for Wentzville, MO
Our Reviews by City
Amazing service on a Sunday!
Ron - Wentzville, MO
Our A/C went out in the 100+ degree heat on a Saturday night, called first thing Sunday and was told it would be Monday night before a tech could come out. Corey came out Sunday afternoon instead, and saved us and our 3 large dogs from a second sweltering night without A/C. He fixed our issue within 15 minutes, very professionally! We could not have been happier with the service!
Laura - Wentzville, MO
Technician left a service jumper in on the compressor relay that caused the unit to run all the time and froze up the coils.Had to take another day off of work to meet the new technician to remove the jumper.
Service was terrific. Quick and efficient.
Rene - Wentzville, MO
Excellent service. Technician was knowledgeable, fast and friendly.
Friendly and knowledgeable
Chris - Wentzville, MO
Very knowledgeable and friendly. Diagnosed our AC unit and had it working within 30 minutes. Technician arrived on time at our appointment time, very convenient.
Joe - Wentzville, MO
technician was very helpful friendly and professional
Jane - Wentzville, MO
Very helpful and knowledgeable.
Prompt Professional Service
Kimery - Wentzville, MO
Jeff - Wentzville, MO
Repaired a/c system
Repaired a/c system
Replaced evaporator coil
Replace warranty coil
Found system low on Freon. Also, AC in need of cleaning. I leak tested system and found evaporator coil leaking! Needs a new coil. Has parts only warranty. I charge the system for temporary cooling.
Clean & check a/c system
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Checked filter. Checked temperature drop. 19.5. Checked Freon level. Low: Superheat: 28. Target: 10. I also found five ton System using for ton coil with 4 ton Piston (82)! System has two row condenser coil. I split and washed coil. I replaced piston with the proper size (90) to match condensing unit. Compressor: 13.8A .Condenser fan: 1.2A . Blower:6.6A .ambient: 75 .liquid line: 87 .suction line: .metering device: piston . Suction pressure: 118(39).head pressure: 279(92) . Checked temperature drop. 21.5. Return air: 69.5 .supply air: 48 .wet bulb:59.5 .
Diagnost bad circuit board
Cleaned and checked ground source air conditioners. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Checked filters. Check to pump: 4.6 A, 244 V. Water inlet temperature: 58. Basement system: 7507: found system to have mixed refrigerant! Running very high subcooling. Temperature drop: 15.5. Target: 18.5. Compressor: 8.6A.Condenser fan: NA . Blower: 1.5A .liquid line: 62 .suction line: 56 .metering device: TXV . Suction pressure: 67(39) .head pressure: 199(101) . Return air: 70 .supply air: 54.5 .wet bulb: 59 . Main floor system: 0101: Found compressor run capacitor weak: 22%low. Replaced capacitor and tested amp draw. Compressor: 13.2A. liquid line: 68 .suction line: 52 .metering device: TXV . Suction pressure: 115(39) . Return air: 70. supply air: 52 .wet bulb:58.5 . Second floor system: 7659: adjusted superheat. Compressor: 9.5A . Blower: 1.7A .liquid line:68 .suction line: 37 .metering devi
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Condenser coil: dirty. Compressor: 9.4A .Condenser fan: .72A . Blower: 5.2A .ambient: 73.liquid line: 95 .suction line: 36 .metering device: piston . Suction pressure: 63(36) . Return air: 66 .supply air: 50.5.wet bulb:55 . I adjusted blower speed for proper temperature drop and humidity removal. 3.8A. Checked temperature drop. 17.