Air Conditioning Service in the St. Louis, MO Area
In the summer, the air conditioning system in your St. Louis home or business takes the edge off the heat and makes it far more comfortable for both work and relaxation. Without it, the summers would be far less enjoyable, so it makes sense to protect your investment with regular air conditioning service.
Our team at Classic Aire Care can help. Our residential and commercial AC services in the St. Louis area include:
- Air conditioner repair service
- Air conditioner installation and replacement
- Air conditioner maintenance
- 24-hour emergency air conditioning service
- Heat pump repair, installation, and maintenance
- Air handler repair, installation, and maintenance
- Ductless AC system installation, repair, and maintenance
- Planned maintenance agreements for cooling systems
Contact us today at (314) 300-6755 to learn more about our air conditioning services!
Air Conditioner Repair Services in the Greater St. Louis Area
When your air conditioner malfunctions, it is advisable to have the system inspected and repaired as soon as possible. Even minor problems like a clogged air filter could lead to more serious ones, such as an overheating compressor. Some of the more common air conditioner problems include:
- Inadequate cooling due to dirty coils, clogged air filter, or improper refrigerant levels
- Frozen evaporator due to duct obstructions, dirty condenser, or clogged air filter
- Unusual noises due to damaged fan belt, blower motor, or compressor problems
- Startup problems due to tripped breakers or safety systems, failed start capacitor, or damaged compressor
Whether the problem is minor or major, our team at Classic Aire Care can quickly find the cause and recommend the best repair options for your needs and your budget. We also offer 24-hour emergency repair services, for any problems that happen outside of our normal bluishness hours.
For all your air conditioner service and repair needs, contact our team at Classic Aire Care today!
St. Louis Air Conditioner Replacement & Installation Services
Once your air conditioner is beyond a certain age, it is often more cost-effective to replace it than to continue repairing an inefficient system. You should consider a new air conditioner if your current one:
- Is over 15 years old
- Requires frequent repairs or has major problems
- Costs a fortune to operate
- Has a SEER rating of less than 13
With today’s advanced technologies, a new system will be far more energy-efficient, up to 20 SEER, and it will cool more effectively.
At Classic Aire Care, we offer both air conditioner replacements and new installations. Contact our team for information about our available air conditioning systems!
Air Conditioner Maintenance for St. Louis Homes
Routine maintenance is essential to keep your air conditioning system running properly and efficiently. By having the system professionally inspected at least once a year, you can prevent unnecessary repairs, reduce cooling costs and extend its life. Though each system varies, the maintenance process typically includes:
- Cleaning the evaporator and condenser coils
- Checking the refrigerant levels
- Replacing the air filter
- Cleaning the air handler
- Checking the blower fan belt
- Lubricating bearings and pulleys
- Inspecting the safety and electrical systems
- Cleaning the condensate drain
- Measuring airflow at supply and return ducts
During a maintenance visit, our team from Classic Aire Care will thoroughly inspect your system, perform any required maintenance, and recommend any repairs that are necessary to prevent future problems.
Contact us today to schedule a service visit!
Call Classic Aire Care for Air Conditioner Service in the Greater St. Louis Area
At Classic Aire Care, we can handle all of your air conditioner service needs, including installations, maintenance, and repair, and we also offer heating, plumbing, indoor air quality, and insulation services.
Contact us today at (314) 300-6755 to schedule an appointment!
Our Air Conditioning Service Area in Greater St. Louis
We serve cities throughout the St. Louis area including much of St. Louis, St. Charles, and Jefferson counties. Specific areas we serve include Creve Coeur, Olivette, Maryland Heights, St. Charles, University City, Chesterfield, Clayton, Town and Country, and Overland.
for St. Louis, MO
Parkland - Glendale
David - St. Louis, MO
Great service Unhappy to spend so much on 3 year old unit
Judy - St. Louis, MO
Ronnie - St. Louis, MO
John's service is excellent.
very professional service
Victor - St. Louis, MO
I will be requesting Roger for all my heating/AC needs...very impressive
Ann - St. Louis, MO
August 22 2018
John - St. Louis, MO
Classic and quality
Ann - St. Louis, MO
Their response was prompt, thorough and professional and the problem was solved at that first service call. Their serviceman was knowledgeable and explained all aspects of the repair and the operation and maintenance of the a/c system.
Francis - St. Louis, MO
Jeff is a great guy, professional and gives the best (practical and easy to understand) advice
Tom - St. Louis, MO
The repair tech called first.He listened to what I had to say. When he arrived he went right to work. He solved the problem very quickly. He explained the problem to me and showed me the defective part.
Excellent service as usual
Richard - St. Louis, MO
Roger has lots of experience as well as being a good guy.
Edward - St. Louis, MO
My family and I enjoy having a consistent technician coming to service the unit. It gives us a sense of comfort.
Grace - St. Louis, MO
McCracken - St. Louis, MO
Knowledgeable and thorough
Autry - St. Louis, MO
John is the very knowledgeable technician. In addition to his detailed description of the issues, he also provided practical solutions.
Linda - St. Louis, MO
I was a little surprised it cost as much as it did.
Cleared drain and cleared fitting—sign up for maintenance plan!
Customer complaint of periodic noise that last less than one minute. Found condensate pump buzzing when it pumps. I discovered a piece of plastic “knock out” in reservoir right under pump! Removed piece of plastic to solve noise.
I found blown fuse in disconnect box. Also found bad dual capacitor: open circuit. Also, condenser coil very dirty. I replaced blown fuse. Replaced dual capacitor. Cleaned condenser coil. Checked filter. Blower: ml . ambient: 95 . liquid line: 104 . suction line: . metering device: piston . Return air: 81 . supply air: 60 . wet bulb: 68 .
Start up AC installed in April. Complaint second-floor too warm. Recommend closing first for vents during summer. I found air filter clogged with dirt! Replaced air filter. Checked Freon level. Topped off for proper sub cooling. No leaks found. Compressor: 7.7A. Condenser fan: 0.6A . Blower: M . ambient: 90 liquid line: 99 . suction line: 54 . metering device: TXV . Suction pressure: 120(41) . head pressure: 344(105) . Return air: 68.5 . supply air: 54 . wet bulb:59.5 .
Serviced furnace and humidifier and replaced filter and installed air purifier
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Blower: M . Inducer: 1.45A . Gas pressure: 3.35 inches water column.
Thermostat would not keep air conditioner running. I jumpered out thermostat to test system operation. I found air conditioner low on Freon! Condenser coil fans are smashed, restricting airflow. Coil is too damaged to restore. I also found dual run capacitor week: 24% low, compressor side. Work suggested: recommend replacing air conditioner. Richard price new AC with complete system option.
Living room unit: 778: replaced condenser fan motor, fan blade/prop assembly, fan capacitor, compressor overload and compressor capacitor. Cleaned condenser coil. Tested cooling operation. Front bedroom unit: 690: replace compressor overload. Clean condensing unit and tested operation. Rear bedroom unit: 776: cleaned condenser coil. Clean air filter. Tested cooling operation.
Cleaned & checked 2 gas furnaces. Inspected heat exchanger & flue venting. cleaned burners & flame sensors. Checked voltage & amp draw of motors. Test capacitors. Replaced air filters. Clean and check humidifier, replace pad, checked water flow and drain.
Serviced ac unit