There are 52,575 people living in St. Peters, MO and 20,861 households, making St. Peters tied with Blue Springs, MO as the 10th largest city in Missouri! Classic Aire Care might not be able to clean and check all 20,861 AC’s and furnaces, but we would love the opportunity to take care of yours! Whether you need to complete your annual maintenance or are looking for a quick repair, Classic Aire Care is a phone call away. If you are in a brand new home or even one of St.Peters’ charming historical homes, Classic Aire Care is here for you with 24 hour emergency service. Head on over to the Rec-Plex! We’ll call you when we’re on our way.
Classic Aire Care has been providing heating and cooling services in the St. Peters area for decades. Whether your furnace needs a tune up or your air conditioner needs replacing, Classic Aire Care has the staff to get the job done. Our highly trained, licensed service technicians and installers get the job right the first time. If you live in the St. Peters area and you need a furnace or air conditioner repair, maintenance or install call us at 314-300-6755.
for Saint Peters, MO
Our Reviews by City
Mary - Saint Peters, MO
Jewel - Saint Peters, MO
John was very informative. explained my problem and helped me make a decision.
Very friendly and polite employee
Michael - Saint Peters, MO
Nancy - Saint Peters, MO
Sheila - Saint Peters, MO
The serviceman who replaced our thermostat explained the options available clearly and did his work quickly.
Tami - Saint Peters, MO
Came out on a Saturday late in the day and fully explained the issue and fixed it so it worked until the new part came in.
Sonia - Saint Peters, MO
Corey was very thorough and completed his inspection in a timely manner. He explained the results and my options. He was very personable and would like him to be my service man.
Edward - Saint Peters, MO
Very satisfied with service provided so far
Always the best
Marian - Saint Peters, MO
The technician was very polite, on time, friendly, very informative and knowledgeable about his job. He's also very professional. Will gave him come back.
Homeowner was very happy with the service
Earl - Saint Peters, MO
Clean and check.....
Clean and check on a Raheem unit.... system running normally!
Replaced OEM condenser fan motor. Tested amp draw.
Found water dripping off of left side of Micro-channel evaporator coil. Found low Freon charge causing dry section of coil to drip. System has been running a couple weeks without a filter. Evaporator coil collecting dirt. I charged system to proper level per manufacturers subcooling chart. Compressor: 6.7A .Condenser fan: .65A .ambient: 78 .liquid line: 80.suction line: 45 .metering device: TXV . Suction pressure: 103 (33) .head pressure: 281 (91). Return air: 68. Tank61/17.
Repaired a/c system
Repaired a/c system
Ameren ue tune up
No cool, temporary..l.