Quality Plumbing & HVAC Services in Creve Coeur, MO
With plenty of older and historic buildings in the Creve Coeur area, residents and business owners need to have an HVAC and plumbing company they can trust to take care of their prized investment.
At Classic Aire Care, we have served the residents of Creve Coeur and St. Louis County since 1926, providing a level of service and value that has made us one of the most trusted HVAC and plumbing services in the region. Our talented professionals provide heating, air conditioning, plumbing, insulation, energy efficiency and air quality services, as well as 24-hour emergency HVAC and plumbing services. We operate throughout the Greater St. Louis area, serving both residential and commercial clients.
Whether you live near on of the many parks in Creve Coeur or in the middle of the city, you can count on Classic Aire Care for all your HVAC and plumbing needs. Contact us today at 314-300-6755 to request an estimate or to schedule an appointment!
Creve Coeur Heating & Air Conditioning Services
With NATE-certification and numerous industry credentials, our HVAC team at Classic Aire Care can handle all of your HVAC services, from new system installations and replacements to routine maintenance and repairs, Some of the services we offer include:
- Furnace service: From routine air filter changes and burner cleaning, to blower motor replacement and new thermostat installations, our team will keep your furnace running efficiently and safely.
- Boiler service: Whether you have a hot water boiler or a steam boiler, residential or commercial, we can keep you boiler running properly, from routine maintenance like cleaning the boilers to purging air from the system or replacing radiators.
- Air Conditioning service: We install, repair, and maintain nearly any kind of air conditioning system, including central air systems, ductless mini-splits, heat pumps, packaged systems, and commercial AC units.
- Planned maintenance: To make the maintenance process easier and more convenient, we offer planned maintenance agreements that help keep your HVAC equipment in great condition.
- Emergency HVAC service: Heating and air conditioning systems can break down at the worst times, which is why we offer 24-hour HVAC repair, for problems that happen on nights or weekends.
- And more!
For more information about our HVAC services, contact our team today!
Plumbing Services in the Creve Coeur Area
A plumbing problem can cause a lot of damage quickly, but with our professionals at Classic Aire Care, you can be sure nearly any problem is diagnosed and repaired quickly, day or night. Our plumbing services include:
- Water, gas and sewer pipe installation and repair
- Plumbing system maintenance and inspections
- Drain and sewer repair and installation
- Sewer and drain cleaning
- Clog removal
- Video camera sewer inspections
- Grease trap installation
- Leak detection
- Water heater installation and repaire
- Fixture installation and repair
- 24-hour emergency plumbing service
For all your plumbing needs, residential or commercial, contact our team today!
Energy Efficiency & Air Quality Services for Creve Coeur Homes
Energy efficiency and indoor air quality can have a significant impact on your overall comfort. At Classic Aire Care, we offer a variety of air quality and energy services, including:
- Air purifier and air cleaner installations
- Ventilation system installations
- Humidifier and dehumidifier installations
- Home energy audits
- Programmable thermostat installations
- Duct installation and cleaning
- Insulation and air sealing
Contact us today to learn more!
Call Us Today for HVAC & Plumbing Services in Creve Coeur, MO
From HVAC installations to water heater replacements, our team at Classic Aire Care can handle all your HVAC and plumbing needs.
For an appointment, contact us at 314-300-6755 today!
for Creve Coeur, MO
Our Reviews by City
Justin - Creve Coeur, MO
Exemplary service from Sean!
Shelley - Creve Coeur, MO
Sean is always a welcome addition to our day. His knowledge, and eagerness to answer questions is much appreciated!
Thorough and great service!
Jessica - Creve Coeur, MO
Elizabeth - Creve Coeur, MO
Helen - Creve Coeur, MO
I was a few minutes late arriving home from work, but the technician was here waiting for me with the appropriate part for the furnace
Service far exceeding the norm
Joe - Creve Coeur, MO
Explained the issues, if any, options, cost and very informative on all that he was doing and why.
knowledgeable service rep
Barry - Creve Coeur, MO
Kevin - Creve Coeur, MO
Miriam - Creve Coeur, MO
Brian Smith educated me about my humidifier. It seems that it was last serviced 2015. I didn't know it should have been added to my contract. I added it today. Brian was personable, informative, quick & left the area nice and clean. 5 stars for Brian!!
Elaine - Creve Coeur, MO
Alvah - Creve Coeur, MO
Classic Aire is always dependable, courteous, neat and a good deal.
Abdul - Creve Coeur, MO
Quick service and worked with my schedule
Patrice - Creve Coeur, MO
Was a quick fix and especially illy important during another St. Louis heat wave in late September.
Marilyn - Creve Coeur, MO
John - Creve Coeur, MO
Our service Tech Patrick, was thorough, efficient and friendly.
Saved a ton of money from other bid
Robert - Creve Coeur, MO
Technicians and office staff was helpful, professional and very competitive on the service and components I needed for my AC Thx
Henrietta - Creve Coeur, MO
Arrived on time, performed services in a timely manner. Great personality!
Roger was great! Highly recommend
Chris - Creve Coeur, MO
Roger was thorough and detailed. He did exactly what I expected an inspector to do which was to let us know if we should have any concerns. He sat down with us and talked through everything. Great guy!
Julio - Creve Coeur, MO
I have always had complete confidence in the quality of the work and advice of the service professional.
very efficient and polite
Shirley - Creve Coeur, MO
Serviced heating system
Fall clean & check on 2 furnaces, also servicing humidifier
Maintenance on 3 carrier furnaces and humidifiers
Clean and ce, change filters
Fall clean & check on 15yr old Bryant furnace
Serviced heating system
Maintenance on Comfortmaker furnace and humidifier.
Serviced heating system and humidifier
Maintenance on York electric furnace.
Cleaned & checked 2 gas furnaces. Inspected heat exchanger & flue venting. cleaned burners, pilot & flame sensor. Checked voltage & amp draw of motors. Test capacitors. Clean and check 2 humidifiers, replace pads, checked water flow and drains. Replaced flow control orifice for second-floor humidifier.
Maintenance on Bryant air handler.
modulating condensing furnace was operating when I arrived. Found combustion blower with excessive water. I found drain outlet of Ferncos clogged. Removed combustion blower assembly and unclogged and cleaned out Ferncos boot. Reattached Blower and PVC vent. Found continuous blower speed set very high. Drawing 6.3 amps @ 1,500 cfm. I set up continuous blower speed and cooling speed to proper CFM per condensing and evaporator unit sizing. Cool: 1400, 4.4A. Cont. Blower: 2.5A. Customer signed up for maintenance agreement. I documented equipment.
Cleaned & checked 2 gas furnaces. Inspected heat exchangers & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitors. West system: Blower: 3.6A. Inducer: 1.02A. Gas pressure: 3.5 inches water column. Temperature rise: 57 . Supply: 135 . Return: 78 . East system: Blower: 3.8A . Inducer: 1.3A . Gas pressure: 3.4 inches water column. Temperature rise: 60 . Supply: 140 . Return: 80.
Serviced two heating system and humidifier
Cleaned and checked mini split system. Clean filters. Vacuumed evaporator coil and ionizer. Check temperature rise. 30. Cleaned condenser coil. Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. cleaned filter. Checked drain.
Emergency service on Lennox air handler
John’s note: returned November 3, 2017: replaced broken collector box. Replaced condensate trap (included with collector box kit). Install vinyl drain tubing. Re-installed combustion blower. Replaced broken combustion blower mounting screw. Tested heat cycle. Checked drain.
Serviced heating system
Fall clean & check on 9yr old Lennox furnace, also servicing humidifier