HVAC & Plumbing Contractor in Clayton, MO
Residents of Clayton enjoy the best of both worlds—close proximity to the hustle and bustle of metropolitan St. Louis paired with the quiet charm of a safe, sleepy suburb. With a mix of single-family homes, condominiums, and apartment buildings, Clayton residents and building managers need a reliable HVAC and plumbing company they can call at a moment’s notice.
Whether you live by Shaw Park, near Fontbonne University, or anywhere else nearby in Clayton, you can rely on the experts of Classic Aire Care to handle all of your plumbing and HVAC needs. With our 24-hour emergency service, we’re only a phone call away.
Call us at (314) 300-6755 or contact us online today!
Why Choose Us as Your Clayton Heating, Air Conditioning & Plumbing Contractor?
As a customer of Classic Aire Care, you can expect:
- Happy, helpful, and timely service
- Respect for your property
- Top-notch technicians
- Superior product quality
- 100% satisfaction guarantee
Read more about our company values and see our mission statement here.
Clayton Heating & Air Conditioning Services
Classic Aire Care has more than 90 years of experience offering top-notch HVAC services. We can install, replace, and perform preventative maintenance for your heating and cooling systems. Our services include:
- Furnace services – We’ll change air filters, clean burners, replace motors, install thermostats, and more to keep your furnace in peak working order.
- AC services – We’ll keep the cool air running in your home or business by installing, repairing, or maintaining traditional AC systems, ductless mini-splits, heat pumps, commercial systems, and more.
- Planned maintenance – Get the longest life possible out of your HVAC equipment by having our experts inspect and clean your equipment and repair small problems before they get out of hand.
- 24-hour emergency service – Don’t swelter in a hot home all weekend waiting for Monday business hours to make a call. We’re standing by to get your HVAC equipment back online any time of the day or night.
Air Conditioning Services
- Air conditioner repair service
- Air conditioner installation and replacement
- Air conditioner maintenance
- 24-hour emergency air conditioning service
- Heat pump repair, installation, and maintenance
- Air handler repair, installation, and maintenance
- Ductless AC system installation, repair, and maintenance
- Planned maintenance agreements for cooling systems
- Furnace replacement
- Furnace repair
- Cleaning and repairing the air handler
- Boiler service, repair, or replacement
- Ductless heating services
- Heat pump repair, installation, or maintenance
- Planned maintenance agreements for heating systems
Do you need HVAC services in Clayton? Call Classic Aire Care today at (314) 300-6755 for an appointment!
Clayton Plumbing Services
When a pipe breaks or a drain is clogged, Classic Aire Care is on hand day or night to fix the leak. Our plumbing experts can:
- Gas, water, and sewer pipe repair and installation
- Inspection and maintenance of plumbing systems
- Sewer and drain repair and installation
- Drain and sewer cleaning
- Clog removal
- Installation of grease traps
- Video camera sewer inspection
- Detection and repair of leaks
- Installation and repair of water heaters
- Installation and repair of plumbing fixtures
- Emergency 24-hour plumbing service
- And more!
Call Classic Aire Care at (314) 300-6755 for all of your plumbing needs!
Clayton Air Quality & Home Energy Audits
Don’t spend another day in a home that wastes energy dollars and circulates dirty air that could negatively impact your health. At Classic Aire Care, we offer the following installations and other services:
- Air purifiers and air cleaners
- Ventilation systems
- Humidifiers and dehumidifiers
- Whole-home energy audits
- Installation of programmable thermostats
- Ductwork cleaning
- Air sealing and insulation
From installing a new air conditioner to unclogging a drain, Classic Aire Care does it all. When you need services in Clayton and the surrounding area, contact us online to schedule an appointment.
for Clayton, MO
Our Reviews by City
Sam - Clayton, MO
Jeff Kelly is terrific. Professional and efficient and thorough. Thanks!
Marilyn - Clayton, MO
John always finds the problem and fixed difficult situations.
