for Frontenac, MO
Our Reviews by City
Excellent job. Attention to detail.
James - Frontenac, MO
Excellent job. Attention to detail.
Kim - Frontenac, MO
Great job, provided me update throughout.
Classic Aire to the Rescue
Alex - Frontenac, MO
Jeff systematically checked all options to restore the NEST thermostat to operate. Thermostat was a year old and was faulty. Thanks to Jeff for installing new Nest thermostat!!!
Mark - Frontenac, MO
Very positive experience: both office staff and service technician “John”.
Very professional. Excellent service
Marybeth - Frontenac, MO
Prompt, Courteous, and Professional
Bob - Frontenac, MO
Roger of Classic Aire Care arrived promptly on time, friendly and courteous, timely efficient and above all professional. Kudos!
Great Service per Planned Maintainance Agreement
Celeste - Frontenac, MO
Very nice job cleaning and explaining the system
John - Frontenac, MO
Great service - Frontenac, MO
Leila - Frontenac, MO
We were pleased with our service. We would appreciate a hard cover receipt for the installation of our new air conditioner that we had installed on July 19. The installers said we would receive that by email.
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. North system (kitchen): Replaced air cleaner media. Added 2# of 410A Freon. Compressor: /12.8A . Condenser fan: 0.9A. Blower: 1.8/6.7A . ambient: 76. liquid line: 99, dirty . suction line: 49 . metering device: TXV. wet bulb: 58. South system (bedrooms): Replaced clogged air filter. I found blower not staging properly! I installed an isolation relay for proper blower speeds for cooling stage 1 and 2. Compressor: 4.4/8.3A. Condenser fan: 0.65A. Blower: 1.3/4.0A . ambient: 77 . liquid line: 74 . suction line: 44 . metering device: TXV . Return air: 67. supply air: 49/ . wet bulb: 58. Work suggested: North system: Replace air cleaner media every 6 months. Freon leak search: $189. Freon leak repair: $? South system: replace air filter every month or two.
Installed condensate pump!
Replaced evaporator coil! Returning to install condensate pump
Replaced warranty evaporator coil!
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Tested in dehumidification mode: Compressor: 15A Condenser fan: .95A . Blower: 3.4A, 1400 . ambient: 71 . liquid line: 78. suction line: 48 . metering device: TXV . Suction pressure: 107(37) . head pressure: 250(83). Return air: 70.5 . supply air: 48.5
Replaced current Nest stat with NEW
Serviced ac units and replaced drain hoses and filter
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. Checked filters. Main system: Compressor: 11.6A . Condenser fan: 1.15A . Blower: 7.1A. ambient: 74. liquid line: 76 . suction line: 52 . metering device: TXV . Suction pressure:109(36) . head pressure:260(86) . Return air: 73. supply air:51.5 . wet bulb: 59 . Bedroom system: Compressor: 7.5A Condenser fan: 0.72A. Blower: 4.5A . ambient: 76 . liquid line: 83 . suction line: 52 . metering device: TXV . Suction pressure: 120(41). Return air: 71 . supply air: 51.5 . wet bulb:58 .
Bedroom system: Found low on Freon. Leak checked system and found evaporator coil leaks. Need new coil. Found dual run capacitor weak: 14%low, fan side. Replaced capacitor and tested amp draw. Living area system: Found slightly low on Freon. Topped off with R22 Freon. Work suggested: bedroom system: replace evaporator coil: $1479.
Replaced warranty stat