There are 52,575 people living in St. Peters, MO and 20,861 households, making St. Peters tied with Blue Springs, MO as the 10th largest city in Missouri! Classic Aire Care might not be able to clean and check all 20,861 AC’s and furnaces, but we would love the opportunity to take care of yours! Whether you need to complete your annual maintenance or are looking for a quick repair, Classic Aire Care is a phone call away. If you are in a brand new home or even one of St.Peters’ charming historical homes, Classic Aire Care is here for you with 24 hour emergency service. Head on over to the Rec-Plex! We’ll call you when we’re on our way.
Classic Aire Care has been providing heating and cooling services in the St. Peters area for decades. Whether your furnace needs a tune up or your air conditioner needs replacing, Classic Aire Care has the staff to get the job done. Our highly trained, licensed service technicians and installers get the job right the first time. If you live in the St. Peters area and you need a furnace or air conditioner repair, maintenance or install call us at 314-300-6755.
for Saint Peters, MO
Our Reviews by City
Outstanding Service and Price
Bernard - Saint Peters, MO
Service technician was professional and exceeded my service expectations.
Totally great service - detailed service and very nice service person.
Diana - Saint Peters, MO
The service technician took his time to do the service, he was very professional, answered all my questions and I will use the service in the future.
Ken - Saint Peters, MO
Vicki - Saint Peters, MO
Always great service.
Cathy - Saint Peters, MO
Service team at Classic Air care is the best.
Informative and fast service
Tami - Saint Peters, MO
Explained a problem he found and I felt confident in making my decision on what needed to be done.
Mary - Saint Peters, MO
Jewel - Saint Peters, MO
John was very informative. explained my problem and helped me make a decision.
Very friendly and polite employee
Michael - Saint Peters, MO
Nancy - Saint Peters, MO
Clean and check 2 systems
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Found blower run capacitor weak: 13%low. Replaced capacitor and tested amp draw. Checked filter. Clean and check humidifier, replace pad, checked water flow and drain. Blower: 4.6A . Inducer: 1.0A . Gas pressure: 3.6 inches water column.
Clean and check on ac customer signed up for agreement
Clean and check ac and furnace in a trailer, all checked out good
Cleaned & checked gas furnace. Inspected heat exchanger with Visible Defects solution. Inspected flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Blower: 4.3A . Inducer: NA. Air filter was not covering return air opening. Also unfiltered air enters through bottom of the furnace. Replaced air filter. Secured filter retainer. Blower assembly is dirty. Evaporator coil: moderately dirty.
Serviced air conditioning system
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Compressor: 7.6A .Condenser fan: .6A . Blower: 800 .ambient: 82 .liquid line: 85 .suction line: .metering device: . Suction pressure: .head pressure: 188(95). Return air: 66.5 .supply air: 49 .wet bulb:55 . Found burnt spade connection at start winding lead. Repaired connection.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Compressor: 8.0.Condenser fan: l9A . Blower: 4.5A .ambient: 73 .liquid line: 83 .suction line: 53.metering device: TXV . Suction pressure: 121(41) . Return air: 75 .supply air: 58 .wet bulb: 64. Air filter does not fit properly in blower compartment. I installed an external filter rack in the return air drop. Water heater T&P valve is leaking. Also water heater inlet and outlet is backward! Also, may need expansion tank added.
Clean and check
Ameren ue tune ups