Professional Heating, Air Conditioning & Plumbing Contractor near Olivette, MO
For more than 90 years, Classic Aire Care has been providing quality heating, air conditioning, indoor air quality, and plumbing services throughout Olivette. Our licensed, certified professionals have the experience to handle your most difficult heating, cooling, and plumbing problems, and when the worst happens, we offer 24-hour emergency service so that you can always get the help you need.
Are you having a problem with your HVAC or plumbing system? Contact Classic Aire Care today at (314) 300-6755 for quality service and repairs!
Heating & Air Conditioning Services
With NATE-certification and numerous industry credentials, our HVAC team at Classic Aire Care can handle all of your HVAC services, from new system installations and replacements to routine maintenance and repairs. Some of the services we offer include:
We install, repair, and maintain nearly any kind of air conditioning system, including central air systems, ductless mini-splits, heat pumps, packaged systems, and commercial AC units.
- Air conditioning repair service
- Air conditioning installation and replacement
- Air conditioning maintenance
- 24-hour emergency air conditioning service
- Heat pump repair, installation, and maintenance
- Air handler repair, installation, and maintenance
- Ductless AC system installation, repair, and maintenance
- Planned maintenance agreements for cooling systems
From routine air filter changes and burner cleaning to blower motor replacement and new thermostat installations, our team will keep your furnace running efficiently and safely. We can also keep your boiler running properly, from routine maintenance like cleaning the boilers to purging air from the system or replacing radiators.
- Furnace service
- Furnace repair
- Furnace replacement
- Furnace maintenance
- 24 hour emergency furnace repair
- Boiler services, including boiler repair, replacement, and maintenance
- Ductless heating system installation, repair, and maintenance
- Planned maintenance agreements for heating systems
Heating and air conditioning systems can break down at the worst times, which is why we offer 24-hour HVAC repair, for problems that happen on nights or weekends.
In our area, heat pumps can be the ideal solution for both heating and cooling a home. Using refrigerant and a compressor, the remove heat from your home in the summer, similar to an air conditioner, and in the winter, they can be reversed to pull heat from the outdoor air and bring it inside. At Classic Aire Care, we sell and install heat pumps and we also provide complete heat pump repair, maintenance, and emergency services.
Plumbing Service, Repair & Installation
Whether you have a plumbing leak, a clogged drain, or you need a fixture installed, you can count on our licensed plumbers at Classic Aire Care for reliable service and quality workmanship. Our services include:
- Pipe installation, repair, and replacement
- Drain and sewer cleaning
- Clog removal
- Leak detection and repair
- Video camera pipe inspections
- Water heater installation, repair, and maintenance
- Tankless water heater services
- Fixture or faucet installations
- Sump pump and garbage disposal services
- Commercial backflow and grease trap services
- 24/7 emergency service
Whether you live near Warson Park or Olive Boulevard, contact our team for quality plumbing services anywhere in the area!
Energy Efficiency & Air Quality Services
At Classic Aire Care, we also offer a number of services that can improve indoor air quality and save you money on your utility bills. These include:
- Home energy audits
- Insulation and air sealing services
- Duct cleaning services
- Programmable thermostat installations
- Air purifier, humidifier, and dehumidifier installations
- And more!
Contact us today to learn how we can help you improve your comfort and save money!
Call Us Today for HVAC & Plumbing Services
From HVAC installations to water heater replacements, our team at Classic Aire Care can handle all your heating, cooling, and plumbing needs.
For an appointment, contact us at (314) 300-6755 today!
for Olivette, MO
Our Reviews by City
Very knowledgible and helpful
Ivy - Olivette, MO
Loren - Olivette, MO
Roberta - Olivette, MO
Very good service with polite and knowledgeable serviceman
dmc - Olivette, MO
Te - Olivette, MO
Fast responsive service
Greg - Olivette, MO
Quickly diagnosed the problem and made the repair the same day at a reasonable price. Sean was very communicative throughout the process.
Mei - Olivette, MO
Annette - Olivette, MO
Very good service. I will have Joe again.
Great service always.
Elizabeth - Olivette, MO
Henry - Olivette, MO
professional and experienced and friendly
Fall maintenance today for the furnace! Replaced filter. Recommended humidifier install
Cleaned & checked 3 gas furnace. Inspected heat exchangers & flue venting. cleaned burners & flame sensors. Checked drains. Checked voltage & amp draw of motors. Test capacitors. Chemically Cleaned electronic air cleaners. Clean and check 3 humidifiers, replace pads,checked water flow and drains. First floor system: Found water flow through humidifier very weak. Solenoid valve clogged. Replaced solenoid valve.
Cleaned & checked 2 condensing gas furnaces. Inspected heat exchanger & flue venting. cleaned burners & flame sensors. Checked voltage & amp draw of motors. Test capacitors. Checked filters. Main system: Blower: 6.2A Inducer: 2.2A . Gas pressure: 3.5 inches water column. Rear system: Blower: 4.1A. Inducer: 2.2A . Gas pressure: 3.5 inches water column. Mid season checked of air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Main system: Compressor: 11.4A . Condenser fan: 1.2A . ambient: 79 . liquid line: 90 suction line: 54 . metering device: piston. Rear system: Compressor: 5.8A . Condenser fan: 0.62A. ambient:79 . liquid line: 90 . suction line: 44 . metering device: piston.
Serviced furnace and air conditioner
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. Replaced air cleaner MERV 16 media. Delivered. First floor system: Compressor: 8.2A. Condenser fan: 1.4A. ambient: 76 . liquid line: 79 . suction line: 51 . metering device: TXV . Return air: 71. supply air:51 . wet bulb: 59. Second floor system: Compressor: 7.9A . Condenser fan: 1.2A . ambient:76 . liquid line:78 . suction line: 38 . metering device: TXV . Return air: 71 . supply air: 50.5 . wet bulb: 59 . Found basement pressure negative (-.015inches water column) due to return-air ducting in basement and solid door to basement steps. This is causing downdraft of flu and fluegas spillage at water heater. Recommend adding make up air venting to first floor or block return air vent in basement.
Replaced blower motor and blower wheel
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. Checked filters. Replaced thermostat batteries. Main system: Compressor: 10.4A . Condenser fan: 1.2A . Blower:6.2A . ambient: 73 . liquid line: 82 . suction line: 55 . metering device: piston . Suction pressure: 113(38) . Return air:68 . supply air: 48 . wet bulb: 57 . Sh: T+8. Rear system: rem. 1/4#. Compressor: 5.2A. Condenser fan: 0.61A . Blower: adj. 4.4A . ambient: 73. suction line: 47 . metering device: piston . Suction pressure: 127(44) . head pressure: 272(90) . Return air:67.5 . supply air: 49.5 . wet bulb: 57.
Serviced 2air conditioners