Exceptional Customer Focus, Quality of Service, and Competency
John - Clayton, MO
Classic Aire Care is fortunate to have Roger Henson represent their company in service visits. A most impressive man who competently installed our new lo-ambient kit. He also leaned-in willingly to lead the trouble-shooting of an additional situation and brought it to a simple and effective resolution. In addition, he was responsive to and able to clarify all of our questions. We are grateful for his help in establishing a new Planned Maintenance Agreement as well. Roger Henson is unmatched in our service visit experiences....standing out in any evaluation criteria utilized. Please send Roger for all our PMA service visits!
Carol - Clayton, MO
Everything done in an excellent and straightforward manner despite all the tight places in our house.
Judith - Clayton, MO
I was very pleased with Roger's handling of our two A/C units, including his having to go up into our attic through a hole in a closet ceiling. He was very polite and knowledgeable and went well.
Petra - Clayton, MO
Azar - Clayton, MO
Classic Aire Fan
Nancy - Clayton, MO
Classic Aire has an excellent customer service system. They call to schedule check-ups if you have a contract. They contact you by email as well. They call the day of the visit to let you know the technician is on the way. It is always within the window of time cited on the appointment.Technicians are neat, efficient, friendly, can answer any questions, and finish any billing matters before they leave.
Valerie - Clayton, MO
The service by Classic Aire Care is outstanding. The gentleman were prompt, thorough, respectful of our home and pets, and had excellent communication throughout the process.
Deborah - Clayton, MO
Efficient and responsive
Best HVAC Service man ever
Virginia - Clayton, MO
John is calm, courteous and efficient. He does a great job and always cleans up. We count on him.
Mary - Clayton, MO
Very competent, prompt & courteous: John Murpht
Robert - Clayton, MO
quality work, on time, great service since 1983!
very helpful, glad to set up for regular service
David - Clayton, MO
Everything went smoothly and Sean was very knowledgeable. I appreciated his suggestions and insights.
Thank you for the great service
Sally - Clayton, MO
Minjoo Sim - Clayton, MO
Team of two did a fall AC -> Heat inspection. Did a terrific job, and were great. Turned the lights off after they were done with the various units.
Maireen - Clayton, MO
I have been happy with the services from Classic Air since I bought my condo. Sean provided excellent maintenance service on his annual inspection and discussed everything with me. I was also pleased with the excellent guidance last year from Mike when I had to purchase new heating and air-conditioning units.
Stephen - Clayton, MO
James - Clayton, MO
responsive, timely, courteous, professional.
Used Classic Aire Care for years
Nancy - Clayton, MO
Every serviceperson who comes is knowledgeable, thorough, quiet, patient with sticky issues, courteous, and on time. The office staff call with reminders of inspections due and appointments booked. Very efficient tracking on our account--heating and AC.
Customer stated that yesterday system would run for 30 seconds and shut off for five minutes, then repeat. I turned on the system and tested operation. System stayed on and cold without shutting off. I found superheat a little high. Condenser coil Supply water: 68. Return water: 75. Suction: 59 (33) superheating: 20. Expansion device: Cap tube. I topped off freon level. Total system amps: 10.0A. Superheat: six.
Serviced air conditioner and installed air purifier
AC maintenance for both systems today!
Heating maintenance on both home furnaces! Both look good
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coils. Second floor system: Replaced air filter. Connected float safety to Y1 wire instead of R wire to thermostat. Compressor: 8.6A . Condenser fan: 1.24A . Blower: 4.5A . ambient: 80 . liquid line: 83 . suction line: 57 . metering device: TXV . Return air: 74 . supply air: 52 . First floor system: Replaced air filter. Compressor: 8.5A. Condenser fan: 1.22A . Blower: 3.2A . ambient: 80. liquid line: 82. suction line: 56. metering device: TXV . Return air:71 . supply air: 50.5 . wet bulb: 59 . Suggestions: cover filter slot opening in attic. See attachment email. Follow up: customer is getting squirrels in the attic through opening where electric, gas, and refrigerant lines access the attic. Needs opening closed up.
