HVAC & Plumbing Contractor in Clayton, MO
Residents of Clayton enjoy the best of both worlds—close proximity to the hustle and bustle of metropolitan St. Louis paired with the quiet charm of a safe, sleepy suburb. With a mix of single-family homes, condominiums, and apartment buildings, Clayton residents and building managers need a reliable HVAC and plumbing company they can call at a moment’s notice.
Whether you live by Shaw Park, near Fontbonne University, or anywhere else nearby in Clayton, you can rely on the experts of Classic Aire Care to handle all of your plumbing and HVAC needs. With our 24-hour emergency service, we’re only a phone call away.
Call us at (314) 300-6755 or contact us online today!
Why Choose Us as Your Clayton Heating, Air Conditioning & Plumbing Contractor?
As a customer of Classic Aire Care, you can expect:
- Happy, helpful, and timely service
- Respect for your property
- Top-notch technicians
- Superior product quality
- 100% satisfaction guarantee
Read more about our company values and see our mission statement here.
Clayton Heating & Air Conditioning Services
Classic Aire Care has more than 90 years of experience offering top-notch HVAC services. We can install, replace, and perform preventative maintenance for your heating and cooling systems. Our services include:
- Furnace services – We’ll change air filters, clean burners, replace motors, install thermostats, and more to keep your furnace in peak working order.
- AC services – We’ll keep the cool air running in your home or business by installing, repairing, or maintaining traditional AC systems, ductless mini-splits, heat pumps, commercial systems, and more.
- Planned maintenance – Get the longest life possible out of your HVAC equipment by having our experts inspect and clean your equipment and repair small problems before they get out of hand.
- 24-hour emergency service – Don’t swelter in a hot home all weekend waiting for Monday business hours to make a call. We’re standing by to get your HVAC equipment back online any time of the day or night.
Air Conditioning Services
- Air conditioner repair service
- Air conditioner installation and replacement
- Air conditioner maintenance
- 24-hour emergency air conditioning service
- Heat pump repair, installation, and maintenance
- Air handler repair, installation, and maintenance
- Ductless AC system installation, repair, and maintenance
- Planned maintenance agreements for cooling systems
- Furnace replacement
- Furnace repair
- Cleaning and repairing the air handler
- Boiler service, repair, or replacement
- Ductless heating services
- Heat pump repair, installation, or maintenance
- Planned maintenance agreements for heating systems
Do you need HVAC services in Clayton? Call Classic Aire Care today at (314) 300-6755 for an appointment!
Clayton Plumbing Services
When a pipe breaks or a drain is clogged, Classic Aire Care is on hand day or night to fix the leak. Our plumbing experts can:
- Gas, water, and sewer pipe repair and installation
- Inspection and maintenance of plumbing systems
- Sewer and drain repair and installation
- Drain and sewer cleaning
- Clog removal
- Installation of grease traps
- Video camera sewer inspection
- Detection and repair of leaks
- Installation and repair of water heaters
- Installation and repair of plumbing fixtures
- Emergency 24-hour plumbing service
- And more!
Call Classic Aire Care at (314) 300-6755 for all of your plumbing needs!
Clayton Air Quality & Home Energy Audits
Don’t spend another day in a home that wastes energy dollars and circulates dirty air that could negatively impact your health. At Classic Aire Care, we offer the following installations and other services:
- Air purifiers and air cleaners
- Ventilation systems
- Humidifiers and dehumidifiers
- Whole-home energy audits
- Installation of programmable thermostats
- Ductwork cleaning
- Air sealing and insulation
From installing a new air conditioner to unclogging a drain, Classic Aire Care does it all. When you need services in Clayton and the surrounding area, contact us online to schedule an appointment.
for Clayton, MO
Our Reviews by City
Exceptional Customer Focus, Quality of Service, and Competency
John - Clayton, MO
Classic Aire Care is fortunate to have Roger Henson represent their company in service visits. A most impressive man who competently installed our new lo-ambient kit. He also leaned-in willingly to lead the trouble-shooting of an additional situation and brought it to a simple and effective resolution. In addition, he was responsive to and able to clarify all of our questions. We are grateful for his help in establishing a new Planned Maintenance Agreement as well. Roger Henson is unmatched in our service visit experiences....standing out in any evaluation criteria utilized. Please send Roger for all our PMA service visits!
Carol - Clayton, MO
Everything done in an excellent and straightforward manner despite all the tight places in our house.
Judith - Clayton, MO
I was very pleased with Roger's handling of our two A/C units, including his having to go up into our attic through a hole in a closet ceiling. He was very polite and knowledgeable and went well.
Petra - Clayton, MO
Azar - Clayton, MO
Classic Aire Fan
Nancy - Clayton, MO
Classic Aire has an excellent customer service system. They call to schedule check-ups if you have a contract. They contact you by email as well. They call the day of the visit to let you know the technician is on the way. It is always within the window of time cited on the appointment.Technicians are neat, efficient, friendly, can answer any questions, and finish any billing matters before they leave.
Valerie - Clayton, MO
The service by Classic Aire Care is outstanding. The gentleman were prompt, thorough, respectful of our home and pets, and had excellent communication throughout the process.
Deborah - Clayton, MO
Efficient and responsive
Best HVAC Service man ever
Virginia - Clayton, MO
John is calm, courteous and efficient. He does a great job and always cleans up. We count on him.
Mary - Clayton, MO
Very competent, prompt & courteous: John Murpht
Robert - Clayton, MO
quality work, on time, great service since 1983!
very helpful, glad to set up for regular service
David - Clayton, MO
Everything went smoothly and Sean was very knowledgeable. I appreciated his suggestions and insights.
