for Wentzville, MO
Our Reviews by City
The 2 technician's were very friendly and did GREAT work
Greg - Wentzville, MO
Amazing service on a Sunday!
Ron - Wentzville, MO
Our A/C went out in the 100+ degree heat on a Saturday night, called first thing Sunday and was told it would be Monday night before a tech could come out. Corey came out Sunday afternoon instead, and saved us and our 3 large dogs from a second sweltering night without A/C. He fixed our issue within 15 minutes, very professionally! We could not have been happier with the service!
Laura - Wentzville, MO
Technician left a service jumper in on the compressor relay that caused the unit to run all the time and froze up the coils.Had to take another day off of work to meet the new technician to remove the jumper.
Service was terrific. Quick and efficient.
Rene - Wentzville, MO
Excellent service. Technician was knowledgeable, fast and friendly.
Friendly and knowledgeable
Chris - Wentzville, MO
Very knowledgeable and friendly. Diagnosed our AC unit and had it working within 30 minutes. Technician arrived on time at our appointment time, very convenient.
Joe - Wentzville, MO
technician was very helpful friendly and professional
Jane - Wentzville, MO
Very helpful and knowledgeable.
Prompt Professional Service
Kimery - Wentzville, MO
Jeff - Wentzville, MO
Found control fuse at the furnace control board was blown. Tested for shorts and found all three conductors to outdoor contactor were shorted! I connected one conductor only to contactor, using ground as the other conductor for contactor. Tested cooling mode. Tested heat mode. I set up thermostat for gas heat.
Maintenance for 1st and 2nd fl furnaces! Replaced steam humidifier canister
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Checked filter. Inducer: 0.1 A. Blower: 2.1 A. Clean and check humidifier, replace pad, checked water flow and drain.
Home Depot customer--replaced warranty evaporator coil!
Clean & checked a/c system
Geothermal systems: Main system cooling OK. Checked temperature drop. 21.5 Master bedroom/lower level system: main control board has "HP" LED on and "ESC" LED on. I cycled power to control board and system reset and came on after set delay. I tested operation. I checked Freon pressures. Discharge pressure: 330 to 350. Subcooling: 22 (measured with discharge pressure). Suction: 110 to 116 (SH: 13). Metering device: TXV. Supply water: 81. Exit water: 95. Current pressures are well under high-pressure safety switch rating of 600 psi. Geothermal loop temperature may be getting too high due to extreme hot weather.
Repaired a/c system
Repaired a/c system
Replaced evaporator coil
Replace warranty coil