Residents of Clayton enjoy the best of both worlds—close proximity to the hustle and bustle of metropolitan St. Louis paired with the quiet charm of a safe, sleepy suburb. With a mix of single-family homes, condominiums and apartment buildings, Clayton residents and building managers need a reliable HVAC and plumbing company they can call at a moment’s notice.
Whether you live by Shaw Park or near Fontbonne University, you can rely on the experts of Classic Aire Care to handle all of your plumbing and HVAC needs. With our 24-hour emergency service, we’re only a phone call away. Call us at 314-300-6755 or contact us online today!
Clayton Heating & Air Conditioning Services
Classic Aire Care has more than 90 years of experience in offering top-notch HVAC services. We can install, replace, and perform preventative maintenance for your heating and cooling systems, and more. Additional services include:
- Furnace services – We’ll change air filters, clean burners, replace motors, install thermostats and more to keep your furnace in peak working order.
- AC services – We’ll keep the cool air running in your home or business by installing, repairing or maintaining traditional AC systems, ductless mini-splits, heat pumps, commercial systems, and more.
- Planned Maintenance – Get the longest life possible out of your HVAC equipment by having our experts inspect and clean your equipment and repair small problems before they get out of hand.
- 24-Hour Emergency Service – Don’t swelter in a hot home all weekend waiting for Monday business hours to make a call. We’re standing by to get your HVAC equipment back online any time of the day or night.
Do you need HVAC services in Clayton? Call Classic Aire Care today at 314-300-6714 for an appointment!
Clayton Plumbing Services
When a pipe breaks or a drain is clogged, Classic Aire Care is on hand day or night to fix the leak. Our plumbing experts can:
- Install and repair water, gas, and sewer pipes
- Inspect and maintain plumbing systems
- Install, clean, and repair drains and sewers
- Remove drain clogs
- Perform video camera sewer inspections
- Install grease traps
- Detect leaks
- Install water heaters
- Install and repair water fixtures
Call Classic Aire Care at 314-300-6714 for all of your plumbing needs!
Clayton Air Quality & Home Energy Audits
Don’t spend another day in a home that wastes energy dollars and circulates dirty air that could negatively impact your health. At Class Aire Care, we offer the following installations and other services:
- Air purifiers and air cleaners
- Ventilation systems
- Humidifiers and dehumidifiers
- Whole-home energy audits
- Installation of programmable thermostats
- Ductwork cleaning
- Air sealing and insulation
From installing a new air conditioner to unclogging a drain, Classic Aire Care does it all. When you need services in Clayton and the surrounding area, contact us online to schedule an appointment.
for Clayton, MO
Our Reviews by City
Great customer service!
Valerie - Clayton, MO
John was great! He was on time. He was courteous and professional. He explained things thoroughly.
On time good service
Linda - Clayton, MO
Service was excellent once technician was here. He arrived about 1.5 hours late!
Rudy - Clayton, MO
On location service was very good. However, the technician was supposed to be here between 8 and 9am; he arrived at 10am. I took time from work to be here and available during the service. I had to return to work at 11am. Fortunately, there was nothing wrong with the units and the inspection was accomplished in one hour. It is most important to me that the time of service is respected.
Good work from Classic Aire Co.
John - Clayton, MO
We had a good service call today. Nothing out of the ordinary!!
Really nice guy~
Paulette - Clayton, MO
Corey explained everything he was doing, which I really like! I was thinking of switching companies but I am now sticking with Classic Aire!
Marcel - Clayton, MO
Great service, technician very friendly and knowledgable
Mark - Clayton, MO
timely efficient service.
Robert - Clayton, MO
Everything was great. Showed up on time and was very professional.
Reliable service provider.
Sonia - Clayton, MO
I will miss John's excellent service and customer oriented demeanor!
great service asm usual. Corey is the best technician we have ever had. Love Corey
Samuel - Clayton, MO
Mark - Clayton, MO
Marcia - Clayton, MO
Is very nice to like and trust the person who comes to your house to service your a/c
Very pleased with service
Anna - Clayton, MO
Christina - Clayton, MO
We have been using Classic Aire Care for many years and find them reliable and helpful. I think the service is somewhat overpriced. I also do not like being given a window of time of several hours (I think it should be 2 at most). Also, the service is often not very efficient. Today we had to wait 20 minutes to have the filters delivered from the office.
