There are 8,373 people living in Des Peres, MO and 3,051 households. Classic Aire Care is only a phone call away from making sure your family comfortable in your beautiful Des Peres home. Classic Aire Care is ready to assist you with any repair, maintenance or system installation. Looking to upgrade your system? One of our highly trained Project Managers is ready to walk you through several heating and cooling systems that are sure to fit your needs. Head on over to Des Peres Park! We’ll call you when we’re on our way.
Classic Aire Care is only a phone call away from making sure your family is comfortable in your beautiful Des Peres home.
for Des Peres, MO
Our Reviews by City
Annual Furnace System Servicing and Review
John - Des Peres, MO
Service was excellent. On-time, quietly competent and quickly done.
Nadine - Des Peres, MO
Did a great job diagnosing the problem and performing the necessary fix.
When he arrived he diagnosed the problem within minutes, very Satisfied
Vern - Des Peres, MO
We won't have the A/C repaired totally until Roger can secure a part from Carrier, so far we are very pleased with the fine service we are receiving from CLASSIC AIR CARE! We appreciate the temporary fix that Roger performed!
Professional, Efficient Service with a Smile
Maggie - Des Peres, MO
Moving Day. Frigid temperatures. No heat. We were in a jam and Classic Aire Care saved the day! We are so thankful for the professional and speedy attention to our furnace mishap. With Sean's help, we were able to get back on (a much warmer) track to move into our new home. Thank you!
Alina - Des Peres, MO
Mary - Des Peres, MO
great service. Always prompt and courteous.
Kathy - Des Peres, MO
they don't hesitate to come back free of charge after a service call if something isn't right.
Very thorough and professional - excellent
Joe - Des Peres, MO
Great job and friendly service
Ken - Des Peres, MO
As it turned out we had an area of common interest (hobby) which added some friendly conversation while not interfering with the repair.
Great service. Brian is excellent and professional.
Jane - Des Peres, MO
Frank - Des Peres, MO
courteous, competent, thourough
Gene - Des Peres, MO
Experienced techs provide help on questions
Excellent timely service.
Stephanie - Des Peres, MO
I am happy with Classic Aire Care's service. They were able to provide same day service, all the employees were friendly and customer oriented and the price was reasonable. I will definitely continue to use them in the future.
Great Service as Always
Rick - Des Peres, MO
Susan - Des Peres, MO
Polite, professional, technician.
Tina - Des Peres, MO
Full of Knowledge
Lisa - Des Peres, MO
Classic Aire Care has been wonderful to work with. They are honest, dependable and very knowledgable. Why even consider anyone else?? I am not.
Sean does it right
Jane - Des Peres, MO
Hi - SEan has been to my home several times now, and represents Classic Aire very well. He is courteous, friendly, focused on the work, and a problem solver.
Gas Leak Service for a Furnace not yet a year old
Phil - Des Peres, MO
Service was excellent but very disappointed to learn the source of the gas leak was a defective coupling you used for the installation of the furnace, not yet a year old. Very disappointed.
The men were very nice and hopefully solved the problem
Kay - Des Peres, MO
Found furnace locked out: 2flashes. Found flame current very weak. Cleaned flame sensor and tested: 2.2uA. Found blower dropped out apoun engaging stage 2 heat!! Corrected wiring of blower. Inducer: 0.32/1.04A. Blower: 3.9/5.1A. Checked temperature rise: 30/48. Checked draft: 0.04”. Does not appear to have proper flue liner in masonry chimney. Suggestions: Furnace is about 22 years old. replace furnace soon. Recommend installing new flue liner to protect chimney.
Cleaned & checked condensing gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked drain. Checked voltage & amp draw of motors. Blower: 1.3A/4.9A . Inducer: 0.2/0.62A . Gas pressure: -/1.7/3.5 inches water column. Temperature rise: H:70 . Clean and check humidifier, replace pad, checked water flow and drain. The humidifier pads that we delivered are the wrong size . I am returning three #12 humidifier pads to the office . need to refund customer $49.
I removed blower door to find flashing code 4: open primary limit. There was no voltage to limit and inducer would periodically turn on. I replaced furnace control board, including new igniter. Tested operation. Inducer: .37 A. Blower: 4.0 A.
Fall maintenance today for the furnace!
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Replaced air filter. Clean and check humidifier, replace pad, checked water flow and drain. Blower: 4.8A. Inducer: 1.18A. Gas pressure: 3.5 inches water column. Temperature rise: 54 . Supply: 128. Return: 74 . Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Compressor: 8.2A . Condenser fan: 0.7A. Blower: 5.4A . ambient: 56 . liquid line: 62. suction line: 44 . metering device: TXV . Return air: 71 . supply air: 50.
Serviced furnaces and humidifiers
I removed motor module from murder. I’m doubt motor windings: OK. Installed new module and adapter ring and harness. Tested operation and found Motor would not run. Blower wheel rocks back and forth. I tested wiring harness continuity. I put old motor module back on for temporary cooling. Need to return with another replacement module. Work suggested: need to call Carrier and double check part numbers. Need to order New motor module. Call customer ASAP when availability is known.
No cooling by passed blower module till part is replaced
Serviced air conditioner and replaced filter
Repaired short in wiring..on furnace
AC maintenance! Replace run capacitor for blower and dual capacitor for condenser
Replaced bad pressure switch
Replaced Lennox uv bulb
Clena and chec
No heat, clogged pressure switch
Serviced furnace and humidifier and replaced filter
Clean and check 2systems
Clean and check,
Clean and check, add3 apco and and duct cleaning
Diagnosed a bad inducer motor.