Lake Saint Louis
for Lake Saint Louis, MO
Our Reviews by City
Rod - Lake Saint Louis, MO
I cannot say enough on how impressed I was everyone I spoke with on the phone to the tech that showed up. Very professional, friendly, and constantly informing us of what was going on.
Tom - Lake Saint Louis, MO
Jeff was friendly prompt and knowledgeable
Sharon - Lake Saint Louis, MO
Dependable and professional technicians and customer service.
Lindell - Lake Saint Louis, MO
From making the service appointment to completion of service it is a pleasure to do business with Classic Aire Care. Service truck appeared new and technician performed a thorough service on our HVAC and Humidifiers.
Patricia - Lake Saint Louis, MO
Corey, was fantastic - quick, knowledgeable, and respectful of our time commitments. Second time he has serviced our equipment.
Excellent service, fast, and reliable!!
Jamison - Lake Saint Louis, MO
Our service tech Sean was outstanding! Showed up identified the problem and had it fixed in no time at all! If we have any more issues we will requesting him for our service! We also had Jerry come and install our new system and he was great too, our dogs were there the whole time and took extra care to make sure they were comfortable through out the day! Love classic air care and the employees!
Sue - Lake Saint Louis, MO
James - Lake Saint Louis, MO
Experience so far has been great. Need parts ordered to complete repairs
Jonathon - Lake Saint Louis, MO
difficulty in scheduling
Bryan - Lake Saint Louis, MO
Corey was fantastic and knowledgeable! We had trouble scheduling this visit, When we signed up for the service agreement last summer we were informed that we would be called to set up an inspection before winter - it has been months before our first service visit.
I found flame sensor current weak. I removed and cleaned flame sensor. Tested operation. Flame current: 2.7 µA. Working well now.
Returned March 5, 2018: John’s notes: I arrived with a new scale separator. Wrong part. I happened to have the proper part on my truck. I replaced distributor tray. Also, I corrected the city and zip of the address.
Replaced gas valve under parts warranty
Replaced pressure switch
Clean and check
Approximately three year old tightly constructed ranch. water vapor has been condensing on above grade basement exterior wall. Checked indoor conditions. Has high indoor humidity. Humidity source appears to be coming from the basement. Concrete may still be curing. Main level humidity: 49%, dew point: 45. Basement: humidity: 53%. Dew point: 47. Customer now has two dehumidifiers going at this time. Found blower set too high for cooling speed. Air-conditioner has not been dehumidifying properly during the summers. Has oversize blower and coil. I adjusted blower. Cooling: low. Heating: high. Check total external static pressure: about 1 inch on high-speed. Has .6 inch drop across dirty pleated filter. Needs new filter.
Clean and check
Clean and check electric furnace. Tested heating elements. Tested sequencers. Checked voltage & amp draw of blower. Check temperature rise. 65. Test capacitor. Voltage: 241. System amp draw: 102.5. Replaced air filter. Supply: 136. Return: 69.