There are 35,517 people living in Wildwood, MO and 10,837 households. Classic Aire Care might not be able to maintenance, repair or install all 10,837 AC’s and furnaces, but we sure can take care of yours! Whether you need a repair or need to complete your annual maintenance, Classic Aire Care is a phone call away. Maybe you’re in the market for a new system and are looking for the best equipment to install in your Wildwood home. Classic Aire Care and our team of professionals are just a phone call away. One of our highly trained Project Managers are ready and available to discuss exactly what will meet your needs and find the right system for you. Head on over to the Al Foster Trail! We’ll call you when we’re on our way.
Classic Aire Care has been providing heating and cooling services in the Wildwood area for decades. Whether your furnace needs a tune up or your air conditioner needs replacing, Classic Aire Care has the staff to get the job done. Our highly trained, licensed service technicians and installers get the job right the first time. If you live in the Wildwood area and you need a furnace or air conditioner repair, maintenance or install call us at 314-300-6755.
for Wildwood, MO
Our Reviews by City
Denise - Wildwood, MO
Anthony - Wildwood, MO
Tom seemed very disgruntled about providing service at my home. He didn't know much about the Nest Thermostat I had purchased or about my previous thermostat. He even asked me why I purchased the Nest in a condescending tone. This was not his business.
Good job. Very professional and polite
Thomas - Wildwood, MO
On time, clear, helpful
Jonathan - Wildwood, MO
Prompt and courtious service
Scott - Wildwood, MO
Sean arrived on time and completed the service on schedule. He provided information on surge protection for me to consider.
A/C Maintenance service
Mathew - Wildwood, MO
Patrick was on time, did a great job and was very friendly
Great Service From John Murphy
Thomas - Wildwood, MO
Eric - Wildwood, MO
Sydney - Wildwood, MO
Holly - Wildwood, MO
The service that I received was excellent. The technician was friendly, knowledgeable, and helpful.
Professional and very knowledgeable service technician
Tammy - Wildwood, MO
Great service and service representative
Jerry - Wildwood, MO
Timely and competent to
Brian - Wildwood, MO
Wonderful experience, Patrick was very fast and courteous
John - Wildwood, MO
Appreciate thoroughness of technician. Office called for appointment fairly late in Spring and had already booked out several weeks. Would have appreciated earlier call in season.
Gary - Wildwood, MO
Charles - Wildwood, MO
Cory was thorough in trying to solve our mystery noises. We couldn't repeat them and we found all systems working well.
Very professional, very pricey
Robert - Wildwood, MO
Sean was extremely professional, courteous, and accommodating. I would welcome his services anytime. But Classic Aire Care discontinued my maintenance/service agreement at $10.53/month and offered only a replacement plan for $14.33/month (a 36% increase). & then charged me $89 labor to replace a capacitor on a 4-year old system (capacitor was covered under warranty, $89 was for 15 min labor to replace it -- $356/hr?). I think that labor charge was clearly excessive for a warranted defect.
Dan - Wildwood, MO
Anita Engleman - Wildwood, MO
John - Wildwood, MO
Sean was great. Very informative, polite and professional. He did a nice job of answering my questions and performing his inspections.
Working on air handler
Working on Lennox heat pumps
Working on Lennox furnace
Fall clean & check on 2 10yr old Rheem furnaces, also servicing humidifiers
I found a second-floor bedroom damper blade not turning. I repaired damper under warranty. I moved obstructions away from common area supply registers. I opened second floor bathroom door to supply air to zone two area. I sealed air leaks with caulk, tape, and thumb gum.
Fall clean & check on 3 Lennox furnaces, also servicing humidifiers for systems
Serviced two heating system and humidifiers
Amana gas furnace replaced low voltage fuse
Found large Freon leak at suction connection of compressor. I repaired leak. Evacuated system. Test with bubbles. Recharge system. 10 pounds of 410A. System having trouble Establishing superheat. I tested TXV with ice water. Suction: 95 (29). I polished sensing bulb and suction line and installed copper clamps. Insulated and tested operation. Working good! Compressor: 12.6A.Condenser fan: 1.1A. Blower: 1300 .ambient: 85.liquid line: 99 .suction line: 52 .metering device: TXV . Suction pressure: 132(46) .head pressure: 319(100).
System froze up,found blocked filter...
Replaced evaporater coil
Furnace clean and ac clean. Customer to get a quote
Emergency no cool, bad txv
cleaned & checked 2 A/Cs & performed Ameren post data efficiency analysis. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. First floor system: 3.5 ton system has 16 x 20 x 1 air filter. I replaced restrictive pleated filter with fiberglass type filter. Found dual run capacitor weak: 17%low. Replaced capacitor and tested amp draw. Back-flushed condenser coil with Water-Saber. Re-check Freon level. Compressor: 15.7A.Condenser fan: 1.2A. Blower: 4.1A .ambient: 81 .liquid line: 96 .suction line: 52.metering device: Piston . Suction pressure: 67(40) . Return air: 73.3 .supply air: 53.2 .wet bulb: 61.6. Second floor system: found system very low on Freon. Doing very little cooling .ambient: 81 .suction line: 73 .metering device: Piston . Suction pressure: 23(-1). Return air: 74 .supply air: 69.1 .wet bulb: 62.5 .
Serviced three air conditioning systems
Clean and check
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Replaced air filter. Compressor: 9.65A.Condenser fan: 1.2A . Blower: 1600 .ambient:62 .liquid line: 68 .suction line:53 .metering device: TXV . Suction pressure: 113(38) .head pressure:211(73) . Return air: 69.5 .supply air: 50.
Charged your AC system
Replace fan motor
Added refrigerant to system