Peter - Clayton, MO
Excellent Experience with Corey and Classic Aire Care!
Natalie - Clayton, MO
My technician, Corey, arrived on time and could not have provided more excellent service. Corey is incredibly knowledgeable about HVAC systems and goes above and beyond to make sure that every detail is attended to. I will only ask for Corey for all future visits. Based upon my experience, I am recommending this company to my family and friends. Thanks, Corey and Classic Aire Care!
Chad - Clayton, MO
Effective & Efficient
Doug - Clayton, MO
The tech showed up when scheduled, performed all the diagnostic procedures without delay and was on his way.
Robert - Clayton, MO
Annual AC Service
Joan - Clayton, MO
cleaned & checked A/C & performed Ameren post data efficiency analysis. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Checked filter. Compressor: 11.0A.Condenser fan: 1.3aa.ambient: 85.liquid line: 100.suction line: 50 .metering device: Piston . Suction pressure:73(43). Return air:75.8 .supply air: 54.8.wet bulb: 65 .
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. Replaced air filters. First floor system: Compressor: 8.1aa.Condenser fan: .6A . Blower: L .ambient: 90.liquid line: 104, dirty .suction line: 47 .metering device: EEV. Return air: 76 .supply air: 57. Second floor system: Compressor: 12.1A .Condenser fan: .7A . ambient: 90 .liquid line: 92 .suction line: 64 .metering device: TXV . Suction pressure: 123(43) Return air: 79.
Serviced air conditioning unit and replaced capacitor
Found compressor motor shorted to ground! 20 year old R-22 unit.
Installed trap on condensate line
Found bad condenser fan motor and blade
Added 3 pounds of freon r22 to ac
No cool found failed capicator
Clean and check w systems
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coil. Checked filters. First floor system: Compressor: 8.9A .Condenser fan: .9A . Blower: 3.8A .ambient: 77.liquid line: 79 .suction line: 43.metering device: is TXV . wet bulb: 59. Second floor system: Compressor: 8.5A.Condenser fan: .9A . Blower: 3.7A .ambient: 76 .liquid line: 81 .suction line: 46.metering device: TXV .wet bulb: 59.
Clean & check on a/c system
Clean and check water cooled ac
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coil. Main system: found system 3 pounds low on Freon! Has two year old condensing unit (R22). 31 year old air handler in attic is now leaking Freon. I charged with 2 pounds of R22 Freon for temporary cooling. Compressor: 9.2A .Condenser fan: .7A .ambient: 68.liquid line:80 .suction line: 52 .metering device: TXV . Suction pressure:63(36) .head pressure: 160(87) .wet bulb:60. Family room system: Compressor: 7.9A.Condenser fan: 1.1A. Blower: 1.7A.ambient: 69.liquid line:70 .suction line: 35 .metering device: piston.
Ameren i.e. Tune up and replaced failed capicator
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Cleaned condenser coil. Replaced air filters. First floor system: Found low on Freon. Topped off with R-22 per superheat chart. Compressor: 23.5A .Condenser fan: 1.6A .ambient: 80.liquid line:97 .suction line: 42 .metering device: piston . Suction pressure: 72(42) .wet bulb: 59 . Second floor system: Compressor: 22.5A.Condenser fan: 1.55A .ambient: 80 .liquid line: 90 .suction line: 34 .metering device: piston . Suction pressure: 54 .
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. First floor system: Compressor: 6.4A.Condenser fan: .65A .ambient: 81 .liquid line: 87. suction line: 56.metering device: txv. Return air: 74 .supply air: 55 . Second/third floor system: Compressor:8.5A .Condenser fan: .85A. Blower: 2.1A .ambient: 80 .liquid line: 85.suction line: 59.metering device: TXV .supply air: 52 .
Clean & check on a/c system