for Wentzville, MO
Our Reviews by City
Theresa - Wentzville, MO
Dave - Wentzville, MO
Quick, efficient, friendly.
Great service - on time and fixed the problem
Coleen - Wentzville, MO
The 2 technician's were very friendly and did GREAT work
Greg - Wentzville, MO
Amazing service on a Sunday!
Ron - Wentzville, MO
Our A/C went out in the 100+ degree heat on a Saturday night, called first thing Sunday and was told it would be Monday night before a tech could come out. Corey came out Sunday afternoon instead, and saved us and our 3 large dogs from a second sweltering night without A/C. He fixed our issue within 15 minutes, very professionally! We could not have been happier with the service!
Laura - Wentzville, MO
Technician left a service jumper in on the compressor relay that caused the unit to run all the time and froze up the coils.Had to take another day off of work to meet the new technician to remove the jumper.
Service was terrific. Quick and efficient.
Rene - Wentzville, MO
Excellent service. Technician was knowledgeable, fast and friendly.
Friendly and knowledgeable
Chris - Wentzville, MO
Very knowledgeable and friendly. Diagnosed our AC unit and had it working within 30 minutes. Technician arrived on time at our appointment time, very convenient.
Joe - Wentzville, MO
technician was very helpful friendly and professional
Jane - Wentzville, MO
Very helpful and knowledgeable.
Furnace maintenance! Signed up for agreement
Checking humidity levels
Clena and check, all is good
ML180UH070P36A-53. 1714L13790: Found diagnostic code 7: ignition failure. I cycled power and reset furnace control. Tested heat operation and found very weak flame sensor current. I removed and cleaned flame sensor and retested: 2.7 µA.
No heat- dirty flame sensor. Also replaced filter
Clean and check
Secured filter door
No heat dirty filter
Furnace maintenance—replaced weak run capacitor