Lake Saint Louis
for Lake Saint Louis, MO
Our Reviews by City
Great job. Peace of Mind, now.
Anthony - Lake Saint Louis, MO
Very thorough and explains what he's doing.
Good customer service and information shared with me
Krayle - Lake Saint Louis, MO
Very helpful with size of filters to use and how to order
Rod - Lake Saint Louis, MO
I cannot say enough on how impressed I was everyone I spoke with on the phone to the tech that showed up. Very professional, friendly, and constantly informing us of what was going on.
Tom - Lake Saint Louis, MO
Jeff was friendly prompt and knowledgeable
Sharon - Lake Saint Louis, MO
Dependable and professional technicians and customer service.
Lindell - Lake Saint Louis, MO
From making the service appointment to completion of service it is a pleasure to do business with Classic Aire Care. Service truck appeared new and technician performed a thorough service on our HVAC and Humidifiers.
Patricia - Lake Saint Louis, MO
Corey, was fantastic - quick, knowledgeable, and respectful of our time commitments. Second time he has serviced our equipment.
Excellent service, fast, and reliable!!
Jamison - Lake Saint Louis, MO
Our service tech Sean was outstanding! Showed up identified the problem and had it fixed in no time at all! If we have any more issues we will requesting him for our service! We also had Jerry come and install our new system and he was great too, our dogs were there the whole time and took extra care to make sure they were comfortable through out the day! Love classic air care and the employees!
Sue - Lake Saint Louis, MO
James - Lake Saint Louis, MO
Experience so far has been great. Need parts ordered to complete repairs
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Checked filter. Blower: 3.6A . Inducer: 1.0A. Temperature rise: 55 . Supply:122 . Return: 67.
Furnace maintenance today!
Fall maintenance today! Also renewed maintenance agreement!
Ac maintenance for both systems!
AC maintenance performed!
AC maintenance! Signed up for perpetual maintenance plan!
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level: superheat: T+11. Checked filter. Testing basement pressure with new make up air vents installed: .003 inches water column. Compressor: 7.45A . Condenser fan: 0.7A . Blower: 3.6A. ambient: 88 . liquid line: 98 . suction line: 57. metering device: piston . Suction pressure:71(42) . Return air: 73.5 . supply air: 54.5 . wet bulb: 62. Cleaned condenser coil. Compressor is noisy. Freon level is slightly low. Superheat: target +11. Last year super he was target +5. System uses older type of Freon.Work suggested: filter cover. Recommend budgeting for new air conditioner. Lisa is scheduling a project manager.
Second floor system: I found system very low on Freon. Found evaporator coil oily and leaking Freon. Needs new evaporator coil. I charged up system for temporary cooling. Expect Freon to last a week or two.Work suggested: system uses old type of Freon. Recommend replacing air conditioner for second floor system. John C. to call customer.
HD spring maintenance! Added 1lb of r22 and filter replacement
Found high-pressure safety tripped. I reset safety. Condenser coil is in need of thorough flushing. dual capacitor weak: 24% low on the fan side. Also, condenser fan motor bearings have play in rear bearing. I replace the dual capacitor. Tested motor amp draw: .97 A. FLA: 1.1 A. I also found blower capacitor for furnace blower weak: 14% low. I adjusted oversized blower for proper temperature drop across oversized evaporator coil. Adj. SC. Wet bulb: 69. Temperature drop: 22. T: 17.5. Suction: 150. Superheat: 9. Sub cooling: 10.Work suggested: condenser fan motor may quit working. Replace condenser fan motor: $583. Replace blower capacitor: $113. Condenser coil cleaning: $122.