Top HVAC & Plumbing Services in Clayton, MO
Residents of Clayton enjoy the best of both worlds—close proximity to the hustle and bustle of metropolitan St. Louis paired with the quiet charm of a safe, sleepy suburb. With a mix of single-family homes, condominiums and apartment buildings, Clayton residents and building managers need a reliable HVAC and plumbing company they can call at a moment’s notice.
Whether you live by Shaw Park or near Fontbonne University, you can rely on the experts of Classic Aire Care to handle all of your plumbing and HVAC needs. With our 24-hour emergency service, we’re only a phone call away. Call us at 314-300-6755 or contact us online today!
Clayton Heating & Air Conditioning Services
Classic Aire Care has more than 90 years of experience in offering top-notch HVAC services. We can install, replace, and perform preventative maintenance for your heating and cooling systems, and more. Additional services include:
- Furnace services – We’ll change air filters, clean burners, replace motors, install thermostats and more to keep your furnace in peak working order.
- AC services – We’ll keep the cool air running in your home or business by installing, repairing or maintaining traditional AC systems, ductless mini-splits, heat pumps, commercial systems, and more.
- Planned Maintenance – Get the longest life possible out of your HVAC equipment by having our experts inspect and clean your equipment and repair small problems before they get out of hand.
- 24-Hour Emergency Service – Don’t swelter in a hot home all weekend waiting for Monday business hours to make a call. We’re standing by to get your HVAC equipment back online any time of the day or night.
Do you need HVAC services in Clayton? Call Classic Aire Care today at 314-300-6714 for an appointment!
Clayton Plumbing Services
When a pipe breaks or a drain is clogged, Classic Aire Care is on hand day or night to fix the leak. Our plumbing experts can:
- Install and repair water, gas, and sewer pipes
- Inspect and maintain plumbing systems
- Install, clean, and repair drains and sewers
- Remove drain clogs
- Perform video camera sewer inspections
- Install grease traps
- Detect leaks
- Install water heaters
- Install and repair water fixtures
Call Classic Aire Care at 314-300-6714 for all of your plumbing needs!
Clayton Air Quality & Home Energy Audits
Don’t spend another day in a home that wastes energy dollars and circulates dirty air that could negatively impact your health. At Class Aire Care, we offer the following installations and other services:
- Air purifiers and air cleaners
- Ventilation systems
- Humidifiers and dehumidifiers
- Whole-home energy audits
- Installation of programmable thermostats
- Ductwork cleaning
- Air sealing and insulation
From installing a new air conditioner to unclogging a drain, Classic Aire Care does it all. When you need services in Clayton and the surrounding area, contact us online to schedule an appointment.
for Clayton, MO
Our Reviews by City
Valerie - Clayton, MO
The service by Classic Aire Care is outstanding. The gentleman were prompt, thorough, respectful of our home and pets, and had excellent communication throughout the process.
Deborah - Clayton, MO
Efficient and responsive
Best HVAC Service man ever
Virginia - Clayton, MO
John is calm, courteous and efficient. He does a great job and always cleans up. We count on him.
Mary - Clayton, MO
Very competent, prompt & courteous: John Murpht
Robert - Clayton, MO
quality work, on time, great service since 1983!
very helpful, glad to set up for regular service
David - Clayton, MO
Everything went smoothly and Sean was very knowledgeable. I appreciated his suggestions and insights.
Thank you for the great service
Sally - Clayton, MO
Minjoo Sim - Clayton, MO
Team of two did a fall AC -> Heat inspection. Did a terrific job, and were great. Turned the lights off after they were done with the various units.
Maireen - Clayton, MO
I have been happy with the services from Classic Air since I bought my condo. Sean provided excellent maintenance service on his annual inspection and discussed everything with me. I was also pleased with the excellent guidance last year from Mike when I had to purchase new heating and air-conditioning units.
Stephen - Clayton, MO
James - Clayton, MO
responsive, timely, courteous, professional.
Used Classic Aire Care for years
Nancy - Clayton, MO
Every serviceperson who comes is knowledgeable, thorough, quiet, patient with sticky issues, courteous, and on time. The office staff call with reminders of inspections due and appointments booked. Very efficient tracking on our account--heating and AC.
Kim - Clayton, MO
Very knowledgeable and Informative
Stephen - Clayton, MO
Great customer service!
Valerie - Clayton, MO
John was great! He was on time. He was courteous and professional. He explained things thoroughly.
On time good service
Linda - Clayton, MO
Service was excellent once technician was here. He arrived about 1.5 hours late!
Rudy - Clayton, MO
On location service was very good. However, the technician was supposed to be here between 8 and 9am; he arrived at 10am. I took time from work to be here and available during the service. I had to return to work at 11am. Fortunately, there was nothing wrong with the units and the inspection was accomplished in one hour. It is most important to me that the time of service is respected.
Good work from Classic Aire Co.
John - Clayton, MO
We had a good service call today. Nothing out of the ordinary!!
Really nice guy~
Paulette - Clayton, MO
Corey explained everything he was doing, which I really like! I was thinking of switching companies but I am now sticking with Classic Aire!
Marcel - Clayton, MO
Checked out furnace found blocked filter and found cracked heat exchangers
Serviced boiler replaced thermocouple
Clean and check, replacedfilter and humidifer service
Checked out heat pump
Serviced hot water boiler and replaced thermocouple
Replaced shorted out contractor and fuse on heat pump
Replaced condensate trap assembly
Customer suspects kitchen loop for radiant floor heat is frozen. We were not able to force water through the loop. It may have stuck valve also. May need new manifold (HeatLink). Boiler pressure is OK at this time. But expansion tank may need to be drained.
Cleaned & checked 2 condensing gas furnaces. Inspected heat exchangers & flue venting. cleaned burners & flame sensors. Checked voltage & amp draw of motors. Test capacitors. Checked drains. Replaced air filters. Second floor system: Blower: 5.6A . Inducer: 1.7A . Gas pressure: 3.5 inches water column. Temperature rise: 68 . Supply: 148 . Return: 80 . First floor system: Blower: 5.5A . Inducer: 2.1A . Gas pressure: 3.4A inches water column. Temperature rise: 60 . Supply: 130. Return:70. Clean and check humidifier, replace pad, checked water flow and drain. Found water flow blocked, solenoid valve sticking on. Replace solenoid valve.
Clean and. Heck plus humidifer
Clean and check Amana system
Return December 27, 2017: installed proper rollout safety device. Tested boiler operation. Manifold gas pressure: 3.5. Draft: .04”.
Maintenance on three American Standard furnaces and accessories.
I found rollout safety fuse link tripped. I installed temporary safety switch in place fuse link for temporary heat. I checked heat exchanger: clean. I checked draft: good (.035 inches water column). Check gas pressure. OK. Boiler room does not have proper combustion air venting. Customer keeps door open all the time. Fireplaces were running and may have affected draft.
Serviced furnace and humidifier and replaced filter
Maintenance on Lennox furnace and accessories.
Electric air handler maintenance! Replaced weak capacitor and humidifier pad
Serviced 2- furnaces and humidifier
Fall clean and check on Lennox furnace