Heating, Cooling & Plumbing Services in Florissant, MO
Classic Aire Care has been providing heating, cooling, and plumbing services in the Florissant area for decades. Whether your furnace needs a tune-up or your air conditioner needs replacing, Classic Aire Care has the staff to get the job done. Our highly trained, licensed service technicians and plumbers get the job right the first time.
If you live in the Florissant area and you need plumbing service or HVAC repair, call us at 314-352-1111.
Heating Services in Florissant, Missouri
Classic Aire Care offers a full list of heating system services to keep your Florissant home warm and comfortable, even in the chilly Missouri winters. In fact, we have been providing heating services in the area since 1926 and will continue to exceed your expectations every time you call us for service. Whether you need a new heating system installed or are looking for routine maintenance and repairs to keep your existing unit running at its best, you can trust our experienced team. Our heating services include:
- Florissant furnace repair, maintenance, and installation
- Florissant boiler repair, maintenance, and installation
- Florissant heat pump repair, maintenance, and installation
- Florissant ductless mini-split repair, maintenance, and installation
We service all makes and models of heating systems and will deliver exceptional service at fair pricing.
If you are in need of heating services for your Florissant, Missouri home, don’t hesitate to call Classic Aire Care today at 314-352-1111.
Florissant Cooling Services
While winter is frigid in Florissant, summers are hot and humid. A working cooling system is just as much of a necessity as a working heating system, and we have your needs met. Our expert HVAC pros can come to your home and diagnose any problems with your air conditioner or heat pump, then expertly repair them so you can enjoy a comfortable, properly cooled home again. If your home is in need of a new cooling system, we will help you choose one, and then install it expertly to optimize its function. We also repair, maintain, and service air conditioners of all types.
Contact Classic Aire Care today to discuss your cooling system needs.
Florissant Plumbing Services
In addition to heating and cooling services, the team at Classic Aire Care offers a full list of plumbing services. If you are having trouble with your plumbing systems, we can help. Our plumbing services include:
- Sewer, drain, and gas pipe repairs
- Drain or sewer cleaning
- Repair for all major plumbing systems, including toilets, sinks, water heaters, and sump pumps
- Garbage disposals
- Sewer inspections
- Plumbing system inspections.
Contact us online today or call 314-352-1111 to schedule reliable plumbing services in Florissant.
Emergency Repairs in Florissant, Missouri
Heating, cooling, and plumbing systems don’t keep regular business hours. that’s why we offer emergency repairs whenever they are needed. We are available 24 hours a day, 7 days per week, whenever a problem strikes. Don’t suffer through a hot weekend or wonder what to do about that burst pipe. Let the experts at Classic Aire Care handle the task for you, so you can get back to enjoying your home to the fullest.
Do you have an emergency HVAC or plumbing need? Call Classic Aire Care for prompt emergency service in Florissant.
There are an estimated 51,443 people living in Florissant, MO, making it the 13th largest city in Missouri. Classic Aire Care might not be able to clean and check the air conditioners and furnaces of all 21,247 households, but we can take care of yours! Whether you need a repair or to complete your annual maintenance, Classic Aire Care is a phone call away. Annual maintenance is one of the best things you can do to make sure your furnace and air conditioner are running properly and working efficiently. Whether you are in a brand new house or one of Florissant’s charming historic homes, Classic Aire Care is here for you with 24-hour emergency service.
for Florissant, MO
Our Reviews by City
John was excellent. He took the time to explain a few strategies I needed to be reminded about.
Mary - Florissant, MO
I delayed in filling this out to be sure our AC kept working. John was very professional the entire time in explaining what to him must be very basic facts in keeping our AC bills in daily usage down. I appreciated his quality of service.
Sandra - Florissant, MO
I don't have one
Happy customer - Florissant, MO
John arrived promptly, checked everything insid and out. My air conditioner got a clean bill of health. Love these guys at Classic Aire.
Sharon - Florissant, MO
Wanda - Florissant, MO
great service affordable price
Karen - Florissant, MO
Dan - Florissant, MO
John was on time (early actually), very friendly, and professional during this job. I appreciate his time and knowledge.
Vicki - Florissant, MO
pls provide copies for my records
Barbara - Florissant, MO
I need a copy of the work results from today at 3633 Marietta for my records - I can't really rate the service since it was done at a rental property until I speak to my renter
Sarah - Florissant, MO
They came out to do springtime maintenance on the air conditioning unit they installed in November and found a problem that they came back and fixed, at no cost to me!
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Replaced air filter. Blower: 5.7A . Inducer: 1.2A Temperature rise: 48 . Supply: 119. Return: 71 .
I found humidifier drain tubing clogged! I cleared the blockage. Found humidifier solenoid valve stuck open! Also due for water panel replacement. I replaced furnace air filter. Tested operation. Suggestions: Replace humidifier with larger model: $716. PMA Discount applies.
Cleaned & checked 2 gas furnaces. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitors. First floor system: flame sensor current dropping below minimum. Clean flame sensor and tested: 2.7 micro amps. Replaced air filter. Blower: 6.6A . Inducer: 1.38A . Gas pressure: 3.4 inches water column. Temperature rise: 47 . Supply: 114. Return: 67 . Second floor system: Replaced air filter. Blower: 5.8A . Inducer: 1.45A. Gas pressure:3.4 inches water column. Temperature rise: 46 . Supply: 115. Return: 69 .
Furnace maintenance today! Signed up for new maintenance plan
AC maintenance! System looks good
Serviced ac and furnace
Ac check up
I found condenser fan motor bearings going bad. Found condenser fan motor capacitor very weak. Motor drawing 20% over full load amps. Also compressor capacitor very weak. Compressor drawing high amps. Freon level only slightly low: within 10 degrees of charging chart. Replaced fan capacitor for temporary cooling and tested amp draw: 0.86A.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Cleaned condenser coil. Checked filter: dirty MERV 16. More than 1” drop. I installed temporary 1 inch filter. Need to order MERV 16 air cleaner media. Checked Freon level: Low again. I talked of Freon level enough to get system cooling nearly full capacity. System is still approximately 20% low on Freon. Superheat: 16. Sub :: zero.
Cleaned and checked air conditioner. Checked and cleaned out drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Compressor: 14.9A. Condenser fan: 1A . Blower: 4.7A, 1400. ambient: 90 . liquid line: 92 . suction line: 49. metering device: TXV . Return air: 71 . supply air: 51.5 . wet bulb: 56.