As “The Neighborhood to the World,” University City is a compact St. Louis suburb with a big cultural impact. A mix of housing styles and eclectic businesses, property owners in University City trust the professionals of Classic Aire Care for their plumbing and HVAC needs.
Since 1926, Classic Aire Care has provided outstanding HVAC and plumbing services to the residents of University City and Greater St. Louis. With a dedication to customer service, knowledgeable technicians, and the highest quality equipment on the market, you know you’re getting the best, most trusted contractor in the industry.
Whether you live by Ruth Clark Golf Course or across from Washington University, call Classic Aire Care at 314-300-6755 today for all of your HVAC and plumbing needs!
University City Heating & Air Conditioning Services
When your AC or furnace is on the fritz, the expert team at Classic Aire Care can fix it in a snap. With our 24-hour emergency service, we’re standing by to get your HVAC system back online no matter the time of day. In addition to installation, repair, and preventative maintenance services, we also offer:
AC Services: Our technicians are trained to service traditional units, ductless mini-splits, heat pumps, or commercial HVAC equipment.
Heating Services: Our NATE-certified technicians install thermostats, clean burners, replace blower motors, change air filters, and more.
University City Plumbing Services
When a clogged kitchen drain puts your kitchen out of commission, call the expert team at Classic Aire Care to get the water flowing again. Our plumbers specialize in:
- Gas, water, and sewer pipe repair and installation
- Inspection and maintenance of plumbing systems
- Sewer and drain repair and installation
- Drain and sewer cleaning
- Clog removal
- Installation of grease traps
- Video camera sewer inspection
- Detection and repair of leaks
- Installation and repair of water heaters
- Installation and repair of plumbing fixtures
- Emergency 24-hour plumbing service
No matter your plumbing needs in University City, our team will make your call a top priority. Call us today at 314-300-6755!
University City Home Energy Audits & Air Quality Services
A drafty, poorly insulated home can cost you a fortune in energy bills. Pair that with poor air quality, and you’ll be uncomfortable in your home. Luckily, Classic Aire Care has the tools to fix it. We offer a range of services to determine air quality and energy efficiency, including:
- Installation of air purifiers and air cleaners
- Installation of ventilation systems
- Installation of humidifiers and dehumidifiers
- Comprehensive, whole home energy audits
- Installation of ductwork and duct cleaning
- Air sealing
If you’re interested in finding out where the air leaks are in your home, or if you’re concerned your air quality is subpar, call Classic Aire Care today at 314-300-6755! From a broken furnace to a clogged drain, Classic Aire Care provides the HVAC and plumbing services you need.
for University City, MO
Our Reviews by City
Great Service, Friendly People
Timothyg - University City, MO
Classic Are Care always does a very thorough job.
Hans - University City, MO
Very prompt and great service
David - University City, MO
WENT RIGHT TO WORK
Yvonne - University City, MO
Roger came in and asked about the problem. Then went right to work solving my problem. He guessed the problem and explained and /or answered any of my questions about my boiler.
Donald - University City, MO
Henry - University City, MO
Jeff was thorough, diagnose the problem, and offered options.
Welcome service visit
Craig - University City, MO
Nice guy with a great personality and fun to talk to and gave me good information about my system and some questions I had
Anne - University City, MO
Jack - University City, MO
Prompt, efficient and courteous service
Esley - University City, MO
Margaret - University City, MO
The service man who came to my house was so kind and patient as we worked out the issues with our radiator heat. He was very knowledgeable and worked around our sleeping baby without waking him up. He was an absolute delight and fixed our issues in a timely manner. Fantastic!
Alexis - University City, MO
Charellise - University City, MO
Polite, proficient, explains what he is doing, and what is needed.
Barbara - University City, MO
Debbie - University City, MO
Appreciate you being on time and respecting our home - - wearing your shoe covers!
Billie - University City, MO
Great Service Thank You!
Love the plan we are on
Saundra - University City, MO
Our plan means we get our systems checked out when we should. The service is top notch!
William - University City, MO
John discussed all aspects of my system and did not try to just get in and get out. Answered all questions.
Very good service, would recommend.
Opal - University City, MO
On time, completed inspection and repair in timely manner.
John is fantastic
Joe - University City, MO
John is super. He's diligent and hard working. Does what he's says he's going to do and explains what he's up to. Doesn't oversell but makes recommendations that might be beneficial to us (e.g. fixing / maintaining our humidifier). Would recommend him 100%.
Cassandra - University City, MO
Ron - University City, MO
The technician was very courteous and knowledgeable. He acted in a totally professional manner. Great work!
Doug - University City, MO
Prof. GG - University City, MO
Marc - University City, MO
Couldn't ask for better service from Jeff who was thorough, explained everything and a is very pleasant person.
Great Service by your employee Patrick
Jane - University City, MO
Very thorough and polite
Great Service always on time....
Lois - University City, MO
Had a very positive interaction with John. He was professional and knowledgeable.
Kirk - University City, MO
Great technician (honest)
Patti - University City, MO
Ann - University City, MO
Cleaned & checked condensing gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Replaced air filter. Adjust blower. Blower: 3.2/4.5A . Inducer: .3/.52A . Temperature rise: 65 . Supply: stg2: 133 . Return:68 .
Found hot surface igniter bad. Inspected heat exchanger and flew piping. Flue piping does not have three screws per joint. Also, tee starting to rust. Replaced hot surface igniter. Tested operation. Temperature rise: 54. Inducer: .98 A. Blower: 5.1 A. Return air: 64. Supply air: 118.
I installed new drain pan level sensor. Tested system operation.
Cleaned & checked 2 gas furnaces. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitors. Second floor system: heat exchanger baffle in right chamber has fallen out of place and is warped, causing more heat to exit through the flue. Replaced air filter. Return air opening through attic floor is very small. Has two 8 x 3 1/2“ openings for return air.
No heat- replaced pressure switch
Serviced furnaces and humidifiers
New install— furnace pressure switch hose clogged
Scheduled maintenance on a hot water boiler.
Scheduled maintenance on a Lennox furnace.
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Found blower run capacitor weak: 14%low. Customer declined repair at this time. Replaced thermostat batteries. Checked filter.
Replaced relief valve on boiler...
Performed gas inspection for home sale. Kelvinator furnace model: KG7SC090D-35C. Serial number: KGD110401000. Found furnace running at high temperature rise (73 degrees) due to dirty, pleated filter and air filter rack undersized. I inspected heat exchanger and found crack where heat exchanger tube enters cold-end header box at back of furnace.
Replaced transformer on air handler
Serviced hot water boiler
Installed steam humidifier
Replaced warranty pressure switch
No heat,found locked up inducer draft motor
No heat—faulty pressure switch
Maintenance on Lennox furnace and accessories.
Cleaned and checked gas boiler. Inspected and cleaned heat exchanger. Checked flu piping and draft. Cleaned burners, pilot, and flame sensor. Checked voltage and amperage draw of pump. Bleed air from system. Clock meter: 102K. Checked manifold gas pressure. 3.58”. Boiler pressure: 18. Drain and set tank pressure: 16 PSI. Check the pump: .65 A.
Serviced furnace and humidifier and replaced filter
No heat found blocked filter
Boiler no heat,replaced bad gas valve
Serviced boiler and replaced flue piping
Serviced heating system