for Lake Saint Louis, MO
Our Reviews by City
Tom - Lake Saint Louis, MO
Jeff was friendly prompt and knowledgeable
Sharon - Lake Saint Louis, MO
Dependable and professional technicians and customer service.
Lindell - Lake Saint Louis, MO
From making the service appointment to completion of service it is a pleasure to do business with Classic Aire Care. Service truck appeared new and technician performed a thorough service on our HVAC and Humidifiers.
Patricia - Lake Saint Louis, MO
Corey, was fantastic - quick, knowledgeable, and respectful of our time commitments. Second time he has serviced our equipment.
Excellent service, fast, and reliable!!
Jamison - Lake Saint Louis, MO
Our service tech Sean was outstanding! Showed up identified the problem and had it fixed in no time at all! If we have any more issues we will requesting him for our service! We also had Jerry come and install our new system and he was great too, our dogs were there the whole time and took extra care to make sure they were comfortable through out the day! Love classic air care and the employees!
Sue - Lake Saint Louis, MO
James - Lake Saint Louis, MO
Experience so far has been great. Need parts ordered to complete repairs
Jonathon - Lake Saint Louis, MO
difficulty in scheduling
Bryan - Lake Saint Louis, MO
Corey was fantastic and knowledgeable! We had trouble scheduling this visit, When we signed up for the service agreement last summer we were informed that we would be called to set up an inspection before winter - it has been months before our first service visit.
Rod S - Lake Saint Louis, MO
Called at 345pm. Had Jim (the Tech) on site by 445. Received call saying when he would be there. Went over all the pricing. Very friendly. Took over Survant account when they closed. New customer and was very impressed.
Fall clean & check on 2 14yr old furnace
Maintenance for the furnace! Replaced pure air kit!
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Replaced air filter. Blower: 4.5A . Inducer: 2.25A . Gas pressure: 3.4 inches water column. Clean and check humidifier, replace pad, checked water flow and drain.
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Checked filter. Check humidifier. Found relay board shorting out intermittently! Also motor bearings were very tight at start up.
Found dual run capacitor bad. Replaced capacitor and tested amp draw. Compressor: 7.7A. Fan: .7A. Also, condenser coil is dirty.
Emergency service call--blown capacitor--new planned maintenance agreement customer
D1BF: Customer stated second floor air conditioner breaker has been tripping. Tested system operation. Check circuit breaker and connections. One pole of breaker is slightly warmer than the other pole. May have bad Internal connection. Compressor:12.5A .Condenser fan: 1.3A .ambient:80 .liquid line: 93.suction line: 40 .metering device: piston . Suction pressure: 67(39) . Return air: 75.supply air: 53.5 .wet bulb: 63 . Condenser fan motor draws slightly more than nameplate, but identical unit for first floor dries the same amount. Fan motor bearings are good. Compressor is starting OK under no load condition. Compressor does not have hard starting components. Compressor could trip breaker if starting under loaded condition.
Diagnosed a/c system issues
Clean & checked a/c installed APCO