Master bedroom unit: 6939: Contactor not energize. no 24V at condensing unit. Has 24 V at air handler. Traced thermostat wire through attic space: has 24v. Open wire is inside the flashing that runs up the outside wall to the second floor attic space. Could not pull wire. I found one of the two conductors still good. Connected good wire to 24 V “hot“ and connected contactor coil to ground. Working OK using one conductor and using ground for other 24V conductor.
LEDs: orange & green. I blew out condensate trap with dry nitrogen.
Cleaned and checked air conditioner. Checked drain. Blew out trap. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Tested thermostat batteries. Compressor: 8.0A . Condenser fan: 1.02A . ambient: 71, rain & lightening . liquid line: 88 . suction line: 53 . Return air grill: 58 . supply air vent: 49 . wet bulb: 58 . Work suggested: Replace thermostat batteries.
Installed new water safety float switch
Replaced warranty compressor!
Cleaned and checked 2 air conditioners. Checked drains. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon levels. Cleaned condenser coil. Second floor system: Replaced air filter. Compressor: 7.1A. Condenser fan: 0.8A . Blower: 4.3A . ambient: 73 . liquid line: 79 . suction line: 57 . metering device: TXV. Return air:76.5 . supply air: 56. First floor system: Compressor: 12.1A . Condenser fan: 1.0A . Blower: ml . ambient: 73 . liquid line: 94. suction line: 66. metering device: piston . Suction pressure: 69(40). Return air: 75,50% . supply air: 55 . wet bulb: 63 .
Replaced the main system coil as well as the addition system coil!
Complaint: temperature not coming down after service done. Compressor: 12.8A . Condenser fan: 1.48A . Blower: 6.8A . ambient: 90 . liquid line: 103. suction line: 58 . metering device: TXV . Suction pressure: 73(43) . Return air: 76 . supply air: 57 . wet bulb: 63 . Freon pressures good. Temperature drop good. Motors OK. System appears to be calling at full capacity.
Installed low ambient kit....
Replaced capacitor and serviced ac system
Customer complaint: AC not staying on. second floor thermostat keeps showing a delay countdown. I checked all connections. I checked voltage: 31.5. I adjusted voltage to 27.5. I tested wet switch operation. I checked zone system operation. I found first floor damper not closing! Also, second floor Nest thermostat Having trouble with power stealing mode. I replaced four conductor thermostat wire with five conductor to add “common” wire to thermostat. Tested operation. Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Checked temperature drop. 18.5. Compressor: 21.5. Condenser fan: 1.2A . ambient: 87 . liquid line: 103, dirty . suction line: 49. metering device: TXV . Suction pressure: 70(41) . head pressure:256(117) dirty . Cleaned condenser coil.
Complaint: no cooling. System cooling when I arrived: cooling tower was down the other day. Complaint number two: customer complained of a foul odor. odor is most likely from bacterial growth on water coil. Recommend ultraviolet lamp installation. I found system does not cycle the fan on call for heating and cooling. Needs a fan center installed to enable this. Also temperature drop is only 13.5 degrees. Needs to be 3 degrees colder. Need blower/shieve adjustment. Work suggested: install fan center control: $392. I just belt drive blower: $95. Install apco: $790.
Found dual run capacitor bad. Open circuit. Replaced capacitor and tested amp draw of motor. Found condenser coil very dirty. Work suggested: maintenance plan for three systems: $447.
Replaced dual capacitor for second floor system. Tested cooling operation on Goodman air conditioner.
Customer wants old steam piping removed from garage. All radiators from this loop have been removed. Steam unit heater to be removed. I located area to cut, thread, and cap Pipes in the basement. See pictures. Customer marked Area to cut with blue masking tape.