for Lake Saint Louis, MO
Our Reviews by City
difficulty in scheduling
Bryan - Lake Saint Louis, MO
Corey was fantastic and knowledgeable! We had trouble scheduling this visit, When we signed up for the service agreement last summer we were informed that we would be called to set up an inspection before winter - it has been months before our first service visit.
Rod S - Lake Saint Louis, MO
Called at 345pm. Had Jim (the Tech) on site by 445. Received call saying when he would be there. Went over all the pricing. Very friendly. Took over Survant account when they closed. New customer and was very impressed.
Sharon - Lake Saint Louis, MO
John was very professional and helpful
Great Information and Service!!
Donna - Lake Saint Louis, MO
We are very thankful for Jim's time and ingenuity in explaining our issue and the best ways to solve the issue now and in the future. What a great company and great employee! Even though we don't foresee any issues arising soon, we know we can count on Classic Aire Care if they do. Thanks!!
Great on-time service
Tom - Lake Saint Louis, MO
great service, very professional,
Robert - Lake Saint Louis, MO
would highly recommend your business to my friends.
Jim is a very friendly person. He is very knowledgable of my system and has been taking good care of it over the past 3 years.
James - Lake Saint Louis, MO
I would highly recommend Classic Aire Care to my friends and neighbors.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Low! Superheat: 25. Sub cooling: zero. Cleaned condenser coil. Checked filter. Compressor: 6.3A .Condenser fan: .85A . Blower: 4.0A .ambient: 79 . Subcooling : 9 .suction line: 61 .metering device: TXV . Suction pressure: 126 . Superheat: 18. head pressure: 278 . Return air: 73 .supply air: .wet bulb: 62.5 .
Ac repair on Lennox system. Condensor fan had to be replaced
Ac repair onmlennox system. Fan motor and capacitors replaced
Performed gas inspection for home sale. All pass.
58 PA V
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Found run capacitor weak: 11%low. Replaced capacitor and tested amp draw. Blower: 7.7A . Inducer: 1.5A . Temperature rise: 46 . Supply: 122 . Return: 76 .
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. furnace is tripping hi limit. I set blower speed and manifold pressure for proper temperature rise. Blower:5.3A . Inducer: 1.77A . Gas pressure: 3.0 inches water column. Temperature rise: 68 . Supply:143 . Return: 75 .
Clean & check on Lennox Airhandler
Clean & check on carrier airhandler
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor(.4 µA). Checked voltage & amp draw of motors. Test capacitor. Blower: 6.1A . Inducer:1.45A . Gas pressure: 3. And inches water column. Temperature rise: 55 . Supply: 132 . Return: 77 . Flame current now: 2.8 µA. Found draft inducer motor stopping! Main control board is dropping out voltage to inducer. Needs new board. Replaced faulty CO monitor under warranty.