for Jennings, MO
Our Reviews by City
Cheryl - Jennings, MO
Excellent, timely service!
Susie - Jennings, MO
Good service from the technician
Joann - Jennings, MO
It is good to have the same person to come and take care of my furnace and a/c. That person then knows how it is performing from year to year.
Cheryl - Jennings, MO
Great overall , very nice , explained what I didn't know. Very helpful.
Naomi - Jennings, MO
There should be more like him.
Kirk - Jennings, MO
i've been a loyal customer with Classic Aire Care for over 10yrs now and ha been very pleased with the service i've received. Thank you for all you do.
Karen - Jennings, MO
tech was very pleasant just not like signing screen with nothing on it but the words i agree to pay amount due even though know is no charge
Always on top of the changing seasons.
Robert - Jennings, MO
I've always been more than satisfied with the care and service Classic provides. Basically the same company my father called when we moved into this house over 50 years ago.
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Customer complaint: customer heard a banging noise for a few minutes. Found no unusual noises at this time. Checked voltage & amp draw of motors. Tested capacitors. Found run capacitor weak: 24%low. Replaced capacitor and tested amp draw. Clean and check humidifier, replace pad, checked water flow and drain. Calibrated h-stat.
Cleaned and checked gas boiler. When I turned up the thermostat boiler control would not bring on burners. When I turned knob for limit control setting burners came on! Water temperature was 45 degrees below limit setting. Boiler control should not have kept burners off. It is working properly now though. Boiler may need new control board. inspected heat exchanger & flue venting. Cleaned condenser coil. Checked voltage & amp draw of pump. I bled air from accessible radiators. tested system expansion rate. System expansion tank is waterlogged. I partially drained system and trained expansion tank. Bled air from radiators. Suggestions: boiler may need new control board if it continues to act up.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Tested zoning system. Checked filter. Compressor: 0.65A. Condenser fan:1.2A . Blower: 5.0A,1355 .ambient: 86 .liquid line: 93 .suction line: 58.metering device: TXV. Suction pressure: 116(39) . Return air: .supply air: .wet bulb: .
Replaced warranty blower motor
Spring maintenance on AC system! Replaced weak dual capacitor
Cleaned air conditioner
No heat, pressure switch clogged
No heat pilot out,found large crack in heat exchanger...shut off furnace...getting estimate on new furnace
I found blower motor windings going bad. I replace blower motor and capacitor. Tested heating operation. High stage blower amp draw: 3.0 A. RA: -.6”.