Thank you for the great service
Sally - Clayton, MO
Minjoo Sim - Clayton, MO
Team of two did a fall AC -> Heat inspection. Did a terrific job, and were great. Turned the lights off after they were done with the various units.
Maireen - Clayton, MO
I have been happy with the services from Classic Air since I bought my condo. Sean provided excellent maintenance service on his annual inspection and discussed everything with me. I was also pleased with the excellent guidance last year from Mike when I had to purchase new heating and air-conditioning units.
Stephen - Clayton, MO
James - Clayton, MO
responsive, timely, courteous, professional.
Used Classic Aire Care for years
Nancy - Clayton, MO
Every serviceperson who comes is knowledgeable, thorough, quiet, patient with sticky issues, courteous, and on time. The office staff call with reminders of inspections due and appointments booked. Very efficient tracking on our account--heating and AC.
Kim - Clayton, MO
Very knowledgeable and Informative
Stephen - Clayton, MO
Complaint: temperature not coming down after service done. Compressor: 12.8A . Condenser fan: 1.48A . Blower: 6.8A . ambient: 90 . liquid line: 103. suction line: 58 . metering device: TXV . Suction pressure: 73(43) . Return air: 76 . supply air: 57 . wet bulb: 63 . Freon pressures good. Temperature drop good. Motors OK. System appears to be calling at full capacity.
Installed low ambient kit....
Replaced capacitor and serviced ac system
Customer complaint: AC not staying on. second floor thermostat keeps showing a delay countdown. I checked all connections. I checked voltage: 31.5. I adjusted voltage to 27.5. I tested wet switch operation. I checked zone system operation. I found first floor damper not closing! Also, second floor Nest thermostat Having trouble with power stealing mode. I replaced four conductor thermostat wire with five conductor to add “common” wire to thermostat. Tested operation. Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Checked temperature drop. 18.5. Compressor: 21.5. Condenser fan: 1.2A . ambient: 87 . liquid line: 103, dirty . suction line: 49. metering device: TXV . Suction pressure: 70(41) . head pressure:256(117) dirty . Cleaned condenser coil.
Complaint: no cooling. System cooling when I arrived: cooling tower was down the other day. Complaint number two: customer complained of a foul odor. odor is most likely from bacterial growth on water coil. Recommend ultraviolet lamp installation. I found system does not cycle the fan on call for heating and cooling. Needs a fan center installed to enable this. Also temperature drop is only 13.5 degrees. Needs to be 3 degrees colder. Need blower/shieve adjustment. Work suggested: install fan center control: $392. I just belt drive blower: $95. Install apco: $790.
Found dual run capacitor bad. Open circuit. Replaced capacitor and tested amp draw of motor. Found condenser coil very dirty. Work suggested: maintenance plan for three systems: $447.
Replaced dual capacitor for second floor system. Tested cooling operation on Goodman air conditioner.
Customer wants old steam piping removed from garage. All radiators from this loop have been removed. Steam unit heater to be removed. I located area to cut, thread, and cap Pipes in the basement. See pictures. Customer marked Area to cut with blue masking tape.
Third floor system flat out of Freon. Showing about three PSI. I charged up for temporary cooling. 2.5 pounds of R-22. Water cooled system uses city water. Unit is scheduled for replacement.
Spring maintenance on both ac systems!
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level: low. Condenser coil extremely dirty. LL: 128. SL: 71. WB : 65. Cleaned condenser coil. Replaced air filter. Topped off with R22 Freon. Expect Freon to leak back out. Compressor: 12.2 A. Fan motor: 1.2 A. Work suggested: Freon leak search: $189. Freon leak repair: $? Expect air-conditioner to have trouble keeping home cool enough to do missing sections of the ceiling.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Compressor: 9.2A .Condenser fan:0.7A . ambient: 81 .liquid line: 86 .suction line: 49.metering device: TXV .
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. Second floor system can only operate in first stage due to faulty CFM board in air handler. Second floor system: Compressor: 5.4A .Condenser fan: 1.2A .ambient: 74 .liquid line: 75 .suction line: 35 .metering device: TXV. Return air vent: 68.5 .supply air: 44.5 .wet bulb: 57 . First floor system: customer complaint: thermostat was set to 73, room temperature 78, nothing was running. System started working OK later. Found no problems to cause this at this time. Freon level low. I topped off Freon (R22). Expect system has a Freon leak. System can only operate in stage one operation. Has bad expansion valve and undersized blower.
I found zone damper for zone one, front side of house not closing all the way. Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Work suggested: replace damper under parts warranty: $152. John O. to order damper. Vacuum surface of air cleaner monthly.
Replaced contactor and repaired burnt wires on ac
Serviced air conditioner and added Freon
Spring maintenance for all home AC systems! Good to go
Serviced air conditioner
No cooling added Freon,customer to get estimate on new system
I found addition system evaporator(1780) iced up. Checked first floor thermostat in reading room: cooling set to 67. Checked upper level thermostat: cooling set to 67. I de-iced evaporate or coil. I found system low on Freon!! Freon level was not retested after coil cleaning on Wednesday. Condenser coil was extremely dirty. I charged system to full capacity. Tighten service valve caps. Expect Freon may leak back out. Suction: 59. SL:35. Ambient: 76. Work suggested: system uses older Freon that is being phased out. Recommend replacing rather than repairing any Freon leaks. We will check level next year.