for St. Louis Area
Our Reviews by City
Very Nice young man, with knowledge about his profession.
Ricco - St. Louis, MO
Shannon - Chesterfield, MO
Everything was explained and options presented to fix issues. Great customer service.
Edna - St. Louis, MO
Courteous technician, did a great job even in the rain!
Very professional, very pricey
Robert - Wildwood, MO
Sean was extremely professional, courteous, and accommodating. I would welcome his services anytime. But Classic Aire Care discontinued my maintenance/service agreement at $10.53/month and offered only a replacement plan for $14.33/month (a 36% increase). & then charged me $89 labor to replace a capacitor on a 4-year old system (capacitor was covered under warranty, $89 was for 15 min labor to replace it -- $356/hr?). I think that labor charge was clearly excessive for a warranted defect.
Great service reasonably priced
Jeffery - Olivette, MO
Ken - Fenton, MO
quick and efficient
Mary - Affton, MO
Corey Stiles is Awesome
Kenneth - St. Louis, MO
Corey is awesome....so helpful, explains everything, genuinely friendly and caring. Corey is a credit and a value to Classic Aire Care. Our third service call with Corey. He is great...I meant to write more previously...one time the survey closed before if I finished. One complaint or inquiry...not about Corey but about the problems we are having with the air conditioning unit. Installed 8 years ago.....spent $505 years ago and another $249 today....and possibly more expenses. I don't understand why this is happening. Was it a defective unit? shouldn't the unit that Classic Aire Care installed have lasted much longer without these problems and expenses. We have had service inspections on the furnace and the a/c every 6 months for maintenance. I would very much appreciate a reply. Thank you
Jim - University City, MO
Excellent customer service --
Helen - St. Louis, MO
Tom arrived at specified time and performed work carefully, but quickly. He patiently answered my questions with understandable responses. He was very professional and courteous.
Maintenance on Amana air
Clean and check
Found thermostat would not send enough voltage to bring on cooling mode. Intermittent. I replaced the thermostat. Also, found condenser fan motor capacitor weak: 40% low. Replaced capacitor. Some foam gasket material is deteriorated and needs replaced. Air filter needs washing.
Ac Maintence Lennox
Checked out system repaired short
Clean & check on a/c system
Service AC, replaced drain hose and filters
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels: Low, both systems. Approximately same level as last year. Systems are not cooling at full capacity. Cleaned condenser coil. Also, return air ducts leak, causing negative basement pressure. (-.014 inches water column with both ACs running)
Ac Maintence Lennox
Repaired furnace and a/c system