for Frontenac, MO
Our Reviews by City
Excellent job. Attention to detail.
James - Frontenac, MO
Excellent job. Attention to detail.
Kim - Frontenac, MO
Great job, provided me update throughout.
Classic Aire to the Rescue
Alex - Frontenac, MO
Jeff systematically checked all options to restore the NEST thermostat to operate. Thermostat was a year old and was faulty. Thanks to Jeff for installing new Nest thermostat!!!
Mark - Frontenac, MO
Very positive experience: both office staff and service technician “John”.
Very professional. Excellent service
Marybeth - Frontenac, MO
Prompt, Courteous, and Professional
Bob - Frontenac, MO
Roger of Classic Aire Care arrived promptly on time, friendly and courteous, timely efficient and above all professional. Kudos!
Great Service per Planned Maintainance Agreement
Celeste - Frontenac, MO
Very nice job cleaning and explaining the system
John - Frontenac, MO
Great service - Frontenac, MO
Leila - Frontenac, MO
We were pleased with our service. We would appreciate a hard cover receipt for the installation of our new air conditioner that we had installed on July 19. The installers said we would receive that by email.
Fall maintenance today for the furnace! Replaced humidifier pad, capacitor, and installed a UV purifier
Cleaned and checked 3 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. Replaced air filters. First floor system: 5405: Compressor: 15.8A . Condenser fan: 1.13A . Blower: 1870 . ambient:75 . liquid line: 82. suction line: 50 . metering device: TXV . Suction pressure: 100(33) . head pressure:271(89) . Return air: 69.5. wet bulb: 58 . Second floor system: checked Freon pressures and found suction pressure low and superheat very high: 35 degrees superheat. I added 1.5 pounds 410A. Reducing superheat but, thermostatic expansion valve is stuck. East addition system: Compressor:5.6A . Condenser fan:0.62A . Blower: 2.5A . ambient: 80 . liquid line: 99 . suction line: 41 . I found basement pressure negative: -.014 inches water column with both air-conditioners running. Basement has a large return air vent pulling a lot of air out of the basement. Needs makeup air. Work
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. North system (kitchen): Replaced air cleaner media. Added 2# of 410A Freon. Compressor: /12.8A . Condenser fan: 0.9A. Blower: 1.8/6.7A . ambient: 76. liquid line: 99, dirty . suction line: 49 . metering device: TXV. wet bulb: 58. South system (bedrooms): Replaced clogged air filter. I found blower not staging properly! I installed an isolation relay for proper blower speeds for cooling stage 1 and 2. Compressor: 4.4/8.3A. Condenser fan: 0.65A. Blower: 1.3/4.0A . ambient: 77 . liquid line: 74 . suction line: 44 . metering device: TXV . Return air: 67. supply air: 49/ . wet bulb: 58. Work suggested: North system: Replace air cleaner media every 6 months. Freon leak search: $189. Freon leak repair: $? South system: replace air filter every month or two.
Installed condensate pump!
Replaced evaporator coil! Returning to install condensate pump
Replaced warranty evaporator coil!
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Tested in dehumidification mode: Compressor: 15A Condenser fan: .95A . Blower: 3.4A, 1400 . ambient: 71 . liquid line: 78. suction line: 48 . metering device: TXV . Suction pressure: 107(37) . head pressure: 250(83). Return air: 70.5 . supply air: 48.5
Replaced current Nest stat with NEW
Serviced ac units and replaced drain hoses and filter
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. Checked filters. Main system: Compressor: 11.6A . Condenser fan: 1.15A . Blower: 7.1A. ambient: 74. liquid line: 76 . suction line: 52 . metering device: TXV . Suction pressure:109(36) . head pressure:260(86) . Return air: 73. supply air:51.5 . wet bulb: 59 . Bedroom system: Compressor: 7.5A Condenser fan: 0.72A. Blower: 4.5A . ambient: 76 . liquid line: 83 . suction line: 52 . metering device: TXV . Suction pressure: 120(41). Return air: 71 . supply air: 51.5 . wet bulb:58 .