for Frontenac, MO
Our Reviews by City
Very professional. Excellent service
Marybeth - Frontenac, MO
Prompt, Courteous, and Professional
Bob - Frontenac, MO
Roger of Classic Aire Care arrived promptly on time, friendly and courteous, timely efficient and above all professional. Kudos!
Great Service per Planned Maintainance Agreement
Celeste - Frontenac, MO
Very nice job cleaning and explaining the system
John - Frontenac, MO
Great service - Frontenac, MO
Leila - Frontenac, MO
We were pleased with our service. We would appreciate a hard cover receipt for the installation of our new air conditioner that we had installed on July 19. The installers said we would receive that by email.
Pleasant, efficient prompt
Ken - Frontenac, MO
very clean and profesinal
Ken - Frontenac, MO
Courteous and professional
Amy - Frontenac, MO
Liping - Frontenac, MO
very perfectional service. thanks.
Replaced warranty stat
Bryant air conditioner
Kitchen system: 1165: found system very low on Freon. (R22). I charged up for temporary cooling. 2.5#. Suction pressure: 70. Ambient: 75. Compressor: 5.8 A. Fan motor: 1.3 A. Work suggested: recommend replacing West (kitchen) system. Steve H. scheduled to price new 8AM June 5.
Work Done: Cleaned and checked 2 air conditioners. Remove condensing unit covers. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. Second floor system: Replaced air filters. Compressor:4.9A .Condenser fan: 0.9A . Blower: 1.5A, 690cfm .ambient: 73 .liquid line: 81 .suction line: 37 .metering device: Piston . Return air: 71.5 .supply air: 46.5. wet bulb:57 . First floor system: Compressor:13.6A .Condenser fan: 1.15A . Blower: 7.5A, 1800. ambient: 74.liquid line: 77 .suction line: 51 .metering device: TXV . Return air: 69.supply air: 45.5 .wet bulb:56.
Spring maintenance for both ac systems!
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. Second floor system: Compressor: .Condenser fan: . Adj Blower: 1440 .ambient: .liquid line: .suction line: .metering device: . Suction pressure: .head pressure: . Return air: 66 .supply air: 47 .wet bulb:53 . First floor system: dirty pleated air filter against undersized filter opening. I replaced dirty air filter. I cut furnace return air opening larger for more efficient air movement. Comp
Replaced warranty heat exchanger
First floor system: XJ1G: Replaced gas valve. Checked manifold gas pressure. Sauna room: replaced weak batteries in remote. tested mini split operation. Heating OK. Temperature rise: 22. Discharge: 168. Liquid line: 90. Ambient: 38. System amp draw: 5.6. Liquid line dryer is very rusty.
Installed 17 gal bypass humidifier and replaced filter
Scheduled maintenance on two Trane furnaces.