for Olivette, MO
Our Reviews by City
Henry - Olivette, MO
professional and experienced and friendly
Great Service, Knowledgeable Staff
David - Olivette, MO
Wonderful service from Sean
Shelley - Olivette, MO
Always request Sean! He’s the best, professional, knowledgeable, able to answer any/all questions
Great service, all performed under warranty. John was very professional and identified several issues, some of which were corrected and some need fur
Ron - Olivette, MO
Jerome - Olivette, MO
Everything was good
Patricia - Olivette, MO
Jeff did a great job, explaining things as he was checking the furnace, etc. I would like him back each time.
TM - Olivette, MO
Ted - Olivette, MO
As always, excellent service! Professional, and knowledgeable.
Trevor - Olivette, MO
Julie - Olivette, MO
Clicking noise coming from back furnace
Furnace maintenance for 2 systems!
No heat cleaned flame sensor and changed filter
Furnace maintenance for attic air handler!
Clean and check furnace
Clean and check
Maintenance on Rheem furnace and humidifier
Cleaned & checked 2 condensing gas furnaces. Inspected heat exchangers & flue venting. cleaned burners & flame sensors. Checked voltage & amp draw of motors. Test capacitors. Clean and check 2 humidifiers, replace pads, checked water flow and drains. Main system: blower: 5.4A, L. Check temperature rise. 62. manifold gas pressure: 3.9”. I adjusted blower speed and manifold pressure. Blower: 6.2A, ML. Inducer: 2.23A . Gas pressure: 3.5 inches water column. Temperature rise: 54 . Supply: 129 . Return: 75 . Rear system: 3.8”wc. Blower: 3.9 . Inducer: . Adjusted Gas pressure: 3.5 inches water column. Temperature rise: 54 . Supply: 130 . Return: 76. Blower capacitor: 5.0 µA.
Clean and check
Furnace maintenance for 2 systems! Installed Bluetube UV light!