an appointment!
for Saint Charles, MO
Our Reviews by City
yearly furnace clean & check
Lois - Saint Charles, MO
Been using classic care for a few years. Terrific service. No unnecessary repairs. I minor part replaced. Nominal cost. Great company and service people.
Annual home furnace inspectiom
Chris - Saint Charles, MO
Excellent, very good
Jeffrey - Saint Charles, MO
Very knowledgeable tech.
Service exceptional and price was great
Deborah - Saint Charles, MO
I was impressed with the company, service, and technician. Brian was very thorough, and professional. Readily agreed to clean the water hoses on my furnace and humidifier. A real asset to your company. Hope to get him next spring when I have my air conditioner serviced
great Service and awesome people
Marguerite - Saint Charles, MO
Susan - Saint Charles, MO
Quick Response, Great Service, Honest Tech!
Andrew - Saint Charles, MO
Jeff did a thorough inspection and kept us informed through the whole thing. He ensured that all of our questions were answered and our system was returned to normal after an unexpected issue.
Leann - Saint Charles, MO
Gave me information I was not aware of and made the appointment very easy
I have had great service from Classic Aire for many years. I even bought my new furnace and AC from them in my previous home.
Patricia - Saint Charles, MO
good. service ... fair/ poor price
Tom - Saint Charles, MO
The price of the ultraviolet light and parts seemed excessive however the technician who was here did a very good job
Great and friendly service by John Murphy.
James - Saint Charles, MO
Always the best and very professional service and maintenance.
Gary - Saint Charles, MO
Well pleased with fall maintenance appointment.
Gus - Saint Charles, MO
very happy with the service
Dena - Saint Charles, MO
Good service as usual.
Tom - Saint Charles, MO
Great service. I am sending the survey but I don't know what the Nearby Terms nod conditions are so I am NOT agreeing to them. I just want you to
Judy - Saint Charles, MO
I was very pleased with the service today. Corey Stiles was very thorough on the equipment and made notes for the next time. He was very courteous. Actually, I would like him to come back.
Mike - Saint Charles, MO
Don - Saint Charles, MO
Roxanne - Saint Charles, MO
Very friendly and efficient.
Amazing customer service!!
Debra - Saint Charles, MO
I always have excellent service with Classic Aire Care. Every technician I have encountered has always been professional and on top of their game.
Fall clean & check on 32yr old York electric heat furnace
Working on Lennox furnace
Furnace was running when I arrived. Thermostat set for 78. 70 degrees in the home. Gas valve turned off and on twice very quickly when I removed top door of furnace. I tested flame sensor current: good. 2.2 ?A. Problem would not reappear! Furnace running continuously with no problem! Possible faults to cause this: pressure switch, high temperature limit switch, rollout switches (two), wiring, Circuit board. Most likely culprits are pressure switch and circuitboard. Pressure switch is the most likely and least expensive repair. I replace pressure switch. Calibrated to 0.75 inches. Tested operation.
Cleaned & checked 2 gas furnaces. Inspected heat exchangers & flue venting. cleaned burners & flame sensors. Checked voltage & amp draw of motors. Test capacitor. Replaced air filter. Clean and check humidifier, replace pad, checked water flow and drain. Main system: Blower:2.1/2.8A . Inducer: 0.1/0.22A . Gas pressure: 1.9/3.5 inches water column. Temperature rise: 54 . Supply: 129 . Return: 75. Lower level system: Blower: 2.7A . Inducer: 1.35A . Gas pressure: 3.6 inches water column. Temperature rise: 52 . Supply: 125 . Return: 73 .
Serviced heating system had
Furnace maintenance! Replaced filter
Furnace maintenance for 2 systems. Replaced weak run capacitor
Clean and check
Clean and check
Fall clean & check on 17yr old Furnace, humidifier service included
Service on electric heat
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Clean and check humidifier, replace pad, checked water flow and drain. Blower: 2.8/3.9A . Inducer: .10/.23A. Gas pressure: 2.75/3.9 inches water column.
Furnace maintenance! Replaced weak run capacitor
Maintenance on the furnace! Replaced both furnace filter and humidifier pad!
Heat exchanger check—ok
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Blower: 5.4A. Inducer: 1.4A . Gas pressure: 3.5 inches water column. Temperature rise: 59 . Supply: 136. Return: 77 .
Replaced evaporator coil!