for Saint Louis, MO
Our Reviews by City
Great service came at 8 pm
Mary - Saint Louis, MO
Kent - Saint Louis, MO
We were very pleased with the purchase process, the timely install, the dedicated workman, and cleanup.
Sy - Saint Louis, MO
Very nice guy
Amy - Saint Louis, MO
Great service awesome price
Rufus - Saint Louis, MO
The service was tops and the repairman was excellent
AMAZING!!!! Service!!! Price was perfect
Angela - Saint Louis, MO
Sean Koepke was awesome. He truly cared about our family. Knowledgeable about his craft. Informed us of everything we needed to know. Please thank him he's very kind courteous and respectful. Thank you Classic Aire Care for a job well done.
Charles - Saint Louis, MO
A job well done
Great friendly service
Mark - Saint Louis, MO
Great service from a really nice technician.
Adrienne - Saint Louis, MO
It was great! See previous answer
Norbert - Saint Louis, MO
Maintenance on Lennox air renewed service plan
Maintenance on Lennox air
Maintenance on AC! Replaced nasty drain hose
Clean & check on 2 a/c systems
Ac Maintence Lennox
No cool,found shorted out stat...
Maintenance on AC, replaced filter, UV bulb and dual capacitor
Maintenance on AC, replaced furnace filter, replaced weak dual capacitor on AC
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. supply air: 135. Return air: 75. Customer plants to replace air filters. Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Compressor: 4.5A .Condenser fan: .73A. Blower: 4.5 .ambient: 47 .liquid line: 49 .suction line: 36 .metering device: TXV. Return air: 48.supply air: 68.
Lennox gas furnace replaced air pressure switch assy