for St. Louis Area
Our Reviews by City
Robert - St. Louis, MO
We continue to receive excellent service from Classic Aire Care.
Melissa - St. Louis, MO
On time, thorough, professional.
Actual Working Humidifier
Brenda - Chesterfield, MO
Jeff arrived ahead of schedule, quickly removed old humidifuer and installed the new one. Great job!
Gabriele - St. Louis, MO
Technician was professional, knowledgable, and pleasant. I felt confident in his work output.
Great experience with Tom and Classic Aire Care
Glen - Fenton, MO
Fast emergency service!
Jerry - St. Louis, MO
They were there when I needed them.
Toni - St. Louis, MO
Sean was positive about the other clients he had worked with in the building. Honest about the equipment throughout the building knowing the age of same. Forthright about services to extend the life of my equipment without being pushy. But most of all; a little thing.....he pulled a pair of shoe covers out of his pocket and put them on before entering my unit! That meant a lot. And not everyone does that!!
Rosemarie - St. Louis, MO
Dorothy - St. Louis, MO
As usual Tom is always efficient, professional and willing to answer all my questions clearly and concisely . His calm and business like manner is appreciated. He is an asset to your company.
Wonderful customer service!
Mrs Hargrave - Chesterfield, MO
Dave's expert customer service is why we request him each time. Hang onto this guy. He is a valuable employee!!
Fall clean and check includes humidifier service
Clean and check 2york funsces
Cleaned & checked condensing gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Checked drain. Clean and check humidifier, replace pad, checked water flow and drain. Blower: 4.2/4.2A . Inducer: .25/.45 . Gas pressure: 1.8/3.55inches water column. Temperature rise: 53/68 . Supply: 128/144 . Return: 73/76 .
Serviced heating system and humidifier
Furnace maintenance for 2 systems!
Maintenance on Lennox furnace
Maintenance on Carrier furnace and accessories.
Found bad gas valve..
Clicking noise coming from back furnace
Cleaned and checked gas boiler. Inspected and cleaned heat exchanger. Checked flu piping and draft. Cleaned burners, pilot, and flame sensor. Checked voltage and amperage draw of pump. Bleed air from system. Thermostat cycles pump only. Drained off pressure pressurized bladder tank: 12 psi. Set limit: 140. Pump relay control is very old and has a charred relay coil. Relay is over 50 years old but still working OK.