for St. Louis Area
Our Reviews by City
Natalie - Ballwin, MO
Pam - Ballwin, MO
The service was very thorough and the technician was professional and friendly.
Murphy Is the Best
Suzanne - St. Louis, MO
John Murphy did a thorough spring inspection. All is well with my HVAC system now.
Ken - Maryland Heights, MO
Jeff was very professional and extremely knowledgable.
Ron - Ballwin, MO
Excellent customer service
Sari - Creve Coeur, MO
Called ahead was on time quick, polite, and offered great suggestions
Sarah - Florissant, MO
They came out to do springtime maintenance on the air conditioning unit they installed in November and found a problem that they came back and fixed, at no cost to me!
Roberta - Olivette, MO
Very good service with polite and knowledgeable serviceman
Great service. Dave is very polite, personable, and professioal.
Mr. Ed Kurmann - St. Louis, MO
Dennis - Chesterfield, MO
Classic Aire Care always does a good job and I especially like that they try hard to send out the same technician every time.
Spring maintenance for both systems in home! Renewed their maintenance plan
Work Done: Cleaned and checked 2 air conditioners . Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. Work Suggested: main system: 3 ton air conditioner: replaced dual capacitor: $155. Garage system: 1 1/2 ton air conditioner: replaced dual capacitor: $155. Top off R – 22 Freon: $178.
found batteries in thermostat weak. Replaced thermostat batteries. Tested cooling operation. Found Freon level low: superheat 36 degrees off target. Ambient: 57. Suction: 65. Head: 187. Liquid line: 58. Suction line: 61. Wet bulb: 54. Temperature drop: 14. I found indoor air handler 25% undersized. Need to order metering device for a 2 ton air conditioner. Need to top off freon.
Serviced air conditioner
Spring maintenance on AC system!
Serviced air conditioner and replaced filter and capacitor
Planned spring maintenance visit
Maintenance on Amana heat pump replaced dual run capacitor
Work Done: 3-22-18 PFCC x's 2 Planned Fall Clean & Check completed in error, not attaching fall visit or customer will not get Fall 2018. was supposed to be a PSCC - PSCC rescheduled in Service Titan April 20, 2018: Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. Checked filter. First floor system: 8180: Compressor: 3.9A .Condenser fan: .85A . Blower: 2.1A .ambient:54 .liquid line: 62 .suction line: 45 .metering device: TXV. Return air: 66.supply air: 42.wet bulb:52 . Second floor system: Compressor:3.9A .Condenser fan: .85A . Blower: L .ambient: 54.liquid line: 59 .suction line:48 .metering device: TXV. Return air: 65.supply air: 42.wet bulb: 52 .