There are 22,995 people living in Webster Groves, MO and 9,156 homes. Classic Aire Care is ready to help you with any repair or maintenance needed on your home. Whether you are ready to upgrade your system or still have the original heating and cooling system in your historical Webster Groves abode, Classic Aire Care and our team of professionals are ready to assist you. Head on over to Euclid Records or Serendipity Homemade Ice Cream! We’ll call you when we’re on our way.
Classic Aire Care has been providing heating and cooling services in the Webster Groves area for decades. Whether your furnace needs a tune up or your air conditioner needs replacing, Classic Aire Care has the staff to get the job done. Our highly trained, licensed service technicians and installers get the job right the first time. If you live in the area and you need a furnace or air conditioner repair, maintenance or install call us at 314-300-6755.
for Webster Groves, MO
Our Reviews by City
Carl - Webster Groves, MO
John Murphy does a great job with inspecting and cleaning furnace.
Kathy - Webster Groves, MO
The guys showed up right on time and were very courteous. They recommended some minor improvements, made one of them and replaced my filter.
prompt and professional
Howard - Webster Groves, MO
PJ - Webster Groves, MO
Rapid response, friendly and efficient service.
Great service with know-how!
Eric - Webster Groves, MO
Jeff did a great job and had great familiarity with our furnace even though it is not a new unit! He did a great job inspecting, maintaining and cleaning the furnace. Thanks Jeff!
Mary - Webster Groves, MO
James - Webster Groves, MO
Bob - Webster Groves, MO
Glenn - Webster Groves, MO
Very thorough, competent job done.
Laura - Webster Groves, MO
On time, efficient, neat and tidy. set up next apt for AC....now it is already on my calendar.
Cleaned & checked condensing gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Checked drain. Blew out PVC drain. Checked filter. Clean and check humidifier, replace pad, checked water flow and drain.Suggestions: Need to add humidifier to maintenance plan at next renewal.
I found flame sensor current to low. Also, furnace is in need of cleaning. Replaced flame sensor. Tested operation. Temperature rise very high. I replaced customer’s air filter. Checked temperature rise. 56. I found return air duct is open where it is against the wall!! Apparently had a return air vent on the other side of the wall. wall Has been closed off! System is relying on only the return air duct that comes down from the attic. This only remaining ducting is too small for this equipment. Return duct pressure: -.35 inches water column.Suggestions: need to schedule first visit for maintenance plan purchased today. Customer would like a price to replace the furnace and to correct the duct issues.
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Humidifier not used. Blower: 1.8/5.7A . Inducer: 0.55/1.3A . Gas pressure: 1.9 inches water column. Temperature rise: 52 . Supply: 118. Return: 66.
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Replaced air filter. Clean and check humidifier, replace pad, checked water flow and drain. Blower: 2.6/3.7A . Inducer: 0.11/0.24A . Adj Gas pressure: 2.0/3.7inches water column. Temperature rise: 51/59 . Supply: 128/120 . Return: 69 .
No heat—replaced warranty gas valve
Fall maintenance today for the furnace!
Serviced furnace and installed uv light
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Back-flushed condenser coil with Water-Saber. Compressor: 8.6A. Condenser fan: 1.15A . Blower: 4.6A. ambient: 69 . liquid line: 76. suction line: 53 . metering device: TXV . Return air: 71 . supply air: 53 . Replaced air cleaner media.
I found disconnect pull-out switch missing!! I turned off the breaker at main panel, but still had voltage to one leg! Check voltage at circuit breaker in panel: no voltage, but still has voltage at one leg outside! I wired around missing pull out switch for testing. I found condenser fan motor bad! Shorted windings. Also, compressor run capacitor is bad. Open circuit. Also found system very low on Freon. Air-conditioner is 29 years old. Uses older type of Freon.Work suggested: recommend replacing air conditioner.
Returned after 6 o’clock in the evening to replace GFCI outlet. System had shut off again due to condensate pump float safety. Condensate pump was temporarily plugged into an outlet controlled by the light switch!! Installed new outlet. Tested condensate pump. Thermostat should be OK.