for Wentzville, MO
Our Reviews by City
Theresa - Wentzville, MO
Dave - Wentzville, MO
Quick, efficient, friendly.
Great service - on time and fixed the problem
Coleen - Wentzville, MO
The 2 technician's were very friendly and did GREAT work
Greg - Wentzville, MO
Amazing service on a Sunday!
Ron - Wentzville, MO
Our A/C went out in the 100+ degree heat on a Saturday night, called first thing Sunday and was told it would be Monday night before a tech could come out. Corey came out Sunday afternoon instead, and saved us and our 3 large dogs from a second sweltering night without A/C. He fixed our issue within 15 minutes, very professionally! We could not have been happier with the service!
Laura - Wentzville, MO
Technician left a service jumper in on the compressor relay that caused the unit to run all the time and froze up the coils.Had to take another day off of work to meet the new technician to remove the jumper.
Service was terrific. Quick and efficient.
Rene - Wentzville, MO
Excellent service. Technician was knowledgeable, fast and friendly.
Friendly and knowledgeable
Chris - Wentzville, MO
Very knowledgeable and friendly. Diagnosed our AC unit and had it working within 30 minutes. Technician arrived on time at our appointment time, very convenient.
Joe - Wentzville, MO
technician was very helpful friendly and professional
Jane - Wentzville, MO
Very helpful and knowledgeable.
Follow up. January 2, 2019: I replaced pressure switch assembly. Tested operation. Combustion blower: 0.58A,3phase. Checked temperature rise. 51. Blower: 4.4A. Cfm: 1332. Supply: 116. Return:65.
Second-floor ground source heat pump unit: 7659: found compressor locked up. Will not start. Also, auxiliary heat unit has only 1 element working. Suggestions: project manager to price replacement heat pump unit and auxillary heat unit second floor system tomorrow about noon.
Performed gas inspection for home sale. Furnace room needs combustion air venting per gas code. Also found basement pressure is negative when furnace blowers are on, causing fluegas spillage at water heater vent hood. Basement needs make up air venting or entry door to basement removed.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Adjust blower. Compressor: 6.7A . Condenser fan: 0.65A . Blower: 3.0A . ambient:89 . liquid line: 94, dirty . suction line: 51 . metering device: piston . Suction pressure: 130(45) . Return air: 71 . supply air: 53 . wet bulb: 59.5 ,RH: 56%.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Replaced air filter. Compressor: 14.4A . Condenser fan: 1.2A . Blower: 6.7A. ambient: 77 . liquid line: 88 . suction line: 60 . metering device: piston 90 . Suction pressure: 119(41). Return air: 74.5 . supply air: 54 . wet bulb:62 . SH: T+6.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Checked filter: pleated: .52” drop. Compressor: 7.65A . Condenser fan:0.82A . Blower: 4.9A, H . ambient: 82 . liquid line: 86, dirty . metering device: piston . Suction pressure: 73. Return air: 74.5 . supply air: 50.5 . wet bulb: 60 . Split and washed condenser coil. Rem. Suction: 73. Suction line: 43. Air filter is restricting airflow. Furnace Has only 16 x 16 opening for air filter. Also has restrictive return air ducting and restrictive supply air ducting. Total external static pressure: 1.04 inches water column. replaced filter with fiberglass tape for better airflow. Recommend using fiberglass filters only. Customer would like estimate to install larger air-conditioner and ductwork. Sean schedule for 10 AM August 23.
Found dual run capacitor bad. Open circuit. Replaced capacitor and tested amp draw of motors. Checked Freon level. Compressor: 19A. Condenser fan: 1.35A . ambient: 86. liquid line: 90 . suction line: 45. metering device: piston . Suction pressure: 75(45). Work suggested: Replace air filter.
Replaced evaporater coil
I found bad start assist kit, bad compressor run capacitor (dual), weak fan capacitor: 25% low. Also, condenser coil is very dirty. I replaced defective parts. Tested cooling operation and found system approximately 20 to 30% low on Freon! uses (R22)! Suction: 72 (43) suction line: 78. Metering device: TXV. Head pressure: 208. Subcooling: 0 to 2. Thermostat: 89. Customer plans to have a friend add Freon. Work suggested: recommend putting some repair costs toward replacement. Need to schedule project manager to price out new air conditioner. customer purchased maintenance plan today. Need to schedule first visit.
Turned on system. Was set at 70. Found high temperature drop. 23. Found 3M pleated air filter restricting flow, causing System to ice up. Replaced air filter. Blew out clogged drain trap. Checked system for leaks. Found evaporator coil leaking. Needs new evaporator coil. Work suggested: recommend fiberglass type air filters. Air filters to be delivered. Need to check on cost and availability replacement of evaporator coil for air handler.